Very nice to have Jordan investing time to review a system and answer all the questions I had.
Sent separate for your info
I had two units tuned up for the fall. Work was done professionally and efficiently. Couldn’t ask for a better service call.
Jordan has been amazing throughout the service he has provided for me. He’s been very helpful and knowledgeable. Even when he had to give me the bad news.
A/c diagnostic in flowery branch, upon arrival I found emergency pan filled with water, condensate pump was dirty and clogged, flush drain line and cleaned condensate pump. System came back ON. System is cooling at this time. Outdoor refrigerant pressures are good.
A/c diagnostic in flowery branch, indoor unit was running but not the condenser found one of the low voltage wire broke off do to age fixed problem. System is cooling at this time.
A/c diagnostic in Gainesville, replaced indoor fan motor. System is cooling at this time.
A/c tune up in Lawrenceville, home owners have the house for sale, checked both systems, 1st unit is located in the basement (main level ) system is cooling at this time, unit has a 20Â° split, blower wheel is clean, evaporator coil is clean didnâ€™t fine any leaks, checked all electronics and components they are good, drain line is clean. Outdoor unit is rusty but still working properly, pressures are good. 2nd unit is located in the attic, ( upper level ) system is cooling at this time, unit has 73.4Â° from the return and 55.4 from the supply unit has a 18Â° spilt, blower wheel is clean, evaporator coil is clean but a bit rusty didnâ€™t find any leaks at this time, drain line is clean, both filters are good. Outdoor unit is old and had to add a bit of refrigerant, but system is still working properly at this time.
A/c diagnostic in Buford. Replaced indoor unit main board, Bluetooth control. System has a bad 12 inch zone damper and needs a coil sensor/Plenum sensor. Provided quote to the customer for those items. Customer wishes to speak with Jeff Schmitt before agreeing to any more costly repairs.
Armana coil leaking. Systemnusing R-410A. Recommended receiving quote for replacement. Dispatch fee waived per management.
Tune up flowery branch. Did a leak search on evaporator coil. Did not find any leaks. Blower wheel needs to be cleaned. Indoor capacitor needs to be changed. Condensate pan needs to be replaced. No water safety. Outdoor capacitor is within range. Pressures on system are good. System is cooling at this time.
A/c diagnostic Flowery Branch: we inspected system and diagnosed a faulty capacitor on the condenser. Replaced capacitor on condenser and checked the remainder of the complete system. All other aspects of the system are functioning properly and cooling well.
Tune up flowery branch. Did a leak search on evaporator coil. Did not find any leaks. Blower wheel is clean. Filter is clean. Drain line is clear. Outdoor capacitor is within range. Pressures are within range. System is cooling/heating at this time.
A/c diagnostic in Suwanee. Found indoor unit running, outdoor unit fan was running but not the compressor. Condenser has a bad secondary motor controller. Replaced capacitor system is cooling at this time. Blower wheel is clean, evaporator coil is clean, drain line is flushed.
No cool Buford. Found outdoor system was not turning on. Found plug was not plugged into terminals. Determined that a terminal was leaking and as the pressures built up it was forcing the plug off the terminals. Compressor needs to be replaced.
Maintenance in 2 Goodman gas furnaces and AC. Both systems working at normal operations. Replaced downstairs condensate pump and hose. Recommended blower motor cleanings for both furnaces. Replaced 1 16x25x1 filter upstairs. Downstairs media filter needs to be replaced.
Carrier Greenspeed 4 ton with zoning Supply Plenum 16" damper 12" damper Infinity zone controller Infinity UI Infinity zone sensor
A/c diagnostic in Flowery Branch, unit located in the basement. found emergency pan filled with water, checked evaporator coil, coil is really dirty and rusted, also found a leak on the bottom left side. Evaporator coil has a metal drain pan that is rusted. Blower wheel is really dirty, unit is old R22. Condensate drain tubing is old and needs to be replaced.
Maintenance Buford. Did a leak search on evaporator coil. Did not find any leaks. Blower wheel is clean. Changed filter. Drain line is clear. No cracks in heat exchanger. Outdoor capacitor is within range. Compressor is good. Pressures are within range. System is cooling/heating at this time.