Shawn did a great job and was very helpful with information. Up and running very quickly.
Comfort First did an amazing job getting my HVAC system up and running. Awesome service.
Kelli is knowledgeable about all aspects of HVAC systems and presents the information well. I really got an education today! She is friendly and professional. I am very impressed with her and your company. I am unable to rate the cost with stars as there is no comparison. The pricing of the system as presented with everything included seems fair. Highly recommend your company and Kelli!!!
Service is awesome as always. They come when they say they will and they are the nicest people ever.
Goodman split straight AC diagnosed leaking evaporator case coil
Trane furnace repair
Train gas furnace performed cooling maintenance
Complete 1 System 3 Zones Lennox HP Split System. Came to replaced 12” flex. Removed old flex and installed new one in. I had a hard time time trying to get flex onto collar due to all flexes too closed together. Strapped flex. System is running great at thi time.
Complete 2 System worked on US Rheem HP Split System. HO stated system was not cooling. Found system low in refrigerant. Added 3 lbs of 410A. Checked pressures System is running great at this time.
Complete 2 System worked on US Goodman HP Split System. Came to replace compressor. Recovered refrigerant. Removed old compressor. Flush line with RX11. Removed old filter dryer. Installed new filter dryer. Installed new compressor. Leak tested system. Pulled vacuum. Added 11 lbs of 438A. Checked pressures. System is running great at this time.
Carrier split heatpump replaced cfm
Goodman gas pack performed cooling maintenance
Carrier gas furnace performed cooling maintenance
Complete 2 System worked on US Goodman Straight A/C System and DS Goodman Straight A/C System. came to perform EPA Cooling Maintenance. DS: Checked thermostat and air filters. Checked blower motor amp draw. Checked run cap. Checked all wiring. Inpected evap coil. Made sure drain line was clear. Checked cfm and compressor amp draws. Checked all wiring at condenser. Checked dual run cap. Checked pressures. Cleaned Condenser coil. system is running great at this time. US: Checked thermostat and air filters. Checked blower motor amp draw. Checked all wiring. Checked run cap. Run cap is out of its range. Talked to HO about replacing it. He said he will wait til it goes bad. Inpected evap coil. Made sure drain line was clear. Checked cfm and compressor amp draws. Checked all wiring at condenser. Checked dual run cap. Checked pressures. Cleaned condenser coil. System is running great at this time.
Goodman split heatpump replaced duct work
Trane gaspack no ac
Nordyne gas pack check
Evaporator coil replaced