He was very informative and friendly
Billy did an awesome job with helping me understand the problem and issue. Very understanding and advisable.
Quickly resolved the issue
Andy did a great job to narrow down what was causing my unit not to work. Grant it’s 100 degrees and I know they just want to get home. He was very thoughtful and willingness to find out why it stopped working in the first place was a great welcome. The unit started working before even looking at it and both of us were in awe of why. But Andy didn’t just want to leave without going thru every possible reason of why it happened in the first place. Most people would have said “I don’t know what to tell you?” But he insisted we figure it out. Eventually we found the culprit and was quick to get it up and going. Thanks for your help. Andy did an excellent job!
Mr. David Miles was very kind and knowledgeable, best service that could’ve been provided!
All other technicians would put covering on their feet before entering my home. This technician did not. He asked about the thermostat and lowered my temperature. Did not return it back to original temperature I had it set on. The technician also left the light on under our house and we didn't notice it until Sunday, so the light was on for several (5) days.
Billy was great and a pleasure to work with.
Glad i only had to wait two days for service.
David was a joy to have as a technician and it was great to have a tech who knew what he was talking about. He was great with training his counterpart, Nate. A+ Technician!
We installed a 4 ton 20 seer split heat pump system
Trane low in refrigerant R410-A
Checked system found bad zone damper motor need to replace zone damper motor
performed diagnostic on Goodman heat pump AC
Comfortmaker A/C checked system found compressor out on internal over loud tryed cooling compressor and was not able to cool down and reset need to let set so compressor a d cool and reset a d be probably diagnosed
Cooling maintenance on a carrier heat pump
Cooling 3on a carrier heat pump
Repaired a Rudd heat pump by replacing the capacitor
Worked on air conditioner
Worked on Aprilaire Dehumidifier-
Carrier package heat pump checked system found to be working and maintaining temperature at this time with no machinal issues
replaced blower motor on Goodman heat pump AC
Checked Goodman heat pump system. Recommend yearly clean&service
Repaired restricted coil