Professional installation and expertise
Absolutely could not have had a better experience with Renee and her amazing staff at Comfort First Heating and Cooling. Let me start off by saying That I know absolutely zero about heating and cooling, yet by the end of myself and my family’s visit with Renee I felt that I knew and understood everything that was going to be happening with replacing our entire upstairs and downstairs units along with the upstairs duct work. Renee was so informative and so sweet and was on her game. All of the workers were so king and polite and kept everything very tidy . I have A newborn baby and even with all of the work being done he slept through the whole thing! They could not have gotten the job done faster. It felt like I had Blinked and they were done. They had completed upstairs downstairs and the duct work in a matter of two days. I highly Recommend Renee and her staff at Comfort First Heating and Cooling!
I throughly enjoyed working with Renee as she talked and informed me of the advantages of going with Comfort First. I appreciated her recommendations as she talked me through the package deals and what would make sense for me and my household. She talked me through the whole process and there was never any rush or pressure to purchase. I appreciated all and everything Renee did to help me. Thank you Renee! and Comfort First
Very knowledgeable and professional.
Tech was VERY professional, cordial & prompt.
Renee was very well knowledged! Thanks for all your help
Awesome from the first phone call I received from the company
Shawn was a true Professional. He asked a few questions about the Heat Pump problem and began trouble shooting the system. Around 20 minutes later he had located the problem and....Bingo, order the parts, gave me the estimated time when the parts would arrive. Very courteous and knowledgeable individual. Thanks Shawn!
Amana split heat no cooling
Replacing a breaker for a Rheem air handler
Incomplete: 1System Rheem split Hp: HO said just stopped cooling. At the HP found bad float switch wire from AH. Repaired it and then realized the HP breaker tripped. Unplugged compressor and fan ran. Tested compressor by ohms and it read good until I checked to ground and it is grounded.
Complete one Goodman heat pump/ electric furnace. Found bad dual capacitor and replaced it. Check refrigerant. System is operating properly at this time.
Working on a Rheem heat pump
Replacing a zone damper
Complete two Lennox heat pumps, worked on the right side. Found clogged drain line. Replaced the p-trap and blew out the drain line. System is operating properly at this time.
Working on a Lennox heat pump
Working on a Lennox heat pump
Complete one system, whole house, rheem split heat pump. Found system low in r22 and added 2 lbs of r22.
Routine cleaning on 2 Goodman heat pumps
Carrier split heat pump
Complete main floor system. Found loose wire causing the fan to stay off and repaired. Found low in R22 and added 1lbs of R22. System operating properly at this time.