Great customer service.
prompt knew who was coming update and picture Great job
Response time was outstanding. A/C not working so I called to schedule appointment time (between 3 to 5 PM). Reece called and arrived much earlier. He checked system and made repair immediately. He answered several questions. Would highly recommend Company and Reece.
Service tech Christian was excellent. From beginning to end, this was quite a pleasant experience. He called to advise of arrival time, and was right on time. Once here, he repaired the issue quickly, and was extremely polite and friendly. The price was more than fair! My first time using this company, but definitely not my last. Thanks Comfort Control, and Christian for great service!!
Charged my system and was very nice.
We had a tech at our house within 2 hours of calling for an appointment. Mark, the AC tech, was awesome. He was thorough, knowledgeable, and took time to answer all of my questions. He was kind and respectful. I would call them again.
Good info given.
Heating maintenance flowery branch. Completed heating maintenance. Found everything clean and working properly. Flame sensor is discolored but still working within spec. Capacitor is good. Blower whee is clean. Cleaned induction port. Changed filter. Zone board working properly. System heating at this time.
Heating maintenance flowery branch. Completed heating maintenance on 4 year old system. Everything turning on properly. Flame sensor is clean. Cleaned inducer port. Combustion is good. Sold box of 4 replacement filter. Blower wheel is clean. Capacitor is good. Showed customer how to work dampers on ducts at the plenum. System is working properly.
Heating maintenance flowery branch. Completed 2 system maintenance. Main floor furnace is 12 years old and has good blower with new filter. Inducer motor is good. Cleaned inducer port. Flame sensor is good. Ignitor has silicon build up. Burners have slight rust inside and around openings. If rust gets bad enough it will make a hole and allow carbon monoxide slip into house. Systems are heating properly at this time.
Tune up flowery branch. Completed 2 system tune up. Found both units 7 years old. Upstairs has clogged drain line and very dirty filter. Changed filter cleared drain line that was causing water damage. Downstairs system has clean blower wheel and coil. Replaced filter and added algae tablets to pump downstairs. Both systems have good pressures and are cooling properly at this time.
Heating maintenance flowery branch. Completed one system heating maintenance on 2 year old furnace. Blower is clean. Capacitor is good. Flame sensor and ignitor are both clean. Heat chambers of no sign of rust. Changed filter. Combustion readings are good. Cleaned inducer port. Gas line is up to code. Zoning is correct. No signs of leaks in duct work. System heating properly at this time.
Water leak flowery branch. Completed diagnostic. Found drain line clogged and secondary water switch tilted up and would not activate causing excess water to drain into system and down return duct. Cleared drain line. Reset switch and cleared return box of water and re sealed return duct. System cooling at this time.
No cool 20 year old heatpump system in flowery branch. Check and find Armstrong Evaporator coil in atttic freezing up and leaking charge. Find system housing dirty, and water in side system and drain pan, customer have no water protection in attic. Find heatpump system operating with worn pitted contactor, and compressor operating with high power usages. System 20 year old operating in poor conditions, suggest to replace system and not repair. Customer want to add charge for today visit and also need consultation visit.
Ac service flowery branch. Completed diagnostic. Found drain line clogged at p trap. Cleared drain line. Evap coil has no signs of freezing. Ensured condensate draining properly. System has concerning amounts of mold in and around system. Recommend pure air treatment installed to kill mold bacteria viruses and allergens that could cause harm to residents. System has no water safety installed recommend inline float switch to turn system off in case of clogged drain line. Outdoor unit has good pressures. System not low on refrigerant. System cooling at this time. Customer needs hard copy mailed to her.
Ac service flowery branch. Completed diagnostic. Found bad thermostat and wired wrong at thermostat. Replaced thermostat and wired correctly. Tested system. System cooling at this time.
ac service flowery branch. Completed diagnostic found capacitor dead on compressor side. Replaced capacitor under warranty. System running at this time. Will pay service Wednesday morning.
Ac repair in Flowery Branch, Georgia. Found system with bad blower motor. System is a zoned system and has no bypass damper like it is supposed to. Ductwork is undersized. Recommend replacement of blower motor, Installing an 8â€ return, installing a 10â€ bypass damper, and installing a 10 inch supply duct that branches out into two 8â€ ducts upstairs. Customer just wants to replace motor for now. There is no labor warranty on motor because of undersized ductwork and no bypass damper, customer understands that. Replaced blower motor and system is cooling at this time.
Signing family up for a two system maintenance:) . Checked safety and the performance of the cooling equipment. Completed chemical washed on both outside coils . Concerns found today will be below ... â€¢Downstairs system is very low on R22 due to a leak in the system . The system has hardly any pressure in the system . Would highly recommend upgrading the system due to age and with the R22 phase out by the EPA . â€¢Downstairs outside dual start cap is getting rusty and could eventually leak oil would recommend replacing that electrical part . â€¢Downstairs doesnâ€™t have any form of water safety would highly recommend to prevent water damage. â€¢Downstairs coil has a leak took pictures of the coil conditions . Very rusty with lots of corrosion. Would highly recommend a new system . System also has water damage inside the furnace and has bacteria growing in the system . Took pictures. â€¢Downstairs blower motor is running hot . Family is scheduling a visit for a consultatio
No cool flowery branch. Arrived on site, found outdoor unit not functioning due to bad capacitor. Replaced under parts warranty. Checked pressures and electrical systems. Unit is operating normally at this time