Va has to be your best heating and air technician. He always knows what to do. Very experienced and helpful in explaining everything
Your technicians are well educated in what they do
He did a great job
Vu has been caring for our systems for at least 8or 9 years. We are always happy to see him because we trust his work and his advice. As a result, we don’t have surprise break downs mid-season.
Vu was on time and wasted no time getting to work. He informed me of what he had found on his inspection of the furnace and gave me recommendations for work that may need to be done in the future. Vu made a service call to my house last year as well, and I am overall pleased with his work.
Great service as usual
The technician, Jon, arrived early and after a couple minutes diagnosed the problem. He quickly resolved the problem and was done in less than 30 minutes. I will be using Comfort in the future.
We had an issue with main AC unit one day before a (potential) buyers pre-sale home inspection. Our tech, Vu was very professional, very knowledgeable and most importantly he delivered on what he said he’d do.
no problem, good to go
No heat new installed gas furnace in snellville. Check and find gas valve not open all the way, find furnace operating with high co level and fan speed not set properly for system. Complete combustion calibration service for new gas furnace, open gas valve, balance system and adjust airflow for customer. System operating at this time. Warranty service call. No charge to customer.
Replaced Mercury thermostat with T4 thermostat in snellville (per Jeff)
Heating issues in Snellville Georgia. Arrived and looked further into the heating system and found the heat exchanger has a hole and several hair line cracks on the heat exchanger. Would highly suggest replacing the heating system . Scheduled a consultation.
Pilot had to be relit . If the pilot goes out again in the near future would highly suggest replacing the gas valve or replacing the heating system . Family is aware of the situation with the system .
Complete new heating maintenance from install in snellville. Find new Amana gas furnace operating with in manufacturer spec. Replace media air clear customer provided. Check air purifier system. System operating at this time.
Renew 2 comfort control maintenance plan. Complete 2 heating maintenance in snellville. Change both filter, check safety and operations. Find both carrier gas furnace operating with in manufacturer spec.
No heat in snellville. Check and find pilot light off due to miss Alignment. Connect set pilot and light gas. Warranty service call, tech was out 09/23/2020. No charge to customer
Furnace maintenance in Snellville, Georgia. Two systems. Changed filters. Tested mechanical and electrical components. Found upstairs igniter operating with low resistance and flame safety sensor starting to get weak, recommend repairs. Replaced upstairs igniter and flame safety sensor. Systems are heating at this time.
Complete 2 heating maintenance in Lilburn. Find main system Lennox gas furnace operating with in manufacturer spec. No concern at this time. Find new mini split system operating with in manufacturer spec. Clean filter and add coil protectant. Both system operating at this time. Replace main system apco uv bulb.
Complete heating pm check in smellville. Change filter, check operations and safety. Find Trane furnace operating with weak flame sensor and inducer assembly starting to make noise. Need to keep check on inducer assembly, suggest to replace flame sensor. Replace flame sensor.
One system heating tune up Snellville, arrived on site to find main level unit not operating, found limit switch tripped on inducer housing, reset and blower motor came on. Turned motor to auto at thermostat and unit stopped operating, had high voltage going into board, but would not start heating cycle. Also found blower motor leaking oil. Recommend replacing unit due to condition and age.
Free consultation for new hvac system in snellville
Complete heating maintenance on Rheem system in snellviell. Change filter customer provided. Check safety and operations. Find inducer assembly worn and making noise. Need to keep check on motor. Customer want to keep check on system and may replace system next next. System operating at this time.
No cool upstairs main system In Snellville. Check and find 2 year old system drain line clogged. Flush and clear drain and add drain pan treatment. System operating at this time.
One system heat maintenance in Snellvill, arrived on site, found new furnace we installed. Checked ignition system, combustion analysis, electrical connections amp draw and capacitance. Unit is operating normally at this time