Dylan Wages was very knowledgeable and professional in his installation of our new A/C and Furnace systems. We had to have substantial changes to our ductwork and Dylan was able to design the new ductwork and install it along with new supply and return vents. His knowledge of the systems and skill in installation and explaining the changes was excellent. I give him and his crew the highest ratings and highly recommend Comfort Control based mainly on his work.
The serviceman arrived shortly after we called the company about our problem. He made the repairs and was finished in quick time. His name was Ta.
Quick repair and great service z
i WANT PAUL TO DO ALL FUTURE SERVICE.
I would like Paul Cobb to do all of our HVAC service. He has the knowledge of HVAC equipment which I require.
I couldn’t be happier with the service I received. Reece was knowledgeable, professional and courteous.
Great service !!! Very good Price and a wonderful technician, Reese Wilson !!!!
they are on time, do great work at a fair price. and answer any questions you may have. We love this company. Greg&Cathie Scott
Signed for new contract. Replaced filters, checked electrical and safety switches all ok at this time. Did a combustion test on both furnaces and all within range. Main floor system has high static pressure( space is very limited to add more return air).clean both dirty filter for mini split. Tested and working normal
1 heatpump pm check complete. Left customer with replacement filter. Taped hole in supply plenum. Tested mechanical and electrical components, all in good shape. Recommend surge protection to protect unit from lightning strikes and power surges. System is heating at this time.
We installed a 4 ton condenser with a 100btu furnace. We replaced all plenums and junction boxes. We added one 10" return and one 6" supply. The system has been set in a water pan and has two water detection devices. The system comes with 10 year parts and labor warranties. You must be on continuous maintenance the full 10 years to get the full labor warranty. We must return and change a 6" boot's grill out with a high velocity grill. The grill size is 10x6".
We replaced the system under full warranties. I put the system on single stage only for now.
Adding 1 10 inch return in living room. Sealing all ducts and removing distribution boxes to optimize airflow ASX160481 CAPF4860C6 AMVC81005CX Aprilaire 8466 Labor Warranty (years) (10) X Parts Warranty (years) (10) X Compressor Warranty (years) (Lifetime) X Heat Exchanger Warranty (years) (Lifetime) Bring an 8 10 and 12 inch high velocity register to put in uncomfortable living room
Gave free estimate for a new HVAC system.
Came to assist tom with water removal from drain pan
2 bedrooms Upstairs not getting enough heat. Daughter's room had to much slack on duct work. Cut off about 3 foot of duct work. Both rooms now have great air flow. Heating normally.
No heat/ not keeping up with temperature. Found 13 years old 4 ton heatpump system. Found rusty and leaky evaporator coil. Found system low on freon do to leak at the coil and compressor draws high amps. System is old,phaseout freon and needs to be replace. Owner just wants repair for now. Charged system to manufacture recommend specification for hot gas method, added leak seal to system and installed a hard start kit for compressor. Test system and heatpump and heat strips working normal
Found basement system ignition system to be broken and has a worn flame safety, recommend repair. Replaced ignition system and flame safety and system is heating. Signed customer up for 4 system maintenance plan- 3 systems and 1 mini split system. Main level flue pipe is single wall and therefore not up to code. Main level gas line going into furnace is flex and therefore not up to code. Put new batteries in basement thermostat for customer. Washed mini split filter. Upstairs gas line is also not up to code. Upstairs blower motor controller is running weak and flame safety is failing, recommend repairs. Replaced blower motor controller and flame safety on upstairs system. All systems are heating at this time.
We cleaned the mainfloor and lower level of the home. I gave a $50 military discount. I quoted
No heat on the downstairs system. Found system with bad control boards. replaced board and system heating normally. Ignition and flame safety sensor getting worn. overall, the system is heating normally.
No heat on the downstairs system. Found system with a bad control board. Replaced board and system heating normally. Ignition and flame safety sensor getting worn, overall system is heating normally
Performed 2 System Maintenance. I recommend both systems have a hard start kit added. Both are heat pump systems and the compressor is under twice the stress as a split system.
Completed maintnenace on both new furnaces. Changed filters and checked all electrical, mechanical and safety components. Both units are operating normal at this time!