Amazing service and explanation of what was being done. Great help and really went the extra mile. Vu was outstanding.
great job chris thank you.
Reece was informative thorough and got my air up and running
Awesome! He did a fantastic job
Very good work manners nice guy thank for sending some one that’s got it together and knows what he doing he even done things that other companies have never done the invoice is not the same as what was taken out of my account I need to know the difference 323. On invoice 362. On my bank
From time of first call, to our completed service time, was less than a week!
Very professional and got the job done quickly.
On site found secondary motor controller not operational. Replaced controller system came back on. Found dirty blower wheel recommend to pull and clean. Found dirty evaporator coil recommend to clean in place. Recommend adding back up water safety to system to protect against water damage. System is operating and cooling at this time.
Completed diagnostic. Found zone damper to master bedroom stuck open. Need to order new damper and return to replace.
Water basement system, find drain trap semi clogged and water over floating. Remove trap and check drain. Find drain pan secondary drain port missing cap and missing in line water protection. Suggest installing in-line water protection. Suggest to clean evaporator Airhandler due to molds growth. Customer declined at this time. Suggest CCI plan.
Performed cooling maintenance checked electrical, mechanical components, dusted electrical cabinet, chemical washed unit, cleared drain line, changed filter. Found dirty blower wheel recommend to pull and clean. Recommend adding back up water safety to furnace to protect against water damage. Recommend adding surge protection to both units. Recommend start assist kit to condenser. System operating and cooling at this time.
Replaced outdoor secondary controller, added compressor saver and surge protection for outdoor unit. System operation normal at this time
Arrived on site, found outdoor unit completely clogged (seems like it hadnâ€™t been washed with the maintenance) washed it with chemical and checked pressures. Unit is operating normally at this time
No cool. Found system with bad capacitor, burnt contractor and bad breaker. Replaced all three and system is cooling at this time. System is 20 years old and compressor is pulling above maximum rated amp draw. Due to age and condition, recommend replacing system.
Found bad txv for downstairs system. Customer wants to replace equipment. Sending Garrett out for a free consultation.
No cool main level system. Found bad blower capacitor causing system to not turn on. Replaced blower capacitor and system is cooling at this time. Found mold inside air handler, recommend pureairx air pump to kill mold, bacteria, germs and viruses for improved air quality. Recommend surge protection to protect equipment from power surges. Thank you so much for your business today! It is greatly appreciated! Its customers like you that keep us in business and keep our families taken care of! If you were happy with your service today and you wouldnt mind, please take a few minutes to give us a 5 star review on google! All you have to do is go to google.com and sign into your google account. From there, search for â€œComfort Control Heating and Airâ€. Click on â€œReviewsâ€. Write your review mentioning me, Reece Wilson and please be sure to leave 5 stars! Thank you so much and have a great day!
No cool main level system. Tested system and found the following: Evaporator coil is very rusty and corroded and therefore likely to leak. Blower wheel is dirty. Systemâ€™s water safety is code compliant but it has no overflow protection switch as a backup to primary water safety. System is not cooling due to bad capacitor (55/5 uf). Found main electrical switch in bad condition with electrical pitting present. Existing hard start kit has gone bad as well. Due to age and condition of system, recommend upgrading system to a more reliable, more efficient system. Customer just wants repair for now. Replaced capacitor, main electrical switch and hard start kit. Pulled and cleaned blower wheel. Installed overflow protection switch. System is cooling at this time. Signed customer up for two system maintenance plan. Thank you so much for your business today! It is greatly appreciated! Its customers like you that keep us in business and keep our families taken care of! If you were happy with y
4 and 5 ton Variable speed 20 seer. Need to return to replace txv for main level system
Complete 1 system a/c repair and preventative maintenance check. The customer is interested in air purification. Left pamphlet for pure airX products. The furnace is good with clean blower and working electrical components. The filter is good. Could is clean with 2 forms of water safety that both work. Cleared drain line. The outdoor unit is clean. Has great pressures and working electrical components. The system has no compressor saver or surge protection
Complete 1 system a/c repair and preventative maintenance check. Cleaned outdoor coils and checked all components. Discovered the outdoor unit has a weak secondary controller and needs a compressor saver hard start kit to reduce stress on the compressor and reduce energy consumption on startup. Also the unit needs surge protection. System cooling at this time.
A/c repair call. Tested system and found very rusty, corroded evaporator coil. Found system with no water safety switch and is therefore not up to today's code. Found dirty blower wheel. Filter was dirty and clogged, changed filter. The system is low on r22. Customer wants to recharge system for now until it can be replaced. Recharged the system with 4 lbs r22. The customer understands there is a leak and that refrigerant will leak back out again. No guarantee on how long the refrigerant charge will last. The system is cooling at this time.