Answered all my questions
He is very very good. He is iinformed confident and very polite and personable
Mike Rea explained everything and gave me options to help me make a final decision. I very much appreciate that he was professional, efficient and patient in explaining each option.
George, Michael and Nick are great to work with. Always provide great service, explain what they are doing and provide multiple options to fix.
Couldn't be happier. George is awesome! Thank you to Michael for the great prices.
Assisted hunter with maintenance, recommended adding air scrubbers and surge protectors to units.
Demo wall behind dishwasher. Capped off water supply and drain for dishwasher in wall. Installed a Tee connection under kitchen sink and ran new water and drain supply through cabinet wall. Installed new frost proof hose bib in front flower bed.
Upon arrival performed a one system maintenance checking heating. Checked inside air handlers heat strips, amp draws, blower amps. Found airhandler not leveled properly causing system to not drain properly. Re-leveled unit. Changed customer supplied filter. Checked outdoor units pressures amp draws and capacitors. Found that the compressor capacitor is bad and need to be replaced. 71/80. Homeowner denied repairs Sent estimate over to replace capacitor.
Performed a fall maintenance checking heat. Checked sequence of operation, checked igniter, flame sensor, inducer and blower amp draws. Changed out customer supplied filter. Customer had mentioned that over the Labor Day weekend system had a hard time keeping up. Checked outdoor unit and found that the condenser coil was clogged. Causing pressures to rise. Homeowner deny washing condenser. System is heating properly at this time.
Upon arrival found that the main drain line was clogged up and over flowing out of drain vent. With approval blew drain line out and extended vents so water wouldnâ€™t overflow out of drain. After blowing out drain, sink in bathroom clogged up. Took apart p-trap and found it clogged with gunk and hair. Cleaned trap and put trap back together. System is now draining properly at this time. Recommended a plumber due to drain could still have hair and stuff clogged up in it.
Replace evaporator and suction line service valve
Upon arrival installed 6 Honeywell T9 thermostats. Set up WiFi and set up remote sensors. Tested all units and all systems came on. Owner had trouble connecting 5/6 thermostats to the app. Explained that is a customer support issue for Honeywell.
Run copper line
Customer said upstairs unit wasn't keeping up has it set to 71 and its 85 upstairs. Checked filter. Filter was collapsed and not filtering the airflow well. Replaced filter. Condensing coil was very dirty. Cleaned condensing coil. Blower speeds were not setup. Setup blower speeds for unit. Maintenance didn't seem to be done. Reset unit and ran system through cooling cycle. Took temp reading on supply and return air and checked charge on system. System is low on 410a. Need to do a leak search on system. Will have dispatch call and setup leak search on system and charge system up. Quoted leak search
Needs rescheduling, appointment time missed
Did system maintenance and inspection discovered compressor failing and evaporator coil leaking. Recommend replacing evaporator coil and condenser.
Replaced old thermostat with a brand new programable thermosts
Replaced one filter, cleaned condenser coils, calling for cool correct, checked voltage on units and ensured proper operation
Filter entrance is kinda exact had to flange metal to get filter in without ripping it up .... may wanna use a 20x25x3 if possible..... and drain is kinda rusty on unit to the right side of house.
Unit brand new, clean, replaced customer provided filter, check temperature splits and everything in operational order