Comfort First did an amazing job getting my HVAC system up and running. Awesome service.
Kelli is knowledgeable about all aspects of HVAC systems and presents the information well. I really got an education today! She is friendly and professional. I am very impressed with her and your company. I am unable to rate the cost with stars as there is no comparison. The pricing of the system as presented with everything included seems fair. Highly recommend your company and Kelli!!!
Service is awesome as always. They come when they say they will and they are the nicest people ever.
Carrier 80% furnace heating maintenance
Trane split heat pump. Diagnosed bad variable speed blower motor
Goodman gas package unit Diagnosed 2 bad zone damper motors
Goodman split heat up. Diagnosed loss of high voltage between unit and breaker
Goodman split heat pump. Diagnosed incorrect piston Installed on air handler
Goodman ac and coil I stall
Replaced trane evaporator coil
Replaced evaporator coil
Lennox equipment GFI C tripped 2 condensate pump first floor
Goodman gas furnace heating maintenance
Goodman split a.c. with gas heat. Diagnosed unit low on refrigerant. Found leaking case coil.
Rheem gas Pack. Found bad single pole contactor. Replaced with new and ensured proper operation
Carrier gas package unit. Found a bad dual capacitor and a bad blower capacitor. Replaced capacitors and checked system for proper operation
Goodman gas pack maintenance
Amana furnace uv light kit