Very courteous and knowledgeable technician. Would gladly recommend your company just because of Billy’s kindness and expertise.
Billy customer service was amazing
Maintence service was performed on heat pumps. The service technician was professional, courteous, thorough, on time and addressed all the question I had. Couldn’t ask for anything better
Our technicians were prompt, friendly, and did the job! There was more wrong with my system then initially realized but they cared for it. I will highly consider getting the care plan with them for future maintence!
Good experience, David is the best
Answered my questions on my level in details I understood.
Your service technicians worked overtime to troubleshoot my problem, and did not leave until the problem was solved. It is very difficult to find good customer service today. Thanks!
Terri is the most unbelievable heating and air guy I have run into. He fixed my gas pack today. Other companies have tried to fix it even some of your tax have tried to fix it. Terri did what they could not do. Comfort first should be honored to have Terri working for them!
York package heat pump no heat
Replaced condenser fan motor on goodman heat pump
Heating maintenance on 3 Bryant heat pumps
Worked on gas furnace
Performed diagnostic on goodman heat pump
2 System EPA Maintenance: Rhudd Gas Pack: Checked the Amp Draws on the blower motor. Checked the capacitor. Checked Heat Exchanger. Cleaned burners, Flame sensor and Checked Roll out switch. Washed it cleaned it out. System looks good and working good at this time. Rhudd Split Heat Pump: Air Handler: Checked Amp Draws on the Blower Motor and Heat strips, checked the capacitor and blower wheel. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws in the fan and compressor. Cleaned Unit: System looks good and running at this time.
Working on gas furnace
Second floor gas furnace no heat carrier
Worked on heat pump
Coleman has furnace checked system found blower motor running out of balance due to trash in blower wheel and cleared and cycled system
Installed nest thermostat
Lennox furnace no heat
Carrier equipment no heat G fic tripped
Goodman furnace not heating