Our technicians were prompt, friendly, and did the job! There was more wrong with my system then initially realized but they cared for it. I will highly consider getting the care plan with them for future maintence!
The installers were fast and cleaned up after themselves. Sean was very knowledgeable and very professional. Carlos was the hardest worker I have ever seen. The other guy was a hard worker too. They were amazing! Renee was very knowledgeable and professional. She came out last minute and late at night to take care of my family. Another company was trying to tell me that I HAD to replace both of my systems and I couldn't even get a word in. Completely night and day from their scare tactics and Renees honesty. She said why would I replace a unit that is not broken. Very genuine. I love Comfort First and will be referring them to my friends and family. I was actually referred by my neighbor who just had a system installed by them too!
She was excellent. Very detailed. Helped answer all questions while also putting up with a screaming child.
Two system Lennox split heat pump cooling maintenance
Two rheem split heat pumps cooling maintenance
Provided an estimate for a customer to replace the Mini split in their bonus Room.
Working on goodman heat pump
Goodman split hp no cooling
Performed system diagnostic on Goodman heat pump
Provided an estimate for a customer to replace their mobile home split heat pump with a package heat pump and full duct placement. We will be installing an Amana 16 seer next week.
Working on trane heat pumps
Working on heil heatpump
Air conditioning repair and maintenance service.
Maintenance on Lennox Split Heat Pump: Air Handler: Checked Amp Draws on the Blower Motor , checked the capacitor and blower wheel. Inspected and cleaned Evap coil. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. System looks good and running Great at this time.
Working on lennox heat pump
Lennox Split Heat Pump: Air Handler: Checked Amp Draws on the Blower Motor and Heat strips, checked the capacitor and blower wheel. Inspected Evap coil. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. System looks good and running Great at this time.
Colling maintenance on a heil heat pump