Response from Comfort Control Heating & Air:
David, thank you so much for the 5-star rating for your HVAC Service!
It’s been two weeks and I have not received an estimate I made a call to check someone is going to get back to me but I’ve heard nothing and I’ve not received an estimate not very impressed at this time I feel like my time was wasted
Arrived on time, diagnosed the problem right away. Informed me of the issue and also gave suggestions for maintenance. Will get back as for the yearly maintenance plan
Always a great experience
Brett Castell was an awesome tech! Thank you!
The only bad things was technician forget to rest noth systems back to normal he left them both on 60 degrees
Jon has been coming to maint. my system for a couple of years. Always on time, very efficient and very pleasant to talk to. Very knowledgable.
He was thorough, polite, and very courteous!
He knows HVAC inside and out.
Response from Comfort Control Heating & Air:
We are incredibly grateful that you took the time out to leave us a 5-Star review for you HVAC Maintenance.
Prompt, knowledgeable, polite, and thorough
Reece always does an excellent job very professional
Tune up braselton. Did a leak search on evaporator coil. Did not find any leaks. Blower wheel is clean. Changed filter. Drain line is clear. Outdoor capacitor is within range. Pressures are within range. System is cooling at this time.
A/c diagnostic in Braselton. Unit is located in the attic, System is cooling at this time, Found UV bulb is burnt out, needs to be replaced. ( replaced UV bulb ) bulb Is ON and working. Also found on back side of unit wasnâ€™t sealed properly letting attic air in.
Maintenance Braselton. Did a leak check on all evaporator coils did not find any leaks. Blower wheels on all three are clean. Changed filters. Drain lines are clear. Found weak capacitors on the basement indoor unit and upstairs indoor unit. Changed both. Outdoor upstairs unit had a weak capacitor. Changed that as well. Pressures on all three systems are within range. All three systems are cooling at this time. Customer has black dust particles coming out of supply ducts. Recommend duct cleaning.
Ac service in Braselton. Discovered system completely frozen with good airflow indicating system leaking refrigerant. Homeowner wants to wait a few days to make decision on replacing the coil or replace the outdoor and coil with 10 year parts warranty.
Common wire has became exposed and touched ground, popping the fuse. Capped wire and added new fuse and system cut on properly. Thank you for choosing Comfort Control!
Float switch was tripped, pan had no water in it. Reset switch and system came on properly. Cleared drain line out to prevent overflow, drain is clear. System is not freezing up. System is cooling fine at this time. Customer is not home, will bill $79 diagnostic.
Consultation on insulation blown in and mini split for unfinished attic area. Jeff is also coming out later today to get a second look at measurements and requirements for the job.
Cockroach took out hermetic side of capacitor, replaced 45/5 capacitor and compressor cut on fine. Hard start could be added to help prolong compressor life. Contactor is in fair condition. Coil is dingy. Systems pressures are good 145/320. Indoor coil is clean. 19x54x1 filter is clean. Blower is a bit shaky. Blades are clean. Furnace interior is in good condition.
Replace zone damper and add a bypass
Zone system has been failing, actuator is causing the system to freeze up. Ordered ARP 10â€, CPRD 10â€, and plenum sensor for system to cool correctly. Need to pick up install on a later date. Quoted $770 for work. Picking up parts from Mechanica Equipment co in brasleton.
Replaced bypass duct , 10â€™ of 10â€ flex.
2 A/c maintenance in braselton. 1st unit Upstairs system is cooling at this time. Blower wheel is clean, evaporator coil is clean, flush drain line, changed filter. 2nd unit downstairs system is cooling at this time. Evaporator coil is clean, blower wheel is clean, flush drain line, changed filter.
Static damper flex duct has hole in it, need to schedule for Tech to Come out and repair duct work. $136 for 10â€™ of 10â€ duct.
Drain had clog at male fitting, male fitting was also leaking water out of port. Cleared male fitting, replaced male fitting, added a union, and cleared drain line. System is draining properly at this time.
Water leak from the upstairs unit. Found the source of the leak to be from a poorly connected section of PVC. (See pictures) Removed and rebuilt the beginning section of the drain line, including the clean out and P trap. Confirmed fall for proper drainage. (Also see pictures) Repairs needed: The indoor unit needs to be removed/uninstalled, to address the wet decking and wet insulation under the decking. The emergency pan is showing rust from the water collecting outside of the pan. When the unit is reinstalled, the pan needs to be pulled forward and to the left to be under the drain line, so the pan can catch the water in case of a breakage or backup in the future. Recommend primary and secondary drain outlets to be protected with overflow protection switches.