Billy was awesome. He was prompt and extremely professional. I was impressed with his knowledge and thoroughness in assessing my AC service needs. I’m requesting Billy as the assigned tech for any future needs I may have.
Professional as always me and my family thank you all for your services Bradley McLeod
Billy was awesome and answered all of our questions thoroughly. He broke down the next steps for us and explained everything so we were able to understand exactly what our needs were for the AC unit. We were very happy with Billy as our technician and request that he be the same technician that comes back for our next service. Thanks Billy
I have enjoyed the costumer service I have received from with Bill Smith and Skyler Hunter. They both were very professional.
Will refer Comfort First to others!
Cody and Elmer were very professional and I would highly recommend them. Extremely happy with their service.
Devin went above and beyond to make my install process wonderful.
Billy was knowledgeable and very thorough. I was confident that his recommendation was for my benefit.
He was wonderful he alerted me of the few things that was going on with my air condition and I thank you
Working on Goodman heat pump
added r22 refrigerant to trane heat pump pack
Incomplete 1 System Worked on a Goodman Heat Pump Split System HO said Unit was not keeping desired temperature . Evap. Coil and outside sunction lune was freezing up. Found Unit way too low in refrigerant. Unit holds 14 lbs. and 8 oz of R22 so we started a leak search but when we started rain started pouring a lot of rain. Left nitrogen at 290 psig. Need to reschedule to continue leak search. Spoke with HO completely understands and he thinks they might have been low in refrigerant for some time
Working on a Goodman heat pump
Installed 2.5 ton Goodman split system with nest gen 3 thermostat
Noise in system because of type of filter being used
Complete 1 System worked on a York Heat Pump Split System HO said Unit was not keeping desired temperature. Found a very dirty condenser coil, and broken yellow wired. Cleaned condenser coil, fixed broken wired. Checked refrigerant charge. Almost every thing is running great at this time except for one damper we found its closing and opening over and over again. Checked Static Pressure. Made sure heat strips not coming on. System is running good at this time.
performed leak search on trane ac
Bryant ac check
Carrier Split system.
Bad Cutler hammer breaker
Trane hp....no ac
Goodman ac check