Shawn did a great job and was very helpful with information. Up and running very quickly.
Comfort First did an amazing job getting my HVAC system up and running. Awesome service.
Kelli is knowledgeable about all aspects of HVAC systems and presents the information well. I really got an education today! She is friendly and professional. I am very impressed with her and your company. I am unable to rate the cost with stars as there is no comparison. The pricing of the system as presented with everything included seems fair. Highly recommend your company and Kelli!!!
Service is awesome as always. They come when they say they will and they are the nicest people ever.
Goodman split heatpump replaced evaporator coil charged system with 9lbs of r22
Rheem straight a.c. split. Diagnosed leaking case coil
Trane split heat pump. Repaired bad high voltage wire and pulled new thermostat wire to condenser
Rheem split straight a.c. 2 zone. Diagnosed broken manual damper in upstairs ductwork
Trane gas package unit Diagnosed leaking evaporator coil
Goodman straight a.c. split. Diagnosed leaking case coil
Goodman split heat pump. Diagnosed bad compressor
Goodman split heat pump Diagnosed bad compressor and Cfm
York split straight a.c. Replaced leaking case coil and service valve. Recharged system and checked for proper operation
Goodman unit...no ac
Complete 2 System worked on US Carrier HP split system HO said system was not coming on. Found float switch deactivated due to drain pan full of water. Got about 6 gallons of water out of drain pan. Drain line was stopped up. Replaced P trap. and cleared drain line. Checked refrigerant charge. System running great at this time.
Complete 2 System worked on a Goodman HP Split System DS HO said system was leaking water. Found a lot rust trush in Evap coil case drain pan. P trapped was stopped up. Cleand drain pan in coil case. Replaced P trap. Clear drain line. Checked condensate pump to make sure it was working properly. Found system low in charge. Added 2 lbs. Of R22 and also added a can of leak stop. System is running great at this time.
Complete 1 System worked on a Goodman HP split system HO said system is leaking water. Found drain stopped up. Replaced P trap. And cleared line. Found system low in refrigerant. Added 1 lbs of R22. System is running great at this time.