Had a problem with my water heater and as always Tom with comfort control came right over to fix it! Reliable and professional ‘
Very Positive service call. Was able to repair my unit until I have money for a new system
Very professional and informative! Asset to your company.
I used 3 other companies before moving to Comfort Control. Their service is absolutely second to none. Found out that people at my office use them too. And they had nothing but great things to say also! Can't recommend highly enough!
Tom at comfort control is always there when we need him! True professionals! Thank you for all you do!
Not only was the tech courteous, professional and friendly but he was also early!! That is important when you have no a/c. I will definitely have Reese out again the next time I need maintenance are service.
Comfort Control replaced both our aging HVAC units. The crew did a phenomenal job! They even cleaned up and vacuumed where they worked inside the house. This was easiest and most cost friendly process ever!
No cool. Found thermostat very dim on display. Replaced battery and same thing. Found weak compressor saver and 1 lb low on freon. Installed compressor scar, added 1lb of freon and replaced thermostat to a Honeywell Wi-Fi model. Tested and working normal
Complete 3 system a/c repair and preventative maintenance check. Upstairs- Found the noise coming from the furnace in attic. Discovered it was the filter clip inside vibrating. Replaced filter and noise went away. Furnace is old but in fair condition. Recommend adding a inline safety switch. Checked pressures and amps. System is working good. Recommend adding a start kit to condenser. Main Level - Both Furnace and cooling system are 18 yrs old. Furnace is in Fair condition. Replaced filter. Cooling system is old and running high amps. System is running R22 refrigerant and will be discontinued at the end of the year. System has a new controller and start kit added. Main switch is pitted. Basement - System is new and working good. Checked pressures and amps and found to be to manufacture specs. Would recommend adding start kit to condenser for better startup and decrease the load.
Free consultation for upgrading your system. Thank you for your time. Estimates are valid for 30 days. If you have any questions please contact us at firstname.lastname@example.org or call us at (770) 932-5012.
Complete 2 system a/c repair and preventative maintenance check. No cool main floor. Found variable speed motor with O.L and also board for the motor. The system is old and needs to be replaced. Will have the manager come out.
Complete 1 system a/c repair and preventative maintenance check. Completed diagnostic found a bad capacitor outside. Recommend replacing the capacitor and adding a surge protector to prevent damage to electrical components.
Complete 1 system a/c repair and preventative maintenance check. Completed diagnostic found capacitor bad outside. Recommend replacing and adding a compressor saver to prolong the life of the system. Completed repairs checked pressures system is cooling at this time.
Complete 1 system a/c repair and preventative maintenance check. Found system low on freon. Found oil residue on the condenser coil on the discharge line. The part is still under warranty but not labor. Gave owner price of replacement. The owner will let us know.
Complete 2 system a/c repair and preventative maintenance check. Changed filters. Tested mechanical and electrical components. Found dirty blower wheel in the upstairs system, recommend blower wheel pull and clean. Found downstairs system with no secondary water safety, recommend adding on to protect from potential water damage. The downstairs system has no p trap, recommend adding on for proper draining. The downstairs system is freezing up, the bed is blocking return vent. Customer will move the bed, may want to have pressures rechecked after the return is no longer blocked. Neither system has surge protection, recommend adding on to protect systems from power surges. Neither system has a hard start kit, recommend adding on to reduce the load on compressors and prolong the life of the systems. Chemically washed condenser coils. The upstairs system is cooling normally at this time.
Upstairs system is cooling fine but customer hears humming noise from compressor inside. Only problem I could find is a bad capacitor that needs to be replaced. May not help with noise though. Customer wants to wait on capacitor repair
Complete 1 system a/c repair and preventative maintenance check. Completed diagnostic found outdoor unit very dirty and bad capacitor. Cleaned off coils. Changed the capacitor. Pressures are good customer declined maintenance plan. The system is cooling.
Complete 2 system a/c repair and preventative maintenance check.No cool upstair. Signed new contract. Left filter for the owner, clean condenser coils. Found upstair low on freon, added 3 lbs of freon for upstair and 1 lb of freon for downstair. The system is cooling at this time
Complete 2 system preventative maintenance and system. Smell for the downstairs system. The customer said smell coming from the downstairs system every time come on but it will go away after a few mins. The smell of death rotten flesh. Told customer if system something dies in the duct system we would smell it all the time. Customer will keep an eye on the smell.
Complete 2 system a/c repair and preventative maintenance check. Checked charge. Checked electrical. Replaced filters. Systems are 4 months old. Systems are cooling well at this time.
Complete 2 system a/c repair and preventative maintenance check. Replaced both thermostats. Did not replace the elements because I need a special tool to remove them. If the problem continues I will need to replace the elements.