Reece always does an excellent job very professional
Jon is extremely efficient and answers any questions I have.. Would recommend him to anyone for service.
Jon was very knowledgeable and answered all questions.
I called Comfort Control because I had warm air blowing from my vents. It was late evening on a Friday. They were able to get me in for a Saturday appointment. Reece was the technician who came out. He was prompt to the scheduled appointment time and gave my system a through inspection and gave me some options for the repair. Reece was courteous and professional.
Excellent service. I have no complaints. Everyone we spoke to was polite and very helpful. I will definitely recommend Comfort Control to others.
Jon Fowler was very professional and answered all of our questions.
No cool in braselton. Arrived on site, found all systems with clogged filters, upstairs system and basement system had tripped breakers, reset and tested, both immediately tripped again. Tested outdoor unis and found both compressors grounded. Need to replace both systems. Main level found dirty 20x25x5" media filter clogged customer will replace himself. Turned off power to furnace till he is able to get new filter so no more damage is done to system.
Complete 2 heating maintenance for both gas furnace in braselton. Find upstairs 15 year old carrier gas furnace operating with in manufacturer spec. No concern at this time. Suggest in-line water protection and suggest air purifier system to help improve air quality and prevent molding. Find main level Amana gas furnace 3 year old operating with in manufacturer spec. Change main filter 16x25x5 filter customer provided. Suggest air purifier system. Both gas furnace operating at this time.
Heating maintenance braselton. Completed heating maintenance on 4 year old system. Blower and evap coil clean. Static pressure is good meaning system has good air flow. Filter is good. Heat strips are working properly. Insulation is good in attic. System has no back up water safety to protect system as well as house from water damage. System would also greatly benefit from having surge protector installed as well as UV light treatment to kill bacteria viruses and chemicals in air that could cause harm to residents.
Completed two system heating maintenance in Braselton Georgia . Changed air filters . Checked the safety and performance of the heating operation. Checked the integrity and amps . Checked heating elements. Both systems are heating at this time . Prepaid visit today .
Heating maintenance braselton. Completed 4 system heating maintenance. All 4 systems 4 years old. All clean with working electrical components. Static pressure on all are good as wel as combustion. Left filters for systems. None of the systems have back up water safety devices. Recommend inline float switches to all to protect the system as wel as the house from water damage. Systems would greatly benefit from having surge protectors added to system as well as electro static filters to better keep systems and home cleaner longer and UV air treatments installed to sanatize air and kill bacteria viruses and chemicals in the air that could cause harm to residents.
Flowery branch new furnace
Heating maintenance braselton. Completed one system heating maintenance. Found system 10 years old and working properly. Heat strips cleaned and working in range. Blower is clean. Coil is clean. Changed filter recommend electro static filter for better cleaning. Recommend surge protector for air handler. Also insulation in attic is below beams. Recommend blowing in to avoid heat loss
Looking over cooling system in Braselton Georgia . Second opinion on the upstairs system . System is slightly low on R22 charge and showing its age , the indoor coil is very rusty took pictures . Talked over some options on what we can do . Family has a home warranty and at this time they donâ€™t want to put any repairs on the unit and they want to let it ride and get it through the little bit of warm weather we have left since itâ€™s almost winter .
Furnace maintenance in Braselton, Georgia. Two systems. Changed filters. Wiped down furnace cabinets. Dusted out filter cabinets. Tested combustion, found both furnaces slightly under fire, recommend recalibration to get maximum efficiency out of both furnaces. Wear and tear is present on downstairs flame safety sensor, recommend replacement of part. Recommend surge protection to protect furnaces from power surges. Replaced main level flame safety sensor. Recalibrated both furnaces. Systems are heating at this time.
Heat/furnace maintenance In braselton. Discovered both furnaces underperforming with adjustments to calibration needed for maximum efficiency. Downstairs flame safety is weak but still functional. Upstairs inducer has vibration. Both system heating at this time but are 19 years old. Replacement is highly recommended
Ac repair in Braselton. Found crushed return duct and air leakage at supply plenum connection to evaporator coil. Fixed return duct and resealed supply plenum connection.
Ac service braselton. Completed diagnostic. Found leak in evap coil. Blower wheel is dirty. Filter is clean. Outdoor unit has very low pressures. Failing contactor and compressor running with slightly high amps. With age of system and condition.l recommend replacing against repair. Having jim come out to give quotes.
Quoted pricing on a new compressor for upstairs system.
Ac service braselton. Completed diagnostic. Found system with bad zone damper to back laundry room. Customer says they donâ€™t use that room. Found zone board in master bedroom closet. Found system with no back up water safety. System is 14 years old. Thermostats are outdated. Outside had compressor terminal ripped off inside unit. Reattached terminal and wires. Capacitor is good and contactor is good. Pressures are good. Compressor running at high amps per manufacturing spec. System will not last very long. Is running and cooling at this time.
Ac service braselton. Completed diagnostic. Found system very oversized for area being conditioned. System only servicing front retail back bathroom and back office. System is 5 tons. System should only be 2 tons for that area. System is also leaking refigerant in evap coil upstairs. System is getting severely choked because of the oversize. Condition of system will only get worse if left unchecked. Thermostat controlling system is in back hallway and is mercury thermostat. Customer wants moved to retail area with newer thermostat. Ductwork needs to be sealed to unit upstairs. There is a concerning amount of leakage in ductwork. System has no water safety upstairs. If drain line going outside gets clogged or if system freezes and thaws too quickly it will overflow into attic and cause water damage. Outdoor unit has high amps on compressor and fan motor from the stress of being oversized. Customer needs hard copy mailed to them.