Nate is very knowledgeable and trustworthy. He informed me of various options for my unit, but was not pushy and seemed honest. Would highly recommend!
The guys just left, I assume everything is doing well. They were very professional and did not need much from us at all. Came got the job done and made sure we were informed and asked if we had questions. Not much more that I can ask.
They did my install a day early. Very professional
The installation team was very knowledgeable & courteous.Got to my home@ the time window,no frills knocked the job out & cleaned up behind themselves.
Awesome crew! Great communication and very professional.
Billy E arrived on time and was very friend and customer centric. He is knowledgeable and fixed my system in only a few minutes. Billy was very honest and easy to talk to. He listened to my concerns and recommended upgrades to my system to meet my needs. All in all I could not ask more from an HVAC technician.
Quick and friendly fix to our HVAC evaporator water trap issue!
Awesome! Professional knowledgeable and quick. Good dudes.
On time, courteous, on budget, and excellent service.
Goodman gas pack checked heat open pressuer switch due to bad draft induser motor need to replace draft induser motor
Goodman A/C checked system found week dual run capacitor and replaced with truck stock capacitor and cycled system working at this time
Trane A/C checked system found float switch tripped in secondary drain pan due to water in pan from stopped up primmy drain line and cleared and cycled system working at this time
Goodman equipment no issues
Goodman a/c replaced zone damper motor and cycled system working at this time
Carrier equipment no issues washing machine drain
Goodman heat pump checked system found to be low in refrigerate need to preform die test to locate leak
Heil A/C checked system found contactor shorted and replaced and cycled system working at this time
Payne A/C checked system found CFM over amoing and cuting out need to replace condenser fan motor
ICP A/C checked system found condenser fan blade amd condenser top broken need to replace system to no long available not a good repair for this system
Complete 1 System Trane HP Split System. HO stated system was leaking water at the condenser. Cycled system. Checked pressures. Monitored blower, cfm and compressor. HO was just concerned about the condensation on the suction line and condensation water coming out from drain line. Explained HO that was part of the system and gave him all the details. System is running great at this time.
Complete 2 Systems worked on Both, US And DS Systems. US Goodman Straight A/C: HO stated system was not keeping. Cycled system. Monitored compressor, cfm and blower motor. Checked air filter. Checked pressures. Made sure drain line was clear. No issues. System is running great at this time. DS Rheem Straight A/C: HO stated breaker was tripping like every 24 hrs. Cycled system. Found bad 30 amp breaker. Checked compressor windings and cap. Replaced breaker. Used a 30 amp Breaker Murray brand from truck stock. Checked pressures. Checked compressor and cfm amp draws. System is running great at this time.
System frozen comfortmaker
Goodman ac no issues
Goodman ac insufficient cooling