Peyton was a pleasure to have in my house during the majority of the installation. He was very professional and I would highly recommend him.
I just spent two afternoons being educated on how to make my house a home. For three years I have been wrapped in blankets and overpaying my utility bill. I decided to investigate switching from heat pumps to gas. Bill Smart took so much time to help me understand what was not working well and what my options were. I decided to move forward and have scheduled the installation in just over a week. I can’t wait to enjoy my new home. Bill was extremely knowledgeable and professional, I would recommend him and Comfort First to everyone.
Cody did a great job of explaining everything in detail as to what was wrong with my HVAC system and even answered several texts to help me identify issues after hours. Overall, I rate his customer service 5 stars!
Very friendly, good at explaining technical terms, cared about saving us money and not doing any services that weren't necessary.
Tony was prompt, courteous, and respectful. He quickly diagnosed the problem and replaced a blown transformer. Hi was both professional and friendly.
Sean and Carlos were very professional and respectful of the property. Unit was installed and operational by midday.
Thanks to Margaret, Jimmy, and the whole service team for one of the best customer service experiences that I've ever had!
Trane package heat pump completed EPA cooling maintenance and cycled system working at this time
Lennox checked system found no power to A/C due to tripped breaker in main pannel box and reset and tighten all electrical connections and checked amps and cycled system working at this time
Amanna heat pump checked system found to be lock on on high head pressure and reset and cycled system working at this time
Complete: 1 System: EPA Maintenance Goodman AC/ Gas Furnace Air Handler: Checked Thermostat, Capacitor, Changed Filters and Amp Draws on the Blower Motor, Inspected Evap coil. Replaced P-Trap, checked condensate line. The water box inside furnace was leaking. Repaired leak. Condenser. Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. Washed Coils System looks good and running Great at this time.
Amana ac...cooling tune up
Trane equipment...cooling tune up
Carrier gas pack...no cooling
EPA maintenance on a Goodman air conditioning system
Complete: 1System: Amana Gas furnace: HO was having issues with Nest Tstat. Tstat would not rotate as it should and was causing issues with heating. Replaced Tstat and will turn in old one for warranty.
Amana split heat pump cooling maintenance
Trane gas package unit cooling maintenance
Ruud straight a.c. cooling maintenance
Trane package heat pump cooling maintenance