Very personable and professional Would call again
Billy, the service tech, was fantastic ,very knowledgeable, He went above and beyond to explain our problem and to service us........ I highly recommend Billy with Comfort First !!
Parts were ordered and back to fix quicker than anyone else has done. Billy made sure we had a working unit and did his best to make things right
So nice to have a person who knew what they were doing and talked to me with knowledge and respect. Last company did not come close. Thankful for this great visit!!
Great friendly service! Super nice guys!! Very knowledgeable!!
I’ve used CFH&C twice in the year we have owned our home (through our home warranty). Both times, the issues were addressed in a timely manner and the service was very professional.
Super impressed with how helpful and informative Billy was when he came to our house. He explained the situation to us and outlined options in an easy to understand way.
Billy was incredibly helpful and gave extremely good insight and advice in regards to maintaining our AC! I will be a returning customer!
Super nice guys and very knowledgeable!
Amanna A/C checked system found bad dual run capacitor and replaced with truck stock capacitor and cycled system working at this time
Complete: Carrier: Str8 AC Gas Furnace: Air Handler: Checked Thermostat, Filters and Amp Draws on the Blower Motor, Inspected Evap coil. Checked condensate line and Ptrap. AC: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. Washed Coils. System looks good and running Great at this time.
Carrier gas furnace checked system found stopped up secondary heat exchanger need to replace heat exchanger
Goodman Heat pump checked system found Ground compressor need to replace compressor
Nordyne A/C checked system found compressor not running due to bad dual run capacitor and replaced with truck stock capacitor and cycled system working at this time
Goodman split straight a.c. cooling maintenance
Trane split heat pump cooling maintenance
Heil split straight a.c. cooling maintenance
Trane gas package unit Diagnosed bad blower wheel
No issues.....thermostat replacement requested
Trane furnace repair
Trane furnace check
Trane gaspack cooling maintenance
Trane equipment fan running constantly