I was very satisfied with how friendly, knowledgeable, & clean my technician Christian was when servicing my AC and furnace. They also had the best price around my area!
He is always so professional! Very knowledgeable and explains everything with options!! Highly recommend
The technician who performed the seasonal service on my HVAC system was professional, very knowledgeable, and friendly. He explained what he was checking and answered all my questions.
Reece was very knowledgeable and explained everything very well, that’s why I requested him
Helpful in answering all questions asked.
He worked very hard to resolve my issue
He knew what to do, find the problem in good time, good information in why the part felt. Thank you.
Jon did a great job and we are very happy with the service he provided
Sign 2 CCI plan. Replace disconnect box for package unit. System operating at this time. Find kitchen ac unit operating but with worn/pitted contactor, fan blanace balances and stress compressor. System operating, customer want to keep check on old system and not replace it yet. Complete pm check. Upgrade $98 tune up That was done on 03/30/2020 to CCI plan. Customer pay the difference.
No cool. Found system with clogged filter, changed filter. Tested mechanical and electrical components, found weak blower capacitor. Found evaporator coil to be rusty, corroded and freezing up due to very low r22 pressure. R22 is a refrigerant that has been phased out by the epa. System has no water safety and is therefore not up to code. Main electrical switch has electrical pitting present. Due to age and condition of system and cost of repair, recommend upgrading system to a more reliable, more efficient system. System is not cooling at this time. Customer used $30 off first time customer coupon.
Performed cooling tune up checked electrical, mechanical components, dusted electrical cabinets, changed filter, chemical washed outdoor unit. Found weak capacitor recommend replacement. Recommend start assist kit for outdoor unit. Recommend back up water safety. Recommend surge protection for both units. Recommend pureairx for indoor air quality and prevention of mold growth. System is cooling at this time.
Arrived on site to preform one system maintenance. Indoor: checked all wiring and connections, checked amp draw and capacitance on blower motor, filter is new. Blew out drain line. Outside: checked amp draw and capacitance on motors, checked all wiring, made sure refrigerant pressures were within manufacture spec, cleaned off outdoor coils. Unit is operating within manufacture spec at this time.
Arrived on site to preform a 2 system maintenance, gave quote on duct cleaning with blower assembly and coil cleaning at the customerâ€™s request. Upstairs: found filters completely clogged (changed 2 16x25x1). Both blower motors dirty running on 7.5uf capacitors (reading 4.3-4.2uf). Dirty evaporator coils on both, causing coils to start freezing. Outdoor: both units have duel run capacitors reading low and older system has a burnt and pitted contactor. Both units refrigerant systems are reading lower than normal pressure.
Completed diagnostic on main floor. Indoor system is 15 years old outdoor is 9. Compressor has failed. System running on r22. Indoor system has no water safety and coil is very rusted and likely leaking. System needs to be replaced. Having Garrett come out to give quote on replacing.
1 system cooling pm check complete. Found system not operating upon arrival due to burnt out transformer and main electrical switch that was popping the fuse. Replaced both and restored cooling. Changed filter. Tested mechanical and electrical components. Chemically washed condenser coil. System is cooling at this time.
Arrived on site found blower motor not running. Quoted for replacement. Customer denied replacement
1 system cooling pm check complete. Changed filter. Dusted out electrical cabinet. Tested mechanical and electrical components, all in good shape. Recommend surge protection to protect equipment from power surges. Chemically washed condenser coil. System is cooling normal at this time.
1 system cool pm. Cleaned outdoor coil and checked all components. All components are in good shape. System cooling well but really needs duct cleaning. Bill renewed membership and wants to move forward with the duct cleaning. Please call and schedule. Paid in full
No cool, check and find furnace power switch damage, replace under warranty from install. Check system and charge system to manufacturer spec. System operating at this time. Warranty service call. No charge to customer.
Installing over windows.