Great job. On time. Professional.
Everyone was so friendly from the operator to the scheduler and John!
Wonderful. He explained every little detail how it could be fixed
He is great! Excellent service
Great took the time to explain how they know how much freon to put in.
I would recommend Comfort Control to anyone.
wanted the system for $4000
Install pendergrass. Completed install of pureairx filter in airhandler. Tested to make sure it came on. System working.
Heating maintenance in pendergrass. Completed heating maintenance. Found all systems working properly. Customer wants electro static filter. Ordered filter will return to install.
$300 tax credit $400 Jackson emc rebate $375 manufacturers rebate
Completed inspection. Found outdoor unit level. All electrical components are good. Amps on motors are good. No overheating. Pressures are good. Indoor system has clean blower and coil. Cleared drain line. System cooling at this time.
Completed diagnostic found bad capacitor at heat pump. Replaced capacitor. Checked pressures according to target superheat. System cooling at this time. System missing compressor saver and surge protection. Owner is moving in a month. Does not want to do upgrades.
1 system ac tune up complete. Changed filter. Chemically washed condenser coil. Tested mechanical and electrical components. Found system with no water safety and therefore not up to code, recommend adding water safety to protect ceiling from potential water damage. Found blower capacitor to be weak. Found blower wheel to be dirty. Found ductwork to be dirty. Found evaporator coil to be very rusty and corroded and likely to leak. Found black mold in system. Found static pressure to be high at 1.11 in. w.c. When maximum rated static pressure is 0.5 in. w.c. Ductwork is undersized which is the cause of the high static pressure. Refrigerant pressures are as good as they are going to get with airflow not being properly balanced. Due to age and condition of system, recommend upgrading system to a more reliable and more efficient system. Recommend pureairx air purifier to kill mold, bacteria, germs and viruses for improved air quality. System is cooling at this time.
Completed one system maintenance. Found i door unit running very clean inside system. Blower running at good amperage. No restrictions in air flow. Changed filter. Left algae tablets in condensate pump. Cleaned outdoor unit. Pressures are good all electrical components working good. System has no compressor saver or surge protection. Inside system also has no back up water safety.
Completed one system maintenance found indoor with back up water safety and clean blower. Cleared drain line. Filter is new. Wiped everything down with Lysol wipes. Outdoor system has good pressures and all clean and working electrical components. Missing compressor saver and surge protector which will increase life expectancy in system and better protect it as well.
Complete 1 system furnace repair and preventative maintenance check. Found air handler with no power. The breaker is not tripped but nothing operates. Found blown fuse. Put new fuse and system came on the. Runs and blown fuse. Tested all wires and couldn't locate any wiring issue. The system is operating at this time
Complete 1 system furnace repair and preventative maintenance check. We added freon to summer time. Did a leak search at the evaporator coil and did not detect a leak. We will have to double-check pressure summertime for more accurate pressure.System heating at this time
Complete 1 system furnace repair and preventative maintenance check. found no issues. The system is heating properly
Complete 1 system a/c repair and preventative maintenance check. Recharged basement system with 1 lb r22. The system is cooling at this time.
Complete 1 system a/c repair and preventative maintenance check. Did not change the filter. Tested mechanical and electrical components, all in good shape. Recommend hard start kit to reduce the load on the compressor to help extend the life of the system. Recommend surge protection to protect the system from power surges. The system is cooling at this time.