Very personable and professional Would call again
Billy, the service tech, was fantastic ,very knowledgeable, He went above and beyond to explain our problem and to service us........ I highly recommend Billy with Comfort First !!
Parts were ordered and back to fix quicker than anyone else has done. Billy made sure we had a working unit and did his best to make things right
So nice to have a person who knew what they were doing and talked to me with knowledge and respect. Last company did not come close. Thankful for this great visit!!
Great friendly service! Super nice guys!! Very knowledgeable!!
I’ve used CFH&C twice in the year we have owned our home (through our home warranty). Both times, the issues were addressed in a timely manner and the service was very professional.
Super impressed with how helpful and informative Billy was when he came to our house. He explained the situation to us and outlined options in an easy to understand way.
Billy was incredibly helpful and gave extremely good insight and advice in regards to maintaining our AC! I will be a returning customer!
Super nice guys and very knowledgeable!
Complete 2 Systems worked on US Rheem HP Split System. HO stated system was not cooling. Found bad defrost board. Called Dealers Supply to order board. P#: 47102684204. Price: $47.20. In Stock. Ready for pick up. PO#: 77055. Left epa agreement with HO. He stated he is talking to his wife about it if they decide to sign it they will call us. It’s a 2 System.
Complete 1 System Rheem HP Split System: Tenant stated system was not cooling properly. Checked brazing we performed last time at the evap. Coil. No leaks. Cycled system. Checked pressures. Pressures seemed to be ok. Checked delta t. Found it incorrect. Checked for super heat. Only found 10 degrees of super heat. Checked condenser coil, checked air filter, rechecked evap coil. System was overcharged. Had to remove about 8 oz of 410A to get 26 degrees of super heat and 19 degrees of delta t. System is running great st this time.
ICP a/C checked system found to be low in refrigerate and added 3 lb R-22 to system and cycled system working at this time
Goodman furnace replace control board
Rheem gas pack checked system found compressor not starting due to bad dual run capacitor and replaced with truck stock capacitor and cycled system working at this time
Goodman heat pump checked system found very dirty air filter and removed and cycled system working at this time
Amarican Standard heat pump checked system found bad condenser fan blade need ro replace CFB
Trane gas furnace checked system found blower motor not running due to being bad need to replace blower motor
Goodman A/C checked system found to be low in refrigerate and added 1 lb R-22 also found stopped up primmy drain line and cleared and cycled system working at this time
Rheem checked system found bad condenser fan motor and replaced and cycled system working at this time
Goodman A/C checked system found to be working properly at this time
Goodman ac check
Complete 1 System 2 Zones Rheem HP Split System. HO stated ds was not blowing any air but US was fine. Cycled system. Found damper motor for ds not working properly. Getting stuck. Called Adam at the warehouse, he said we have two in stock. Damper motor for ds needs to be replaced. Checked pressures in system. They are great.
Trane ac.replace txv
Trane heat pump replaced start relay and start capacitor and cycled system working at this time