Reece was very courteous and professional!
Your MAN was courteous, fast, and efficient. We really liked him. Looking forward to our duct cleaning.
I've always had professional service and have been happy with the furnace and air-conditioner.
Couldn't expect better.
Tech did the work we asked for promptly and told us what he was doing each step of the way.
Paul showed up right on time, very polite,knew just what to do.
Reece was prompt, courteous, professional, and explained what he accomplished during tge service call.
As always, great service and knowledgeable service tech (Reece).
Ask for technician Ta Kim.
2 heating system pm check complete. Changed filters. Tested mechanical and electrical components, all in good shape. Recommend apco air purifiers to keep evaporater coils clean and to kill mold, bacteria, germs and viruses for improved air quality. Recommend surge protection to protect units from power surges. Systems heating normal at this time.
Completed maintenance on newer furnace. Found loose connection on zone damper for upstairs, fixed issue and tested system. Found piece of paper stuck in blower wheel removed paper and everything operating normal at this time.
Found bad gas valve. Older Armstrong furnace. Smart valve gas manifold needs replacing
Completed maintnenace on 2 systems. Changed filters, checked all electrical, mechanical and safety's. recommend blower wheel cleaning and air handler cleaning on basement system due to dust build up. Both units are operating normal at this time.
1 furnace pm check complete. Changed filter. Tested mechanical and electrical components, all in good shape. Found co level at 85 ppm, recommend recalibration to lower co levels. Recommend low level co detector. System is heating normal at this time. Recalibrated system for lower co levels.
Found unit not safe due to heat exchanger issue. Customer wants to replace 2 ton gas package unit. Collected money through green sky financing.
Performed 1 system heating maintenance. Very bad black mold problem. Airhandler needs u/v lighting system to kill mold and bacteria. Filter is a ultravation 20x25x5 and needs to be replaced in the spring. Flushed drain line. System is operating properly at this time.
The bottom high limit switch directly beside the burners was set off. I reset the high limit and checked a variety of sub systems to see what may have triggered the set off. All of the system's components are performing within normal range with no obvious sign of the cause.
Replaced rollout switch on gas package unit. Recommend new system due to burners and heat exchanger completely rusty. Inducer and blower motor has high amp draw. Heat is operating at this time.
Completed maintnenace on both systems. Customer complaining about noise issue one of vents is rattling tightened vent to ceiling and problem seems to be fixed. Both systems are heating normal at this time. Customer interested in duct cleaning $850 for first and $650 each additional.
Completed maintenance on Amana distinctions furnace.
2 furnace pm check complete. Left customer with replacement filters. Found main level blower motor controller running weak, recommend repair. Main level system operating at 70 ppm co. Upstairs furnace is slightly under fire. Recommend recalibrations. Tested static pressure and got good readings. Dusted furnace cabinets. Systems are heating at this time.
Found bad pressure switch in 1998 furnace. Recommend replacing furnace customer wants repair only at this time. Replaced pressure switch and everything is operating at this time!
Replaced blower motor capacitor. System is currently heating.
2 heatpump pm check complete. Changed upstairs filter and main level aprilaire 810 media filter. Upstairs airhandler has a weak blower motor controller. Main level system is in good shape. Systems are heating at this time.