I would definitely recommend Mr Manners to others for service.
We have nothing but great experience with comfort first.
Great service and a great guy
Staff are very nice to work with. i appreciate fast service, inspections before seasons to make sure everything is in order, and the knowledgeable staff
Always have a great experience with your technicians. They arrive quickly and on time, they’re friendly, and do great work. The people in your office are also great! I recommend you to everyone I know.
Justin has been great repairing our very old hvac unit. He worked with our warranty company to diagnose several problems and was persistent in getting all of the repairs done timely and with a great attitude.
Great service! Expedited service and part needed. The communications were also very good. All aspects of repair were an A+, return calls, diagnostic and repair! Thank you very much.
Great customer service.
Complete 2 Systems 2 Heating Maintenances: DS Trane Duel Fuel System: Checked tstat and air filter. Checked Blower Motor amp Checked electrical connections. No CO detected. Burners are clean. Flame Sensor is clean. Checked amparage on draft motor. All safety switches are on great condition. System is running great at this time. Checked HP Side: Checked compressor and cfm amp draws. Checked dual cap. Checked all wiring at the condenser. Checked pressures. Cleaned condenser coil. System is running great st this time. US Trane HP split System: Checked heat strips and made sure they were on. Checked blower motor amp draws. Inspected evap coil. Checked all wiring at the AH. Checked run cap. Found it weat. HO said he will call AHS. Checked compressor and cfm amp draws. Compressor is overamping. HO said he will call AHS and ddress this issues to them. Checked dual cap. Checked all wiring at the condenser. Checked pressures. Tested defrost board. Cleaned condenser coil. System is running gr
Installed split system in attic
Rheem hp heating maintenance
Trane heating maintenance
Complete 1 System 2 Zones Carrier Straight A/C: ho stated system was not cooling. Cycled system and made sure both motor dampers were working properly. Checked drain pan and made sure drain line was clear. Found bad dual cap. Used a 35/5 dual cap. from truck stock. Checked pressures. System isbrunning great at this time.
Complete 1 System Lennox AHS Heating Maintenance: cycled system. Checked tstat and air filter. Checked Blower Motor amp draw and run cap. Checked electrical connections. No CO detected. Burners are clean. Checked amparage on draft motor. All safety switches are on great condition. System is running great at this time.
Amana heatpump not working
Complete 3 Systems 2nd Floor York Straight A/C: came to test previously installed compresor. Compressor is running great. Checked pressures. System is running great at this time.