Very personable and professional Would call again
Billy, the service tech, was fantastic ,very knowledgeable, He went above and beyond to explain our problem and to service us........ I highly recommend Billy with Comfort First !!
Parts were ordered and back to fix quicker than anyone else has done. Billy made sure we had a working unit and did his best to make things right
So nice to have a person who knew what they were doing and talked to me with knowledge and respect. Last company did not come close. Thankful for this great visit!!
Great friendly service! Super nice guys!! Very knowledgeable!!
I’ve used CFH&C twice in the year we have owned our home (through our home warranty). Both times, the issues were addressed in a timely manner and the service was very professional.
Super impressed with how helpful and informative Billy was when he came to our house. He explained the situation to us and outlined options in an easy to understand way.
Billy was incredibly helpful and gave extremely good insight and advice in regards to maintaining our AC! I will be a returning customer!
Super nice guys and very knowledgeable!
Goodman A/C checked system found to be working properly at this time
Goodman ac check
Complete 1 System 2 Zones Rheem HP Split System. HO stated ds was not blowing any air but US was fine. Cycled system. Found damper motor for ds not working properly. Getting stuck. Called Adam at the warehouse, he said we have two in stock. Damper motor for ds needs to be replaced. Checked pressures in system. They are great.
Trane ac.replace txv
Trane heat pump replaced start relay and start capacitor and cycled system working at this time
Carrier completed cooling maintenance and cycled system working at this time
Carrier A/C checked system found water in secondary drain pan due to stopped up primmy drain line and cleared and cycled system working at this time
Trane hp...bad hardstart
Trane A/C with case coil checked system found low suction and high head due to bad in door TXV need to replace in door TXV
Trane equipment no ac
Puron gas furnace replaced cfm
Goodman A/C with slab coil checked system found to be low in refrigerate and preferred leak search and found leaking slab coil need to replace coil
Airease heat pump checked system water in secondary drain pan due to stopped up primmy drain line and cleared and cycled system working at this time
Tempstar gas pack checked system found to be low in refrigerate and added 1 lb R-22 to system and cycled system working at this time
Carrier equipment bad zone motor