Very knowledgeable and extremely professional . Very impress with service.
Cooling maintenance on a Goodman gas pack
Cooling maintenance on an Amana heat pump
Payne package heat pump completely out of refrigerat preformed leak search and found leaking evaporator coil
Goodman AC blowing dual capacitor
Rheem ac checked system found stopped up primary drain line and cleared and cycled system working at this time
Goodman gas furnace checked system found bad blower motor and replaced
Rheem gas pack no Cooling
Lennox heat pump pack water dripping
Rheem AC ADP coil leaking in attic refrigerant
Trane gas furnace checked system found bad nest thermostat
Trane air handler checked system found float switch in secondary drain pan tripped due to water in secondary drain pan due to stopped up primary drain line and clear and cycled system working at this time
Repla ed accumulator, and evap coil.
Found system low on refrigerant, added 1 lb for optimal cooling.
3 cooling trane maintenances
Found trane heat pump low on r22.