I'm so thankful for chrome & the last to service guys that came out. They always go Over & Beyond!!!
We were out of AC. Your technicians went above and beyond to make sure my family did not sleep another night without AC. Thank you.
I had pretty much given up on customer service until Brandon Shupak, from the Chrome air conditioning and heating was sent to my service call. Brandon surpassed my wildest dreams as far as outstanding customer service. He was dedicated conscientious, patient, diligent, empathetic, determined, and has the best work ethics I've have seen in a long time. For future service I would recommend chrome air conditioning and heating, to others and request Brandon specifically for future repairs. Chrome is lucky to have him.
We would highly recommend him for service calls.
Change out moen shower cartridge, posi temp. Repair was performed with 15 percent discount off of 298.00
Completed quick check in hvac system. Couldn't find anything wrong with system it was heating properly when we were there.
Performed heat check on both heating systems, I checked all major components within each system, safety switches, sensors, and motors as well as venting clearances. Also changed 16x25x1 filters chrome supplied.
Arrived at home inspection after home inspector had made a list of repairs. Emergency drain pan was slightly rusted in unit #2, although pan is structurally sound and had no sign of leaking. Upstarts bathroom had no hot water under sink or shower. Hot water valve was shut off under sink, and shower handel fixture just needs to be replaced or fixed. Half bathroom commode just needs a minor tank build replacement to stop water from constantly running. There was said to be exposed wire on outside condenser. After inspection of condenser the low voltage wiring is still incased from original casing from factory and has no exposed wire. Estimates attached for work that needed to be done. Pictures also attached
Completed one system fall matience. Changed the filter, checked heating components, safety switches and capacitors. Units is operating correctly at this time.
Completed 2 system fall matience. Both units are operating properly at this time. Estimates and pictures attached.
Heating and air conditioning repair service. Complete disconnect/breaker change out on air conditioning system. Also primary drain line was clogged and had tripped float switch. We cleared blockage at bathroom sink. AC unit is operating properly at this time.
Completed one system heat check. Heat strips are 10KW and both are working properly. Blower amps .94 /Capacitor 5-5uf and filter was clean. No options given at this time.
Completed three system maintenance. Found main furnace for half of downstairs and master bedroom is not working for heat at this time. Found blower motor leaking heavy amounts of oil and gas valve not igniting properly. Customer does not want to repair and prefers to upgrade old system. See all options for details.
Completed one system diagnostic. Air handlers transformer is faulty and not sending voltage to outside condenser. Office is going to call and reschedule for tomorrow. Going to find out if customer has labor warranty. Diagnostic and labor for replacement of warranty transformer Replaced transformer in air handler, unit is cooling again.
Called to unit not cooling. Upon diagnostic condenser fan motor had fallen inside condenser because of loose nuts. He have secured fan motor and rebalanced fan blade. Unit is up and running at this time. Other options were presented and attached.
Repair unbalanced and fallen fan motor
Found leak in evaporator coil (see attracted photo for details) evap coil is under warranty for parts only. Need to order coil and schedule time with customer to complete work.
Completed one system tune up on 6year old system.
System undercharged from previous visit and leak repair due to coil possibly still being frozen at time of visit yesterday. Added two more pounds to system and system is cooling properly at this time. Pulling a 18Â° temperature split.