He knows HVAC inside and out.
Prompt, knowledgeable, polite, and thorough
Reece always does an excellent job very professional
Jon is extremely efficient and answers any questions I have.. Would recommend him to anyone for service.
Jon was very knowledgeable and answered all questions.
I called Comfort Control because I had warm air blowing from my vents. It was late evening on a Friday. They were able to get me in for a Saturday appointment. Reece was the technician who came out. He was prompt to the scheduled appointment time and gave my system a through inspection and gave me some options for the repair. Reece was courteous and professional.
Excellent service. I have no complaints. Everyone we spoke to was polite and very helpful. I will definitely recommend Comfort Control to others.
No heat in braselton. Check and find 13 year old heatpump and Airhandler. Find Airhandler fuse pop. Replace 3 amp fuse and system operating. Check and find Airhandler evaporator coil badly rusted, and missing inline water protection. Find heatpump operating with weak capacitor, worn contactor and compressor start up stress. Suggest to upgrade equipment. Customer want to wait to til January to call for consultation.
No heat in braselton. Check and find master bedroom gas furnace #3 fail due to fail thermostat. Replace Tstat with nest customer provided and replace upstairs Honeywell tstat customer provided. Test both Tstat and bout operating at this time. Test gas furnace and find gas Lennox 13 year old furnace operating with weak flame sensor, weak capacitor, and under temperatures. Suggest repair for system. System missing in line water protection in attic. Suggest Comfort control maintenance plan.
Wire repair in braselton. Arrived on site, found both new furnaces had not been wired for common, landed common wire on both furnaces and thermostats. Tested system to make sure units are operating. No other issues present at this time
No heat in braselton. Arrived on site, found bad blower motor, will need to order one from trane
No heat braselton. Completed diagnostic on 14 year old furnace. Inducer poets were clogged. Cleared ports. System came on. Inducer motor is failing. Running really high amps. Flame sensor is starting to erode and could fail. Heat exchanger shows signs of corrosion and could be detrimental to health if holes occur in exchanger. System should be replaced due to condition and cost of repairs.
Heat pump maintenance in Braselton, Georgia. One system- bonus room system. Changed filter. Tested mechanical and electrical components, all in good shape. Static pressure readings are in good shape. System is heating at this time.
Free consultation for new heat pump Braselton Georgia 30517
One system heat maintenance in braselton. Arrived on site, checked heat strips, electrical connections, amp draw and capacitance. Found system without water safty in crawl space. Recommended installing overflow switch to system as well as surge protectors for each piece of equipment and a compressor assist kit to outdoor unit to take some of the load off of the compressor uppon startup. Unit is operating at this time.
Completed duct run in Braselton Georgia . Mastic . Cleaned .
Gave estimate on replacing a air duct and doing a tune up on the equipment and cleaning . Family wants to move forward. Office will call and schedule the repair . Thank you .
Furnace maintenance in Braselton, Georgia. Three systems. Changed upstairs filter provided by customer and basement filter. Tested mechanical and electrical components. Found upstairs gas line drip leg not up to code, it isnâ€™t long enough. Found gas line going into all furnaces not up to code, flexible gas line should not be inside furnace. Recommend making upstairs drip line longer and replacing flexible gas lines with hard pipe inside all furnaces to bring systems up to code. Brought all three gas lines up to code by moving flexible gas line to outside of furnaces, putting hard pipe inside furnaces and extending upstairs drip leg. Replaced main level flame safety sensor. Systems are heating at this time.
AC repair in Braselton. Discovered main floor variable speed blower motor not coming on. Cycled power to diagnose. Call motor started working system is 13 years old at the end of its lifespan and replacement over any repair is recommended. Need to email and keep in touch with homeowner about scheduling a consultation. System working at this time but do not know how long it will be
â€¢ Completed a two system heating maintenance in Braselton Georgia. Prepaid visit today. Checked the safety and performance. Checked heating integrity. Checked heating elements. Completed maintenance cleaning on the furnace. Both hearings systems are working properly. Family provided filters . Replaced the main floor filter today and the upstairs filter still had some life in it . â€¢Attic insulation is low and below the beams . Would recommend bringing the insulation to specks for better comfort and lower utility bills. Would also recommend a attic tent .
Heating tune up braselton. Completed tune up on 3 year old zoned system. System is heating both zones properly. All electrical connections are clean and tight. Everything inside system is clean. All safety switches working. Insulation in attic is good. System does not have enough return air for size of system. Should have at least one more return in house.
Heating maintenance in Braselton, Georgia. Two systems. Changed filters.tested mechanical and electrical components. Breaker for downstairs heat pump failed. Replaced downstairs heat pump breaker. All other components in good shape. Recommend installing hard start kits in system to reduce load on compressors so they start smoother, runs smoother and therefore last longer. Recommend surge protection to protect equipment from power surges. Recommend pureairx air purifiers to kill mold, bacteria, germs and viruses for improved air quality. Systems are heating at this time.