Renee was very well knowledged! Thanks for all your help
Awesome from the first phone call I received from the company
Shawn was a true Professional. He asked a few questions about the Heat Pump problem and began trouble shooting the system. Around 20 minutes later he had located the problem and....Bingo, order the parts, gave me the estimated time when the parts would arrive. Very courteous and knowledgeable individual. Thanks Shawn!
Mr. Mc Leod, did a great job on this morning and we are well pleased with his work ,we are more than Happy
Everyone who was involved from the representative to the installer was absolutely fabulous. Comfort First will be spoken highly of to all that needs help with their HVAC. Thanks Comfort First!
Our technicians were prompt, friendly, and did the job! There was more wrong with my system then initially realized but they cared for it. I will highly consider getting the care plan with them for future maintence!
Complete: 2 systems worked on US Unit. Goodman split HP: HO said it wasn’t cooling. We just performed EPA on 3/19/20. At the HP found system low in refrigerant. Used bubbles on shrader core and it was leaking and bent. Per Jimmy need to add new valve cores and new brass Caps as well as topping off refrigerant at no charge being we had just been out here to do the maintenance and it could have been us that damaged it. Added 3lbs of r22. System is running like it should at this time.
Complete: 2 Systems worked on DS Unit: HO said wasn’t cooling. Found system a little low in charge. Spoke with HO and she said go ahead and do what I need to do. Added 2 lbs of r22. And had a SH of 27 degrees. System is working good at this time.
Complete 1 System EPA maintenance on a Carrier Heat Pump Split System checked amp draws on condenser fan, compressor and blower motor. Checked refrigerant charge on unit. Cleaned condenser coil. Checked all wiring at condenser and air handler. Replaced P trap. Also checked filters. System running great at this time
Goodman split heat pump diagnostic
Amana split heat pump no cool
Heil split heat pump not cooling
Goodman split heat pump maintenance
2 unit amana heat pump maintenance
2 carrier heatpump split systems
Goodman heat pump diagnostic
Trans dual fuel maintenance
Goodman heat pump package unit cooling maintenance
ICP Heat pump cooling maintenance
2 system Lennox heat pump cooling maintenance
Changed out goodman system for 16 seer amana system