Comfort Control is very dependable, honest and efficient. Service technicians are top notch.
Comfort Control installed my HVAC system and upgraded my ductwork. They have done the seasonal maintenance on my system ever since. Always friendly and professional and in the these times of Covid they took steps to keep us and then safe. I highly recommend them.
Very knowledgeable. Professional!
Very knowledgeable, professional.
Free consultation for hvac systems in LAWRENCEVILLE Georgia 30045
Customer reported fan noise for downstairs system. Tested and could not get problem to duplicate itself. Tested fan and it is in good condition with a clean blower wheel free of obstructions. System is heating at this time.
Heating maintenance in Flowery Branch. Tested operation of 3 systems. Discovered basement system with weak blower motor controller and blower motor spun in reverse at one point during tested and systems tripped on high limit, system also has no water safety and worn draft inducer motor. Due to extent of repair and system being 17 years old replacement is recommended. Main level system also has no water safety and gas line is flexed through cabinet, supply plenum is choked down and is restricting airflow and efficiency, system is 11 years old. Upstairs system has dirty blower wheel, worn ignition, improper gas line flexed through cabinet, improper flue pipe not sized right for system and leaking carbon monoxide no drain line water safety to help prevent flooding in the case of common drain line clogs. System is 15 years old and replacement is recommended over repair.
Complete heating maintenance in Suwannee. Check safety and operations. Find Amana gas furnace operating with in manufacturer spec. Find flame sensor starting to ware, getting weaker and need to keep check. Suggest air purifier system to help improve air quality, suggest to surge protection and in-line water protection for system in attic. System operating at this time.
Furnace tune up in Lawrenceville, Georgia. Two systems. Found upstairs system with no filter inside, put filter inside. Tested mechanical and electrical components. Found both systems with no water safety so it is therefore not up to code. Found upstairs furnace with worn igniter. Found upstairs furnace with weak flame safety sensor. Found upstairs blower capacitor to be weak. Found upstairs blower wheel to be dirty. Found upstairs ductwork to be dirty. Found upstairs evaporator coil to be dirty. Found upstairs evaporator coil to be rusty and corroded and likely to leak. Upstairs ductwork is not of r8 insulation rating. Found downstairs blower capacitor to be weak. Found downstairs blower wheel to be dirty. Found downstairs igniter to be worn. Found intermittent issue with downstairs gas valve failing, either gas valve is going bad or control board is. Both systems are 16 years old. Due to age and condition of both systems, recommend upgrading systems to more reliable, more efficient s
Ware Bethlehem. Completed diagnostic. Fuse broken in air handler again. Replaced fuse. System came on and ran and satisfied twice. If problem continues will need to replace thermostat.
Heating repair in Buford. Mobil home furnace symptoms indicating issues with board and ignition flame recognition but board code indicated pressure switch stuck open. Cleaned pressure ports and system produced same systems for a few tries them started working normally. Tested system 4 time and started up and ran every time. System may need board, ignition and flame recognition replaced soon. Homeowner wants to wait
Free consultation Buford Georgia 30518
Free consultation for new heat pump cumming Georgia 30041
Complete Heating tune up special inspection in Suwannee. Check and find 17 year old Nordyne electric Airhandler operating with high power usage on motor, find evaporator coil dirty and UV unit not operating. Suggest water protection, surge protection, comfort care plan, clean evaporator coil and upgrade UV light to pureAireX air purifier system.
Warranty cumming. Completed replacement of evap coil and 2 capacitors. Pressure tested for leaks on new coil. Pulled vacuum to 450 microns. Re charged system to manufacture spec. System heating at this time.
Heating maintenance in Buford. Tested operation of 1 heat pump system. Discovered system with failing outdoor fan motor. System would also greatly benefit from compressor saver hard start kit to reduce stress on compressor and reduce energy consumption on start up. Added compressor saver to system. System 12 years old and may need to be replaced soon. System heating at this time.
Complete new system inspection in John Creek. Check and find new Carrier package unit on rooftop operating with in manufacturer spec. No concern on unit. Suggest to upgrade thermostat, suggest CO detector for building, suggest pureAireX air purifier system.
Furnace maintenance in Buford, Georgia. Two systems. Changed filters. Changed uv bulbs. Tested mechanical and electrical components, all in good shape. Found systems with no surge protection, recommend installing surge protection to protect equipment from power surges. Neither system has a hard start kit installed. Recommend installing hard start kits to take a load off compressors so they start smoother, run smoother, and therefore last longer. Systems are heating at this time.
Heating tuneup in Gainesville. Tested operation of 1 heat pump system. All components tested within normal manufacturing spec. Discovered system without drain line water safety to help prevent flooding in the case of common drain line clogs. System would greatly benefit from compressor saver hard start kit to reduce stress on compressor and reduce energy consumption on start up. Discovered organic growth inside system. Recommend ultraviolet light system to combat organic and viral growth in system and throughout the home. Added compressor saver to system and will revisit other repairs in the spring. System heating at this time