I've used this company for well over a decade and they do excellent work and provide superior service.
Found problem immediately . Very courteous and professional.
Thanks to Vu and his expertise and dedication. It's all the little things that Vu does that keeps me a loyal Comfort Controls customer.
Once again Comfort Control did an incredible job and their Tech Vu Tran is the best! He is incredibly knowledgeable and detailed every time he comes out.
Vu Tran like the rest of the staff at Comfort Control is a professional. He is prompt, friendly and helpful. He gets to the root of the problem and then will demonstrate the issue and make the suggestions for repair.
Great to work with Vu. He explained everything to me and provided pictures ofthe issues so i could make an educated decision.
didnt identify problem, tried to flagrantly overcharge for coolant (quanty and price), and lied about checking filter
Free consultation Atlanta georgia
One system tune up in Atlanta. Arrived on site, found package unit on right side of house. Customer complaint of bedroom not heating up, found it is due to improperly run Y. Found many spots in ductwork where rodent had chewed through ductwork. Found weak capacitor for blower motor, as well as duel run capacitor. Blower assembly is dirty and should be pulled and cleane, cannot access evaporator coil due to design of unit. Upon finishing tasks, I plugged disconnect in and unit started operating, but burner started rolling out and started to catch inducer motor wiring on fire. Unit needs to be replaced due to age and condition of system. Unit is not operational at this time. Left disconnect off because of heavy rollout.
Heating tune up atlanta. Completed 3 system tune up. Found both upstairs and main floor with dirty blower wheels. Heating elements working good. Main floor evap coil is leaking refrigerant out of evap coil. Coil needs to be replaced. Basement system is clean and working good. Capacitor is weak and needs to be replaced. All 3 systems missing secondary water safety switch to protect furnaces as wel as home from water damage. Insulation in attic is good. Filters are good. Cleaned outdoor coils.
Complete 3 heating maintenance in Atlanta. Check safety and operations. Find upstairs Amana gas furnace operating with in manufacturer spec. Suggest surge protection for gas furnace. Duct system not R8 to meet code. Find basement older Lennox gas furnace operating with worn blower motor and need to keep check. Find bio growth on air distribution box. Suggest pureAireX air purifier system. Suggest surge protection for furnace and suggest wet switch to help detect water due to not drain pan. Find basement Airhandler operating with in manufacturer. Suggest wet switch water detector. Suggest pureAireX air purifier system. All 3 system operating at this time.
2 system maintenance in Atlanta
2 system maintenance in Atlanta/
Two system heat maintenance in Atlanta. Arrived on site, changed filters and cleared barometric ports. Checked ignition systems, electrical connections, amp draw and capacitance. Found left side main floor system ( in crawl space) with inadequate amount of duct work putting a great deal of stress on system. Recommended installing more to help system to better move air throughout the space. Also recommend installing surge protectors for each system to protect electrical systems and Uv purifier to improve air quality inside house. Both systems are operating at this time
No heat in Atlanta. Check and find 21 year old Lennox gas furnace fail due to bad flame sensor. Test and find furnace operating with worn ignition, weak blower capacitor and dirty blower assembly. Duct system dirty and not code due to R6. Find system have not water protection in attic. Find gas line not code at furnace. Due to system age and conditions, suggest to upgrade, customer only want repair at this time. Replace flame sensor and furnace operating. Sign 2 cci plan and need to schedule for summer visit in Spring of 2021 and fall in 2021.
â€¢Completed a 3 system heating maintenance in Atlanta Georgia. Checked the safety and performance of the heating equipment. Checked the integrity. Changed air filters . Checked amps and motors . Signed up for the maintenance program. â€¢Upstairs system has a leak in the coil and operates on R22 which is phased out ...would highly recommend a new system due to age and conditions. Took picture of coil conditions. Going to be giving a price for a replacement AC and Coil for upstairs. Family wants to go with the 16seer AC and coil . Will send pricing . â€¢Basement system is heating at this time. 20x25x1 filter . â€¢Main floor is heating at this time . Cleared the drain line on this system and put towels in the safety pan . 16x20x1 filter .
Complete heating maintenance in Atlanta, find Trane gas furnace operating with weak flame sensor and incomplete combustion, causing high CO level. Complete combustion calibration service and replace flame sensor for 18 year old Trane system. System operating with worn ignition, damage water safety and missing cover for condensation pump. Note: master bedroom not comfortable due to long duct run. Suggest to run direct 10â€ supply run and drop down to 8â€ to help improve airflow.
Complete 2 heating maintenance in Atlanta. Find upstairs Lennox 7 year old furnace operating with worn flame sensor and not calibrated. Complete combustion calibration service, replace flame sensor and change filter. System operating with in manufacturer spec. Find downstairs duel fuel system 15 year old Amana. Find heatpump system low on charge and leaking at evaporator coil. Find coil baldy rusted and air distribution plenum molded. Find heatpump operating with worn contactor and stress compressor. Find furnace blower assembly dirty, flame sensor getting weak and rusted burner. Due to system age and conditions, customer need consultation visit.
Complete heating maintenance for gas furnace in Atlanta. Find Lennox Tstat fail. Replace Lennox tstat with Nest tstat. Test new tstat and system operating with in manufacturer spec. Did not change filter. System operating at this time.
Warranty service call in Atlanta. Check and find drain line loose and cause water to leak. Repair drain and run drain to main drain system.
No cool in atlanta. Arrived on site, found system off and not operational due to water safty. Condensation drain line backed up due to clog. We were just out here cleared drain and vacuumed out water. Unit is operating normally
New hvac system install