Did fix everything well. Did know that we were elderly and isolating but stayed in our house too long and did not wear mask when he was in basement. Have paid bill through office but no receipt yet.
Most dependable AC company I’ve ever dealt with! Christian does an awesome job and always offers solutions to improve the efficiency of our systems.
Nice gentlemen, went right to work and gave detailed observation.
Christian was prompt, courteous, knowledgeable and answered all of my questions. He seemed to have my best interest at heart. An asset to your company.
They were very pleasant and got the work done in a timely manner.
Reece came on time and he is very knowledgeable. He provided periodic maintenance service to our Daikin VRV with 5 Air Handlers. He provided valuable recommendations in which we will have done during the next visit. I would recommend Reece to provide service to everyone.
Free consultation Suwanee Georgia
Ac repair in lawrenceville. Discovered failed compressor on 15 year old system. System needs replacement. Consultation scheduled
Ac maintenance in Dacula, Georgia. One system. Changed filter. Tested mechanical and electrical components. Found weak dual capacitor (45/5 mfd). Found electrical pitting present on main electrical switch. Recommend repairs. System does not have a hard start kit installed, recommend installing hard start kit to reduce load on compressor so it starts smoother, runs smoother and therefore lasts longer. Refrigerant pressures are slightly off. Recommend topping off refrigerant (r410a). Chemically washed condenser coil. Recharged system, replaced dual capacitor, replaced main electrical switch, installed hard start kit and installed surge protection for full system. System is cooling at this time.
2 system ac maintenance in Buford. Changed filters. Cleared drain lines. Checked mechanical and electrical components. Found upstairs blower wheel to be very dirty, recommend pull and clean service. Found upstairs blower capacitor(10) to be weak, recommend replacement. Found upstairs thermostat to have a faulty mode selection switch, recommend replacement. Found basement system blower wheel to be dirty, recommend pull and clean service. Found basement system to have a weak blower capacitor(5), recommend replacement. Found both evaporator coils to be dirty, recommend clean in place service. Found mold inside supply on basement system, recommend UV purification system to kill mold, bacteria and viruses. Found burnt and pitted contractor on upstairs condenser, recommend replacement. Due to the age, condition and cost of repairing both systems I recommend upgrading to a new and more efficient setup. Systems are operating at this time.
Arrived on site, changed filter and cleared drain line, checked electrical connections, amp draw, capacitance, cleaned outdoor coil and checked refrigerant pressures. Recommend replacing the supply plenum up in attic because it is too small for coil and moving duct that is coming out of the top of plenum to more evenly distributed air flow. Recommend installing surge protection to each piece of equipment, and a compressor assist kit to each outdoor unit to prolong the life of the compressor. Both systems are operating normally at this time
Water heater inspection in Buford. Homeowner concern was humming at water heater. Humming is coming from recirculating pump. Homeowner wants to wait until it fails to replace. There is a brand new pump in box by water heater.
Ac maintenance in cumming Ga, two systems. Checked all electrical and mechanical components. Found upstairs furnace blower capacitor to be weak.(4.4/5). Checked all electrical components for ac condensers. Both systems are cooling at this time.
Tune up suwanee. Completed tune up on 3 systems. Main and basement have clean blower and coils. Changed filters. As lines ran good. Missing back up water safety. Pressures are good on both. Upstairs has very dirty blower wheel and void of refrigerant. Tested with nitrogen. Pressure held. Could not find leak. Gave quote on filling with 410a and duct cleaning for all 3 systems. Having consultant come out to give quote on new system for upstairs.
Ac maintenance in Suwanee, Georgia. Three systems. Upstairs system not cooling. Found burnt wire going to compressor. Found pitted main electrical switch. Due to age and condition of upstairs system, recommend upgrading system to a more reliable and more efficient system. Set up consultation for customer. Recommend adding additional ductwork to upstairs system with install to reduce high static pressure. Changed upstairs and main level filters. Cleaned washable basement filter. Found basement blower capacitor to be weak (7.5 mfd). Basement dual capacitor is completely non functional (35/5 mfd). Basement main electrical switch has electrical pitting/ burning present. Replaced basement dual capacitor. Main level and basement systems are cooling at this time.
Two system cooling maintenance in Flowery branch. Arrived on site, changed filters and cleared drain line, checked electrical connections, amp draw, capacitance, cleared outdoor coil and checked refrigerant pressures. Recommend installing surge protector to each piece of equipment, a compressor assist kit to each outdoor unit to assist compressor upon startup and an electro-static filter to help purify air coming into system. Both systems are operating normally at this time.
Ac repair in Cumming Ga. discovered failed variable speed blower motor and furnace control board. Tested electrical components in outdoor unit and discovered weak secondary controller and main electrical switch. System also needs a compressor saver hard start kit to reduce stress on compressor and reduce energy consumption on start up which will extend the life of the system. Consultation s heâ€™d for today 3-5 for replacement of the furnace and will need to replace components in outdoor system as well
Ac maintenance in norcross Ga, one system. Checked all electrical and mechanical components. Everything is functioning as they should at this time. Found found hard start kit for ac condenser to be in bad condition recommend replacing. Also found disconnect box to be in bad condition. System cooling at this time.