Billy really took care of me and did and excellent job! I am very happy with my service
Billy did a great job servicing our units. Also educating me on his findings as well as future replacements.
GREAT SERVICE... VERY PROFESSIONAL
Tech was very nice and put covers over his shoes
Great service, explained what was wrong and fixed it
Brad Gowan was excellent. He was friendly and knowledgeable. Most importantly he was honest. Thanks Brad!
Billy is very nice, knowledgeable and completed the work quickly.
Future need please send brad, great customer service
replaced compressor on trane heat pump AC split system.
Adjusted txv on amana split heat pump
Complete: Came to repair wires on Nest Outdoor camera. Repaired wire. Went inside to check breaker and it was ok. So I locked the deadbolt on the doorlock upstairs and on the one going into the garage. I exited the garage and pushed the door down a little further after it had closed. Camera should be should be good to go now.
Working on amana heat pump.
Incomplete: 1 System: Lennox Split HP:HO said she found Condenser frozen over night of 25° weather. Checked charge it looked fine checked defrost board. Found board 24v coming into the board. Could not get defrost board to go into defrost mode. Need new defrost control board.
Rest fan limit on Trane gas furnace
Ruud hp check
Apollo system lines crossed
Rheem heat pump diagnosed bad wiring terminal
Comfortmaker gas furnace checked system found bad smart value need to replace smart gas valve
Trane gas furnace Replaced faulty inducer motor assembly
Water Heat Pump
performed preventive maintenance on Goodman gas pack
Payne heatpump changed blower motor
No heat Payne split go