I would like to express my appreciation to the crew that came out to install my Emergency Generator on one of the Worst Days this year. It was "POURING" rain most of the day but that did not deter the crew. They continued working all thru the rain to get the job done. I was briefed on the operation of the generator after they finished and given manuals to read about the generator. Also, I would like to give a shout out to Joel Worsham who stayed until near 7 p.m. to insure the tech from Duke power came and restored the electricity. THESE GUYS ARE FANTASTIC and reflect the service provide from COMFORT FIRST. They truely live up to the companies name...JOE GUTIERREZ
Very personable and professional Would call again
Billy, the service tech, was fantastic ,very knowledgeable, He went above and beyond to explain our problem and to service us........ I highly recommend Billy with Comfort First !!
Parts were ordered and back to fix quicker than anyone else has done. Billy made sure we had a working unit and did his best to make things right
So nice to have a person who knew what they were doing and talked to me with knowledge and respect. Last company did not come close. Thankful for this great visit!!
Great friendly service! Super nice guys!! Very knowledgeable!!
I’ve used CFH&C twice in the year we have owned our home (through our home warranty). Both times, the issues were addressed in a timely manner and the service was very professional.
Super impressed with how helpful and informative Billy was when he came to our house. He explained the situation to us and outlined options in an easy to understand way.
Billy was incredibly helpful and gave extremely good insight and advice in regards to maintaining our AC! I will be a returning customer!
Super nice guys and very knowledgeable!
I appreciate Billy’s courteous and professional service; he showed true concern and prompt attention to my needs. I will request his services again.
I can’t remember his name but he was very personable and knowledgeable and completed his work in a timely manner.
Billy is awesome. Give that man a raise. He is the kind of technician you want representing your company.
Billy was very informative. Really appreciate his assistance. Will take his professional advice and go from here.
Complete 2 Systems 2 AHS Cooling Maintenances. US Armstrong A/C System. Checked tstat and air filter. Checked blower motor amp draw and run cap. Inspected all wiring at the AH. Inspected evap coil. Drain line found clear. Checked compressor and cfm amp draws. Checked pressures. System found low in 410A. Will need about 1 or 2 lbs of 410A. HO will get a new dispatch transfered to us. Inspected all wiring at the condenser unit. Checked dual cap. Cleaned condenser coil. System is not running great at this time. DS Arm Strong A/C System. Checked tstat and air filter. Checked blower motor amp draw a d run cap. Run cap found weak. 7.5 out of 10 Uf. HO will address this issue to his home warranty. and get a new dispatch transfered to us. Inspected all wiring at the AH. Inspected evap coil. Drain line found clear. Checked compressor and cfm amp draws. Checked pressures. Inspected all wiring at the condenser unit. Checked dual cap. Cleaned condenser coil. System is running grea
Trane furnace replace capacitor
Generator installation. Gas plumbing.
Rheem airhandler heatstrips not working
Complete 2 Systems 2 AHS Heating Maintenances. US Goodman HP Split System: Checked tstst and air filter. Checked heat strips and made sure they were on. Checked blower motor amp draws. Inspected evap coil. Checked all wiring at the AH. Checked compressor and cfm amp draws. Checked dual cap. Checked all wiring at the condenser. Checked pressures. Tested defrost board. Condenser coil is clean. System is running great st this time. DS Goodman Gas Furnace: cycled system. Checked tstat and air filter. Checked Blower Motor amp draw and run cap. Checked electrical connections. No CO detected. Burners are clean. Cleaned Flame sensor. Checked amparage on draft motor. All safety switches are on great condition. System is running great at this time.
Incomplete 2 Systems worked on US Rheem HP Split System: HO stated condenser unit was not coming on. He got maintenance done and they told him defrost board was bad. Found bad defrost board bad. Common side coming from defrost board to contactor not working. Defrost board needs to be replaced. Called Dealers Supply in Raleigh. They said board is not under warranty any more. P#: 47-102684-204. Price: $44.01. In Stock, ready for pick up. PO#: 78070. Part on order.
Replaced heatexchanger gaspack
Complete 1 System Trane Gas Pak, Heating Maintenance: cycled system. Checked tstat and air filter. Checked Blower Motor amp draw and run cap. Checked electrical connections. No CO detected. Burners are clean. Cleaned Flame sensor. Checked amparage on draft motor. All safety switches are on great condition. System is running great at this time. Collected payment for call on HO Rental house and this house.
Goodman furnace airflow ADJUSTMENT
York equipment heating maintenance
Complete 2 Systems worked on US Rheem HP Split System. HO stated system was not cooling. Found bad defrost board. Called Dealers Supply to order board. P#: 47102684204. Price: $47.20. In Stock. Ready for pick up. PO#: 77055. Left epa agreement with HO. He stated he is talking to his wife about it if they decide to sign it they will call us. It’s a 2 System.
Complete 1 System Rheem HP Split System: Tenant stated system was not cooling properly. Checked brazing we performed last time at the evap. Coil. No leaks. Cycled system. Checked pressures. Pressures seemed to be ok. Checked delta t. Found it incorrect. Checked for super heat. Only found 10 degrees of super heat. Checked condenser coil, checked air filter, rechecked evap coil. System was overcharged. Had to remove about 8 oz of 410A to get 26 degrees of super heat and 19 degrees of delta t. System is running great st this time.
ICP a/C checked system found to be low in refrigerate and added 3 lb R-22 to system and cycled system working at this time
Goodman furnace replace control board
Rheem gas pack checked system found compressor not starting due to bad dual run capacitor and replaced with truck stock capacitor and cycled system working at this time