Complete: 1 System: EPA Maintenance Amana Split Heat Pump: Air Handler: Checked Thermostat, Filters and Amp Draws on the Blower Motor, Inspected Evap coil. P-Trap and checked condensate line. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. Washed Coils System looks good and running Great at this time.