Everything was handle correct
Service visit to correct a minor issue with the original inspection. Joshua did a great job to resolve the issue and even adjusted another issue not identified during the original inspection. Great customer service and more than willing to answer any questions.
I appreciate the honesty and not trying to oversell.
Very, Very professional, personable and went through out all the details in a manner I could understand. I was Very pleased with Justin and Comfort First
Justin was courteous and very helpful. Thank you! I was not happy waiting a week for service, but I thoroughly understand the demand for your services at this time of year...again, thank you!
Well pleased with service proprovi Provided.
Couldn’t ask for more professional service and courteous installation technicians great work ethics professional knowledgeable. I’d be proud to have these two representing your company
Honesty goes a long way in the service industry, you can trust these guys.
Nate showed up within the time range, he was courteous, knowledgeable, and professional, but best of all - he fixed the problem quickly and checked that we were getting cold air before he packed up and left! We are very relieved and happy!
Working on a Heil heat pump
Fixed drain issues an Goodman a/c unit
Amanna gas pack checked system found duct down for up stiars supply vents and repired and cycled system working at this time
Working on an Amana heat pump
Goodman heatpump inspection
Carrier heatpump inspection
Amanna heat pump completed EPA cooling maintenance and cycled system working at this time
Tempstar air handler checked system found no power to conyral transformer due ti bad contal board need to replace contral board
performed diagnostic on Trane heat pump split unit AC zoned
Working on an Amana Heat pump
Trane A/C checked system found condenser fan motor not running due to bad dual run capacitor and replaced with truck stock capacitor and cycled system working at this time
Trane split Heat pump cooling maintenance