Kelli is knowledgeable about all aspects of HVAC systems and presents the information well. I really got an education today! She is friendly and professional. I am very impressed with her and your company. I am unable to rate the cost with stars as there is no comparison. The pricing of the system as presented with everything included seems fair. Highly recommend your company and Kelli!!!
Service is awesome as always. They come when they say they will and they are the nicest people ever.
Cooling maintenance on a Lennox heat pump
Repaired a carrier heat pump by replacing the blower capacitor
Repaired Rudd heat pump by recharging the system
Working on a carrier heat pump cleared drain line and recharged system
A.c. cooling maintenance
Found bad reversing valve
Found straight a.c. 1 lb low on 410, caused outdoor unit to freeze up and not produce cold air.
Found stopped up drain line that turned the system off
Found bad capacitor on straight a.c. unit. Blowing hot air
2 unit cooling maimtenance
2 cooling maintenance a on carrier ac, also checked drain line for blockages
Found bad condensor motor on upstairs heat pump
Found straight a.c. 1 lb low on r22
2 unit cooling maintenance