Great service as usual
The technician, Jon, arrived early and after a couple minutes diagnosed the problem. He quickly resolved the problem and was done in less than 30 minutes. I will be using Comfort in the future.
We had an issue with main AC unit one day before a (potential) buyers pre-sale home inspection. Our tech, Vu was very professional, very knowledgeable and most importantly he delivered on what he said he’d do.
no problem, good to go
Excellent work Vu!
Mark, the technician, was courteous, friendly and professional. He took time to explain the problem to my understanding.
Chris was a very courteous technician and did a great job for us.
Free consultation for new hvac system in snellville
Complete heating maintenance on Rheem system in snellviell. Change filter customer provided. Check safety and operations. Find inducer assembly worn and making noise. Need to keep check on motor. Customer want to keep check on system and may replace system next next. System operating at this time.
No cool upstairs main system In Snellville. Check and find 2 year old system drain line clogged. Flush and clear drain and add drain pan treatment. System operating at this time.
One system heat maintenance in Snellvill, arrived on site, found new furnace we installed. Checked ignition system, combustion analysis, electrical connections amp draw and capacitance. Unit is operating normally at this time
Ac service snellville. Completed diagnostic. Found bad capacitor outside. Replaced capacitor. System is running. Amps are good on motors. Contactor is clean and pressures are perfect. System cooling properly at this time.
Free hvac replacement consultation snellville Georgia
3 system tune up in Snellville. Indoor, changed filter and cleared drain line, checked electrical connections, amp draw and capacitance. Found all coils rusted, corroded and dirty due to most of them not having filters in them. Blower motor assemblies are all dirty for same reason. Water safety is missing on main level and basement and capacitors are all out of spec. Outdoor, checked refrigerant pressures, electrical connections, amp draw and capacitance. Found basement system condenser fan motor completely locked up, capacitors week on all three units, Pressures are off due to condition of evaporator coils. Cannot recommend repair due to age and condition of systems, recommended replacement on all 3 units.
Completed consultation snellville. Gave customer estimate for duct cleaning for both systems. Duct cleaning will include. Cleaning ducts, plenums, boots, and vents on both the return and supply side as well as include micro bacterial sanitizer to ensure all duct work is mold free.
Heating tune up in Snellville, Georgia. Customer as wondering why fan for system was running at night. Found fan set to â€œonâ€ on thermostat, switched it to â€œautoâ€. Performed heating tune up while I was here per customer request. Tested mechanical and electrical components and found no issues. Changed filter. System is heating at this time. System only has furnace, customer has no ac. Recommend installing condenser and evaporator coil so home has central air conditioning. System is heating at this time.
No cool in Snellvill, found r22 system has no refrigerant due to a large leak. Found numerous other concerns, recommend replacing equipment due to age and state of equipment.
Service call back. Find furnace control fail and calling for inducer assembly to operate without calling for heat. Customer will order and replace control board. System operating at this time.
Replace main system evaporator coil. Pressure test, vacuum and replace system to manufacturer spec. System operating at this time. Clean ac system for customer.
No cool main system. Find system frozen. Find evaporator coil badly rusted and leaking charge. Sold new coil and cci plan. Need to schedule to come back and replace evaporator coil and complete cooling pm check. Add charge so customer can have cooling til coil replace.
Arrived on site, found upstairs unit not running with no high voltage going to furnace. Found wire nut melted at line voltage. Cut back burnt wire and replaced wire nut, unit came right on. Recommend installing surge protector to each unit and signing up for maintenance to clean outdoor units. Checked electrical connections, amp draw and refrigerant pressures. Unit is operating normally at this time.
On site found system to be cooling and operating. System is zoned client stated that upstairs was not cooling tested zones are opening and operating. Found system low on refrigerant recommend a leak search. Client request refrigerant be added to system approved 3 pounds. System is operating and cooling at this time. Recommend to add back up water safety switch to system. Recommend to add surge protection to both units.