They were both very professional and did neat work
Installed promptly and professionally.
Peyton was a pleasure to have in my house during the majority of the installation. He was very professional and I would highly recommend him.
I just spent two afternoons being educated on how to make my house a home. For three years I have been wrapped in blankets and overpaying my utility bill. I decided to investigate switching from heat pumps to gas. Bill Smart took so much time to help me understand what was not working well and what my options were. I decided to move forward and have scheduled the installation in just over a week. I can’t wait to enjoy my new home. Bill was extremely knowledgeable and professional, I would recommend him and Comfort First to everyone.
Cody did a great job of explaining everything in detail as to what was wrong with my HVAC system and even answered several texts to help me identify issues after hours. Overall, I rate his customer service 5 stars!
Very friendly, good at explaining technical terms, cared about saving us money and not doing any services that weren't necessary.
Tony was prompt, courteous, and respectful. He quickly diagnosed the problem and replaced a blown transformer. Hi was both professional and friendly.
Rheem equipment.ductwork down
Trane gaspack leaking coil
Coleman replace outdoor unit disconnect
Coleman outdoor unit contactor failed
Amanna and Trane heat pumps Complete EPA cooling maintenance and cycled systems at this time
Goodman A/C checked system found shorted contactor and replaced and cycled system working at this time
Incomplete: 2 systems worked on DS Unit. $59 maintenance: Goodman split HP: Complete: 1 System: EPA Maintenance Goodman Split Heat Pump: Air Handler: Checked Thermostat and Capacitor, Filters and Amp Draws on the Blower Motor, Inspected Evap coil. Replaced P-Trap, checked condensate line. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. Washed Coils Also spoke with HO about Air purifier. Heat Pumps capacitor is running out of spec and needs to be changed. I have no signal where I am so need to get dispatch to run back by here and replace 45/5 dual cap. Will call tech support for dispatch Collected $62.90 For Maintenance CK #7853
Complete: 1System: Trane split HP: Replaced leaking start assist and relay. Also found 40mfd cap running at 35mfd so I replaced it as well. Checked charge and system is running as it should at this time.
Carrier equipment replace variable speed motor
Trane ac....low charge
Carrier airhandler blower motor bad