They sent out a technician named Ryan, he was on time and got us up and running in no time.
Working on a carrier heat pump
Replaced evap coil on a carrier heat pump
Replaced evap coil on a nordyne heat pump
Trane heat pump checked system found bad hard start and dual run capacitor and replaced and cycled system working at this time
Nutone gas pack checked system found bad dual run capacitor and replaced with 45/7.5 dual run capacitor and cycled system working at this time
Install draft motor on mobile home gas furnace
Worked on 3 ton Split Rheem heat pump. Found bad capacitor. Replace with truck stock part. Test operation. System is cooling properly at this time.
Arrived to perform heating maintenance. Checked all operations of the system, checked amp draw on fan motor, heater kit and compressor. Checked all capacities temperatures and refrigerant pressures. System working properly at this time.