Needed a soft start installed on an existing Lennox no one else said they could do it, they did and got it in with part in under a week. Happy.
Good communication. On time. I signed up for yearly maintenance. Jeremy our tech was professional and informative
Jeremy was awesome. Great service tech
Good job. Polite fast.
Ac Replacement- Estimate to replace evaporator Coil
Ac Repair- service call for system with leaking coil
Ac Repair- no cool, Replaced TXV
Estimate given for new dual HVAC unit zoned system
Residential maintenance call in Prosper and Upon arrival performed a one system maintenance checking cooling. Starting with indoor air handler, checked all electrical, mechanical and safety components. Checked amp draws and filter. Checked temperature split, everything checked out properly. Then checked outdoor units pressures, amp draws and capacitor. Everything checked out properly. System is cooling properly at this time.
Residential service call in Prosper to install a soft start on condenser. Tested operation of condenser. System is running properly at this time.
Springtime HVAC Maintenance for a residential homeowner near Preston Lakes. Performed a three system maintenance checking cooling. Starting with indoor units check all mechanical, electrical and safety components. Checked amp draws and filters. Found that the air filters needs to be changed out, two aprilaire 410’s. Checked outdoor units pressures, amp draws and capacitors. Found that the upstairs unit looked overcharged, checked units configuration and found that the first for downstairs was connected to the upstairs and upstairs furnace connected to the downstairs. Installers will need to return to swap furnaces.
Springtime A/C Maintenance for a residential customer near Artesia. Came out on a 2 system maintenance Checked pressures checked ductwork checked insulation levels cleaned condenser coils checked bearings checked blades checked electrical connections checked contactors checked run capacitors checked Amp draws Found Unit 2 Burnt and pitted contactor 1.5 pole Dirty condenser coils / cleaned during visit Unit 2 no transition for evap doesn't get full air flow Primary drain is stopped up as well as not stopped down hill. Unit number 2 evap coil is stopped away from the drain lines No surge protection
Springtime HVAC Repair Service near Windsong Ranch. Residential service call in Prosper and Found Master bedroom working properly at this time. Main unit compressor is off on overload high temp. Cooled down compressor turned unit on low side started going negative pulling vacuum highside starts to climb Opened up evap coil evap coil is clean there is a txv but no signs of freezing at all
Provided Quote for HVAC Replacement to a residential customer near Whispering Farms. Gave estimates for a 14,16,18 seer units, if going with 16 seer or higher plenums need replacing, if going with 18 seer plenums and thermostat wiring would need to be replaced. If going with 16 seer include a air scrubber. If going with 18 seer include air scrubber and surge protectors. Current system is a 3.5 ton, if going with 14 seer it needs to be a 3.5 ton.
Commercial Air Conditioning Repair Service for a customer in Prosper. Upon arrival found system that covers the right side of the office not cooling. The customer had the system off, turned the system on, and checked the indoor unit. Found everything operational, recommend replacing filters within the next few weeks. Checked the outdoor unit and found it slightly low on refrigerant and a contactor wore out. Refrigerant system is a sealed system and shouldn’t be losing refrigerant. Refrigerant does have the potential to Lea back out. The customer opted to add refrigerant and replace the contactor. Added 2lbs of 410-a to set charge, and replaced contactor. The system is now operating properly.
Commercial Air Conditioning maintenance for a client Prosper. Came out on 3 system maintenance today. Checked run capacitors, checked Amp draws, checked pressures, cleared drains, changed filters, checked bearings, checked blades, checked electrical connections, checked contactors, checked belt, checked temp splits, & checked economizers.
Spring Air Conditioning Service call in Prosper. Came out and Checked contactors, checked run capacitors, checked bladed, checked bearings, checked electrical connections, checked Amp draws, checked temp split, checked filter, checked duct work, and checked insulation levels. Customer happy on departure.
Residential Air Conditioning Maintenance Service. Came out on 2 system maintenance Changed Customer 16x25x4 filter and 20x25x4 filter homeowner supplied. Checked duct work checked temp split checked Amp draws checked electrical connections checked bearings checked blades checked coils checked motors for oil checked drain lines checked pressures Found Dirty condenser coils (recommend washing) No surge protection No IAQ (air purifier)