3 system ac tune up complete. Changed filters and added a nice citrus scent to them to fring extra freshness to the room! Added chlorine tablets to evap coil drain pan and condensate pump. Checked mechanical and electrical components, all in good shape. Found main level and upstairs system low on charge, recharged systems, added in leak sealers, replaced voltage absorption systems, and added in performance enhancement systems. Systems are both at ten degrees superheat and amp draw to compressors has been improved. Customer also upgraded tune up to 3 system maintenance plan. Since customer got 2 platinum packages, it will come with two years of maintenance, covering the year of 2018 and 2019. If customer wants to renew maintanence plan, she will be up for renewal summer of 2020. Found no surge protection, recommend adding on to protect units from lightning strikes and power surges. Systems operating normal at this time.
2 system ac tune up complete. Changed filters and added a nice citrus scent to them to bring a little extra freshness to the house! Installed unions on drain lines and cleared lines. Added chlorine tablets to drain lines to help clean lines. Checked mechanical and electrical components, all in good shape. Gave condenser coils a chemical wash and applied rust proof waxing. Recommend surge protection to protect units from lightning strikes and power surges. Recommend Apco uv light systems to prevent mold, kill bacteria and viruses, and reduce volatile organic compounds. Recommend performance enhancement systems to reduce load on compressor, help the system to operate smoother and help with electric bill. Systems operating normal at this time.
Replaced 40amp breaker on a Amana Ac system. 410a Puron refrigerant charge running properly.