Never will used this company again
When I called and they heard the heater was having problems they scheduled us ASAP with the cold weather coming. The person on the phone was professional and personable. Our repair tech, John, was very professional. He explained what was wrong, how the malfunctioning part worked, and what he needed to do to fix it before repairing it. It’s been close to a month and things are still running fine. I have confidence in this company and their work. The cost is expensive, of course but, I do not feel cheated.
Josh was very personable and professional. Also, very helpful and efficient. Also, it was wonderful to get such fast service at a great price.
We will recommend your company with everyone! The service was stellar!!
Would certainly call again. Explained what they were doing in detail and didn't charge me or replace something I didn't need. (that is, was honest, forthcoming and displayed trustworthiness
I am very happy with the service, and would highly recommend Chrome.
Nick Shain worked quickly and efficiently to check out and clean the AC compressors and recharge the refrigerant that was needed. The units are again functioning well. Our AC is back!
Very Bright guys.
very professional, friendly and honest,
Pull and reset 2 toilets, replace 1 flange, replace 1 anit-frost hose bibb
Shower Valve Replacement
Grill and boot replacement
Water Heater Replacement
Upon arrival homeowner showed me which vent was leaking. Checked attic space and found that the area itâ€™s leaking from has insulation coming off of the hard pipe. Explained to homeowner that we will just have to re-insulate the pipe to keep it from sweating. Repairs approved and will need to return with insulation to wrap ductwork.
Replace blower motor in rtu1/stock, change blower 3 pole contactor, labor, check rotation, check amps, adjust sheave, adjust belt on blower, and test operation. Can return Tuesday 6/22/21 for repairs.
Tune up on both Roof top units. Includes filters ( up to 8 per unit included per unit) any additional are 22 per filter.
Discovered faulty compressor with bad valves, a failed condenser fan motor. A contactor that is in bad condition. To get unit operational the parts listed above need replacement.
Replace emergency drain pan under furnace install safety float switch. Will have to remove existing drain pan. Install and level new emergency drain pan. Re pipe condensate line to appropriate location and Install two safety float switches to prevent any damage in the future.
Upgrade filtration to 4inch, add return ducts to all 4 rooms, get insulation up to 16-18 inches throughout and Upgrade plenium.
Customer said unit wasn't cooling. Found thermostat calling for heatand cooling at the same time. Need to replace thermostat. Bypassed thermostat and ran system through cooling cycle. Found condensing coil dirty. Split and wash condensing coil. Reset unit and ran system through operation. Checked refrigerant charge, took temp reading on supply and return air, took line temp temps. Found txv shutting down causing high superheat and high subcooling. Subcooling called for 3 degrees, unit was running 8 degrees, superheat was running at 41 degrees. Need to replace txv, recovery refrigerant, change dryer, pull vacuum on system, recharge unit, and test system. Lewisville store has txv in stocks. Customer is trying to submit repairs to his insurance for a claim.
Upon arrival found system running. Checked inside unit and found return box dirty and blower motor dirty. Recommended blower motor to be pulled and cleaned. Checked outdoor unit and found that my pressures were showing poor airflow across my evaporator coil. Checked inside coil and found it clogged with dust and dirt. Home owner approved cleaning of evaporator coil in place. Cleaned coil and checked pressures. Pressures look a lot better. Homeowner said he would clean blower himself.
Did spring maintenance. Noticed coils were very dirty, recommended acid bath and went ahead with it. Refrigerant level was a little low, we installed recently so I charged 1/2 pound.