Jon was outstanding! Very thorough, personal, professional and knowledgeable! Also recommended a couple of things I will address in the near future.
Chris came today to check out my Heating unit because I have a problem with my gas bill. December bill was $62.98, January bill was 180.79 and February Bill already paid is 338.71. When I called Ga Gas Co to find out why my bill is so high, the customer service person said I probably set it too high. I keep the temp at 71 and 68 when I leave house. Chris checked out entire system and gas meter outside. Everything looked good. I only use gas for gas heat Chris said leave on 71 and let’s see what next bill reads. If high again , I may have to call gas person to check out. Chris could not find a problem anywhere. I feel he was very thorough.
Very friendly and knowledgeable
Comfort Control installed my HVAC system and upgraded my ductwork. They have done the seasonal maintenance on my system ever since. Always friendly and professional and in the these times of Covid they took steps to keep us and then safe. I highly recommend them.
Reece is friendly and very knowledgeable. He solved our problem, and explained everything to us, in easy-to-understand terms.
Great service, quick, and communicated great!
Heating tune up flowery branch. Completed tune up on 5 year old system. System is very clean inside. Customer is going to replace filter. Air flow is ok. Customer has problem with master bedroom not getting as warm as living room. Slightly low cfm reading. Recommend redoing ductwork above room and adding high velocity vents. System has no secondary water safety device to protect system from water damage. Customer also wants quotes on water heaters.
Heating tune up flowery branch. Both systems 7 years old. With slight dust build up on blowers. Evap coils very clean. Changed filters. Air flow is good on both. Heating elements working properly and clean. All electrical components working good. System missing secondary water safety switch to protect furnace from water damage. Systems also missing any form of indoor air quality treatments. Sending estimates for both to customer.
Customer called the wrong company to come out. Will call back after they get original company to see if they can fix it
Heating tune up in Flower Branch. Tested operation of 2 systems. Upstairs system components all tested within normal manufacturing spec. Discovered beginning stages of organic growth in ductwork. Recommend ultraviolet light system to combat organic and viral growth in system and throughout the home. System would also benefit from a duct cleaning. Downstairs system has a weak blower motor controller, is extremely old and will needs to be replaced soon. Homeowners will sign up for membership in the spring
Free consultation flowery branch georgia 30542
Heating tune up in flowery branch. Tested operation of 1 system. Discovered compressor running at higher amps and system heating but not as effective as it should. Discovered blower wheel dirty and motor pulling high amps. System has no water safety and ducts need cleaning. Due to age and condition of system replacement is HIGHLY recommended. Homeowner would like phone consultation for estimate on replacement
No heat in flowery branch. Check and find flame sensor fail. Test and find system operating with weak blower capacitor, missing in-line water protection. Replace furnace flame sensor and system operating at this time. Suggest comfort control care club, suggest in-line water protection for system in attic, suggest surge protection and air purifier system.
Heating repair in Flowery branch. Tested operation of 1 system. Discovered outdoor unit locked out on high pressure. Reset system and ran for 30 minutes with no issue. Recommend new compressor saver hard start to help compressor start and overcome pressure in system during cold winter months along with surge protection for system. Installed new compressor saver and signed up for maintenance membership
No heat in flowery branch. Discovered pump vinyl tubing outside oriented with trap and water inside froze forcing pump to shut everything down on safety. Remove trap from vinyl tubing system draining properly now and heating. Homeowner wants price on Generac whole home generator
Heating tune up in Flowery Branch. Tested operation of 1 system. Discovered system with heavy a,out of organic growth, dirt blower wheel, dirty ductwork, no water safety, weak secondary controller, failing outdoor fan motor, worn main electrical switch, bypassed outdoor disconnect, compressor sounding rough, and dirty indoor coil. System is is rough shape and is 15 years old. Typical lifespan of a system is 10-15 years. Due to high repair cost replacement is HIGHLY recommended.
Heating tune up flowery branch. Completed tune up on 9 year old system. System heating and cooling properly. Blower is a little dirty. System has no water protection. Air flow and combustion is good. Pressures and all electrical components are good. Installed inline float switch and compressor saver to system.
Warranty flowery branch. Completed ac tune up. System cooling very well pressures are perfect. All electrical components working within range. System has no compressor saver to take load off compressor during start up or surge protection. Recommend both.
Heating tune up. Found 2 year old furnace running properly. Coil and blower very clean. All safety switches working. Changed filter. Insulation in attic is good. Air flow is ok. Combustion is good. System heating properly at this time.
One system heat maintenance in Flowery branch. Arrived on site, cleared barometric ports, checked ignition systems, electrical connections, amp draw and capacitance. Found outdoor unit fan motor drawing higher than normal amp as well as a burnt and pitted contactor. Recommended replacing these parts as well as adding surge protection to both pieces of equipment to protect electrical systems from surge and an attic tent for the attic stairs to prevent heat transfer into unconditioned space. . Unit is operating normally at this time.