Great service tech, knowledgeable and professional!
He was very quick work of it once he had the part in hand.
Garret is very polite and very knowledgeable about his products. We felt the price may be high so we are going to get a couple more estimates before making a decision.
Great service as always!
Great service! Thank you Reece for your compassion at my sorrow, and for draining my hot water heater. It seems like the hot water is flowing faster.
Vu has been caring for our systems for at least 8or 9 years. We are always happy to see him because we trust his work and his advice. As a result, we don’t have surprise break downs mid-season.
We really appreciated not just the quality service but Jon wearing a mask the entire time he was at our house.
Very fast and efficient. A pleasant young man.
Lose wire connections on the neutral wire . Fixed issue system is now operating. Warranty .
Heating issue in Cumming Georgia. Inducer port was clogged . Took inducer housing off and cleaned . Cleaned flue pipe out as well . Lubricated port . Repair comes with a 1 year warranty.
HVAC issues in Alpharetta Georgia. System has a bad Lennox thermostat. Thermostat needs replacing. Supply house for Lennox is not open till Monday . Will have to see what the stock is on the communications thermostat. Will call Monday and inform the family on availability.
HVAC issues in Suwanee Georgia. Fuse was blown on the mother board . Replaced fuse . After replacing the fuse found the mother board on the start up is chattering and can smell a burning smell . Also found the zone board was non responsive and didnâ€™t have any of the led lights glowing and didnâ€™t have 24 volts . The zone board is bad most likely weather related with the storms and the mother board for the furnace has took some damage. Would highly recommend replacing the zone system . After getting deeper into the job the air boxes and dampers need replacing. The air boxes have biological growth all in them and the dampers are burned out . Going to have Jeff the field engineer come out and design a new zone system / plenums . Charging labor tonight that will credit on whatever the family decides to do . Thank you .
HVAC issues in Buford Georgia. â€¢Upstairs AC system has a bad outside dual start cap . Family wants to hold off on replacing that electrical part due to the weather cooling off and not really a demand for their AC at this time . They will call us when the weather warms back up to replace that part . â€¢Today I installed a UV light for the basement. Installed power module and UV Light in the evaporator coil . Took pictures. Working properly at this time . Price quoted for the UV light back October was $560.15 . Collected for the project today .
Two system heat maintenance in Buford. Arrived on site, changed filters and cleared barometric ports, checked ignition systems, electrical connections, amp draw and capacitance. Recommend installing secondary water safty to both systems to prevent water damage to electrical systems as well as surge protectors. Both systems are operating normally at this time
Free consultation for ductwork corrections flowery branch Georgia 30542
Free consultation for hvac system Dacula Georgia 30019 air conditioning mini split furnace
â€¢Completed a 1 system heating maintenance in Suwanee Georgia. Checked the safety and performance of the heating integrity. Checked heating elements. Checked amps . Checked oxygen and combustion levels . System is heating at this time . Would recommend having this system on a maintenance program to allow us to service the system yearly. â€¢Flame reader is getting weak and below speck ratings would highly recommend replacing that electrical part to prevent future break downs. Took flame reader out and cleaned to a good surface. â€¢Would recommend putting a sediment trap on the gas line going into the gas valve . To prevent trash and sediment getting into the valve . Family is signing up for the maintenance program. Signed family up .
Two system heat maintenance in sugar hill. Arrived on site changed filter and cleared barometric ports. Checked ignition systems, electrical connections, amp draw and capacitance. Recommend installing secondary water safty switch to each system and surge protection to protect electrical systems. Both units are operating normally at this time
No heat downstairs gas furnace in Grayson. Find downstairs Goodman gas furnace operating with worn inducer assembly and pressure port clogged. Clear port and test system. Find gas furnace under fire, operating with weak flame sensor and worn ignition. Suggest cci plan and suggest to upgrade system. Customer want to calibration both furnace and wait on repair. Give customer estimate to repair system. Complete combustion calibration.
Pre sold repair Dacula. Completed condenser fan replacement under parts warranty.
Inspection Dacula. Completed inspection on 2 systems. Main floor system is 7 years old and heating and cooling properly. System upstairs is 1 year old and heating and cooling properly. Systems have no water safety and air quality is not great. Suggest adding 2 forms of water safety on each system and installing electro static filter to better filter air of dust hair and spores. Also suggest installing UV air treatment systems to sterilize air and kill bacteria viruses and chemicals that could cause harm to residents health.
Heating tune up in suwannee. Arrived on site. Tested system from 1981. Blower motor would cut off and on during heating cycle. Found bad blower motor relay. Un able to get parts for system, will need to replace equipment.
â€¢Completed a two system inspection on the HVAC equipment in Buford Georgia . Looked over the safety and integrity of the performance. Checked electrical parts and amps . Cleaned static filters . Both systems are operating and working at this time. System pressures look good and passed a Delta T test . Burner assembly and gas valves working properly at this time .