I've used this company for many years and I've always had excellent service and very satisfactory systems installed by them. Where there was a problem, the management stepped in and made it right. Highly recommend.
Dylan and Eric were such hard workers. It was very cold the day of the installation, but they didn’t let that slow them down. I am very happy with the install.
Quick repair and great service z
2 furnace pm check complete. Tested mechanical and electrical components, all in good shape. Customer has asthma, recommend apco air purifiers to help keep evaporater coils clean, prevent mold and to kill bacteria, germs and viruses for improved air quality. Systems are heating normal at this time. Insulation levels are low, recommend adding more in for improved comfort and efficiency. Changed upstairs filter with filter customer provided. Did not change main level filter.
No heat main floor zone system. Found no signal to furnace, found arzel zone board on lockout. Potential cause by surges, reset and system came on. Found worn ignition and weak flame safety sensor, replaced and system heating normal Main floor
Faulty fan motor. Found bad compressor voltage absorbsion system. Installed float switch on main level attic pan. Put a 14x20x1 filter in basement airhandler.. system operating properly at this time. Replaced condenser fan motor. Replaced outdoor voltage absorbsion systems.
Came to check on noise. System working normal. Will hear more air noise if one or two zone is off.wokring normal
System is not starting up due to bad pressure switch. It will start every once in a while but the pressure switch is going bad. Need to replace pressure switch for system to work consistently
Picked up parts at supply shop, installed and working normal
2 furnace tune up complete. Changed filters. Tested mechanical and electrical components, all in good shape. Systems are heating normal at this time. Customer upgraded tune up to maintenance plan.
No heat downstair system. Found system retries and code 1 and 6 for smart valve. Have 24v coming from valve to ignition but no burners. Found bad ignition/flame rod assembly. Replaced and system now heating.
2 heatpump pm check complete. Changed filters. Tested mechanical and electrical components, all in good shape. Systems heating normal at this time.
Replace both airhandler heating element relay and control board. Test and and new control and relay operating normal.
Full warranty, picked up humidifier parts at mechanical in Braselton. Went to Lennox in Norcross to pick up i comfort thermostat. Replaced motorized damper and circuit board for humidifier. Tested and working normal. Replaced Icomfort thermostat, owner did not know Wi-Fi password. Owner will register himself
Found basement system ignition system to be broken and has a worn flame safety, recommend repair. Replaced ignition system and flame safety and system is heating. Signed customer up for 4 system maintenance plan- 3 systems and 1 mini split system. Main level flue pipe is single wall and therefore not up to code. Main level gas line going into furnace is flex and therefore not up to code. Put new batteries in basement thermostat for customer. Washed mini split filter. Upstairs gas line is also not up to code. Upstairs blower motor controller is running weak and flame safety is failing, recommend repairs. Replaced blower motor controller and flame safety on upstairs system. All systems are heating at this time.
No heat downstairs. Check and find damage furnace power switch. Repalce main power switch for upstairs and downstairs system. Both heating furnace operating at this time.
We cleaned the mainfloor and lower level of the home. I gave a $50 military discount. I quoted
3 system furnace prepaid. Clean filter and replaced basement system filter. 3 system heating normal. Suggest to replace burnt main switch for 3 system and suggest hard start kit for all 3 compressor