He is very very good. He is iinformed confident and very polite and personable
Mike Rea explained everything and gave me options to help me make a final decision. I very much appreciate that he was professional, efficient and patient in explaining each option.
George, Michael and Nick are great to work with. Always provide great service, explain what they are doing and provide multiple options to fix.
Couldn't be happier. George is awesome! Thank you to Michael for the great prices.
Replaced one filter, cleaned condenser coils, calling for cool correct, checked voltage on units and ensured proper operation
Filter entrance is kinda exact had to flange metal to get filter in without ripping it up .... may wanna use a 20x25x3 if possible..... and drain is kinda rusty on unit to the right side of house.
Unit brand new, clean, replaced customer provided filter, check temperature splits and everything in operational order
I went through settings on control board at air handler, also through settings at thermostat. I reconfigured system so it recognized the heat strips,system is now working correctly and efficiently.
Found and capped leak behind shower so customer could have water. Master plumber will come back to make necessary repairs. Repaired 1/2" copper water line in master shower cold side.
Performed tune up of heating system, also set the winter schedule on the thermostat.
Completed one system matience. Unit is a 20 seer 3 year old unit. It has been kept clean in a clean attic with good insulation and a UV light to keep inside of unit clean. Unit is operating properly at this time.
Unit is sending flame ignition failure, unit does come back on and run when it retries to light. I tested and cleaned flame sensor, gas valve and board... I cannot get unit to fail at this time.
I contacted lennox support for intermittent "will start soo" being displayed on downstairs stat. It was determined that not all unused wire had been grounded properly. I did so, and while doing so I found some exposed copper in the wires being used. I also fixed this issue and tested. Unit is working properly.
Unit was working upon arrival, I tested unit off and on again. I checked furnace in attic and verified all is working properly. Customer will observe and let us know if it happens again.
HVAC system preventative maintenance service.
Air conditioning system diagnostic. Furnace door was loose and not pushing door switch in. Furnace is 27 years old. New board, gas valve, ignitor, flame sensor, pressure switch and blower motor are all new.