Professional installation and expertise
Absolutely could not have had a better experience with Renee and her amazing staff at Comfort First Heating and Cooling. Let me start off by saying That I know absolutely zero about heating and cooling, yet by the end of myself and my family’s visit with Renee I felt that I knew and understood everything that was going to be happening with replacing our entire upstairs and downstairs units along with the upstairs duct work. Renee was so informative and so sweet and was on her game. All of the workers were so king and polite and kept everything very tidy . I have A newborn baby and even with all of the work being done he slept through the whole thing! They could not have gotten the job done faster. It felt like I had Blinked and they were done. They had completed upstairs downstairs and the duct work in a matter of two days. I highly Recommend Renee and her staff at Comfort First Heating and Cooling!
I throughly enjoyed working with Renee as she talked and informed me of the advantages of going with Comfort First. I appreciated her recommendations as she talked me through the package deals and what would make sense for me and my household. She talked me through the whole process and there was never any rush or pressure to purchase. I appreciated all and everything Renee did to help me. Thank you Renee! and Comfort First
Very knowledgeable and professional.
Tech was VERY professional, cordial & prompt.
Renee was very well knowledged! Thanks for all your help
Awesome from the first phone call I received from the company
Shawn was a true Professional. He asked a few questions about the Heat Pump problem and began trouble shooting the system. Around 20 minutes later he had located the problem and....Bingo, order the parts, gave me the estimated time when the parts would arrive. Very courteous and knowledgeable individual. Thanks Shawn!
Lennox heat pump replaced evaporator coil
Routine maintenance on 2 Rheem heat pumps
Complete: Goodman 2 zone split HP: HO said system would only heat in auxiliary heat. Found condenser dropping out pressure wise. Checked filters and Evap coil. Flipped to cool and refrigerant was at 50 and 195. Added 3lbs of 410, hard start and a can of leak stop. System is working great at this time.
Routine maintenance on a Carrier heat pump
Routine maintenance on Trane package unit
Wiring repair on a Goodman heat pump
Goodman Air Handler, Leak in Evaporator Coil No refrigerant, R22a refrigerant. 188oz
Cleaning a drain line on a Goodman air handler
Amana split heat no cooling
Replacing a breaker for a Rheem air handler
Incomplete: 1System Rheem split Hp: HO said just stopped cooling. At the HP found bad float switch wire from AH. Repaired it and then realized the HP breaker tripped. Unplugged compressor and fan ran. Tested compressor by ohms and it read good until I checked to ground and it is grounded.
Complete one Goodman heat pump/ electric furnace. Found bad dual capacitor and replaced it. Check refrigerant. System is operating properly at this time.
Working on a Rheem heat pump
Replacing a zone damper
Complete two Lennox heat pumps, worked on the right side. Found clogged drain line. Replaced the p-trap and blew out the drain line. System is operating properly at this time.