Mr. Mc Leod, did a great job on this morning and we are well pleased with his work ,we are more than Happy
Everyone who was involved from the representative to the installer was absolutely fabulous. Comfort First will be spoken highly of to all that needs help with their HVAC. Thanks Comfort First!
Our technicians were prompt, friendly, and did the job! There was more wrong with my system then initially realized but they cared for it. I will highly consider getting the care plan with them for future maintence!
The installers were fast and cleaned up after themselves. Sean was very knowledgeable and very professional. Carlos was the hardest worker I have ever seen. The other guy was a hard worker too. They were amazing! Renee was very knowledgeable and professional. She came out last minute and late at night to take care of my family. Another company was trying to tell me that I HAD to replace both of my systems and I couldn't even get a word in. Completely night and day from their scare tactics and Renees honesty. She said why would I replace a unit that is not broken. Very genuine. I love Comfort First and will be referring them to my friends and family. I was actually referred by my neighbor who just had a system installed by them too!
She was excellent. Very detailed. Helped answer all questions while also putting up with a screaming child.
Working on rheem gaspack
Working on amana heat pump
Working on goodman heat pump.
Complete: 2 Systems: EPA Maintenance Lennox Split Heat Pumps: Both US and DS Perfect: Air Handler: Checked Amp Draws on the Blower Motor and Heat strips, checked the capacitor and blower wheel. Inspected Evap coil. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. System looks good and running Great at this time.
Working on trane gas pack
Working on a york gaspack
Working on rheem gaspack
Complete: 1 System: EPA Maintenance Amana Mortex Split Heat Pump: Air Handler: Checked Amp Draws on the Blower Motor and Heat strips, checked the capacitor and blower wheel. Inspected Evap coil. Evap needs cleaning in the spring. Needs to replace air filters now. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. System looks good and running Great at this time
Found bad control board on aman heat pump
Replaced evap coil on split heat pump
Found bad inducer motor on Payne gas pack
Working on rheem gaspack.
Working on carrier gas pack.
Payne heatpump found system low in Freon
Neil split heat pump noheat