Customer called about a squeaking noise. Arriving to the job we could find new squeaking noise occurring. M#60MGE4-11-241NP-1A s#1619K28609
Performed preventative maintenance for a magic-pak package unit model # 60mge4-11-241np-1a, serial #1619k28609. I powered the system down and removed the access panels. Removed and cleaned carbon off of the flame sensor. Cleaned out the burners and burner box. The system is located in a closet in the apartment. The return duct is not connected to the system. There is a flue for a gas fire place that blocks the return duct from being connected. The closet has been insulated so that when the door is closed it will pull air from the return duct (see photos). The homeowner has a washable filter that she will wash. The filter size is 12x24x1. I currently do not have this size however since the return is not connected I can place a larger filter in its spot until the washable filter is dry. Checked all electrical connections to ensure that they are secure and in good condition. I powered the system back up and called for heat. I took a combustion analysis test and received the following read
Survey for whole house dehumidifier. Will email a quote to homeowner. Please update ST with address and contact information.
Performed air duct cleaning and sanitation. All vents and ductwork are clear of dust and debris at this time. Unit is functioning properly at this time. Recommend duct cleaning every 3-4 years. Performed dryer vent cleaning. Dryer vent, duct, flex hose and lint trap are all clear of lint and debris at this time. Dryer is functioning properly at this time. Recommend dryer vent cleaning every 1- years. Thank you for your business!
Performed air duct cleaning and sanitation. All vents and ductwork are clear of dust and debris at this time. Unit is functioning properly at this time. Inside of ductwork is very rusty and is starting to show signs of rusting through in places. Customer is aware of the situation. Recommend duct cleaning every 2-3 years.