Good job. Polite fast.
Checked temp splits, indoor furnace voltages to unit, filter were clean, unit and coils made sure were clean, checked outdoor coils and superheat and charge, operating functionally
Checked temp splits and filters, one of the cleanest units have seen, calls for cool and heat properly
Checked indoor and outdoor coils. Breaker at outdoor unit was off on arrival, cause for not cooling. Dirty air filter causing blower to work harder and electric heating element to work harder and raise electricity usage. Filter replaced and breaker switched on
Checked volts across contactor, relay switch, checked line voltage going in and out of breaker. Airflow across coils at optimal performance. Superheat at ideal temperature. Heating element clean and coming on properly. Calls for cooling and heating on thermostat check out. Everything in order.
I found the buzz to be coming from the doorbell mounted on the wall.
Dispatched to heat pump not heating correctly. I checked amperages voltages of heat pump. Heat pump seems to be working correctly. 103 supply when heat strips were activated. Customer also talked about a thumping sound in attic as well.
Dispatched to potential duct cleaning. Son is having issues with mold/fungus is house. After inspecting the units, ducts were spotless. We decided that a UV light would better service there needs by keeping the upstairs system free of mold and fungus, as well as purify the air. UV light was installed, and monthly membership was purchased as well.
Need to call landlord for payment
Dispatched to unit not heating well. Unit is brand new. Upon inspection only 1/2 of the power strips were getting power. This was because only 1/2 of the high voltage was ever hooked up on install. An electrician should be coming either today or tomorrow to correct issue.
Replace compressor includes refrigerant
Completed one system matience. Upon inspection I noticed that the txv inside the heat pump was frozen. I further diagnosed and determined that the tax isn't metering properly. Unit is running on emergency heat only. Leaving quote to replace. Estimate attached
System was not lighting upon arrival error code 270. I witnessed it a few times. After I preformed a simple matience and cleaned up the unit. Blew through the lines and now unit is working properly. I tested the unit 7 times. No charge was added to invoice, unit was just installed in August.
Completed 3 system fall matience, on aromstring air units. Changed filters, heating elements, amperages, motors and safety switches. Units have no air purification system. Estimate and pictures are attached.
Could not repair faucets on existing, customers had new faucets that we replaced. this is a call Back per Aaron no charge for replacement of new faucets
Take loose faucets on cold side of 3 sinks, free them of debris. Tighten flanges so they would not spin with handle. Test all 3, all are working properly at this time.