Water leak. Check and find water leak due to clogged drain system. Cut and repair drain, flush drain and clear drain with water safety HF3B and remove water out of drain pan. Sign up 1 plan with comfort control inc. complete cooling pm check. Did not change filter. Clean ac coil and add r22 to help system cool better. Insulate suction line for outdoor unit. Find main circuit voltage supply box burnt and damage, customer want to wait to repair main circuit and will call Comfortcontrol inc back to replace main circuit and no service fee to come back. System operating at this time.