Good job. Polite fast.
Replace compressor includes refrigerant
Completed one system matience. Upon inspection I noticed that the txv inside the heat pump was frozen. I further diagnosed and determined that the tax isn't metering properly. Unit is running on emergency heat only. Leaving quote to replace. Estimate attached
System was not lighting upon arrival error code 270. I witnessed it a few times. After I preformed a simple matience and cleaned up the unit. Blew through the lines and now unit is working properly. I tested the unit 7 times. No charge was added to invoice, unit was just installed in August.
Completed 3 system fall matience, on aromstring air units. Changed filters, heating elements, amperages, motors and safety switches. Units have no air purification system. Estimate and pictures are attached.
Could not repair faucets on existing, customers had new faucets that we replaced. this is a call Back per Aaron no charge for replacement of new faucets
Take loose faucets on cold side of 3 sinks, free them of debris. Tighten flanges so they would not spin with handle. Test all 3, all are working properly at this time.
Got serial and model numbers for units. Going to call lennox Monday yo check availability, tmin order to give accurate pricing. Going to contact Monday with findings. Completed estimate and sent to customer 11:55 10/19
Found loose Common wire inside of furnace. Tightened wire and reprogrammed furnace, condenser and thermostat. System is operating properly at this time.
Completed three system fall maintenance. Customer is aware that $36 will be deducted tomorrow for a three system club agreement. Found faulty ignitor on Main US system. All ducting systems need to be properly cleaned as well. Customer declined all options and repairs.
Installed new drain pain, verified correct slope to drain outlet on pan. Insulated txv body on outside of coil. Cleaned primary and secondary drain lines. Verified that system is operating properly and found that it is.
Found faulty compressor and system almost empty of 410-A. Customer is going to use first company. They just wanted to see if the price was around the same for us as it was the other company levy and son. Gave option and customer declined all work currently and will be contacting other company unless they canâ€™t do the work.
Thermostat had filter allert. I (john) brought josh a new filter after replacement system recalibrated and cleared all allerts and codes. System is functioning properly.
Removed leaking coil, installed new. Tested all is working properly.
Customer stated there was vapor coming out of office supply vent when it shut down. I cycled the unit 3 times and never witnessed it for myself. I preformed a safety check and couldn't find the cause of the problem. Besides the unit being a few lbs low on refrigerant system looked normal. Customer was told to shut unit off if problem keeps occurring.
Installed new thermostat wire from condenser up exterior wall into attic and connected to furnace.