Cody did a great job of explaining everything in detail as to what was wrong with my HVAC system and even answered several texts to help me identify issues after hours. Overall, I rate his customer service 5 stars!
Very friendly, good at explaining technical terms, cared about saving us money and not doing any services that weren't necessary.
Tony was prompt, courteous, and respectful. He quickly diagnosed the problem and replaced a blown transformer. Hi was both professional and friendly.
Sean and Carlos were very professional and respectful of the property. Unit was installed and operational by midday.
Thanks to Margaret, Jimmy, and the whole service team for one of the best customer service experiences that I've ever had!
Armstrong air handler second-floor evap coil leak
Replace compressor...Goodman gas pack
Goodman package heat pump checked system found condenser fan motor not running due to bad dual run capacitor and replaced and cycled system working at this time
Trane heat pump checked system found bad dual run capacitor and to be low in refrigerant and added 2 lb R-22 to system and cycled system working at this time
Trane package unit blown 40/5 dual capacitor
Rheem HP set Subcooliing and super heat
Lennox A/C bad capacitor
Bryant A/C low in refrigerant R22
Goodman gas apck checked system found high suction pressure and low head pressure due to compressor not pumping to full capacity due to being bad need to replace compressor
Found water in secondary drain pan due to stopped primary drain line and cleared and cycled system working at this time
Carrier ac checked system found grounded compressor need to replace compressor
Goodman package heat pump replaced blower motor and cycled system working at this time
Weatherking gas pack replaced evap coil and recharged system with 7 lb R-22 and cycled system working at this time
Goodman ac add refrigerant
Goodman ac replace compressor