Great Service Friendly Technicians
Nice, courteous staff
We would definitely recommend Dennis to others; a top-notch HVAC technician! Thanks!
Jon was very knowledgeable and courteous during the service call.
Very good service
Performed diagnostic on Lennox heat pump AC
Completed measurements for a home warranty customer for them to have their system replaced.
Completed measurements for a home warranty customer who is having their system replaced.
Performed diagnostic on Goodman heat pump.
Replaced capacitor on Goodman heat pump
Replaced blower control board on Goodman heat pump
Replaced blower motor and compressor on Goodman heat pump
Performed diagnostic on Payne heat pump
Added r22 refrigerant to Goodman heat pump
Measured for a home warranty customer to have their system replaced.
Performed preventive maintenance on Goodman heat pump
Repaired refridgerant leak in Goodman heat pump
Gave estimate to replace a full duct system. We will be replacing the duct system next week.
Provided an estimate for a customer to replace both of their split heat pumps. We will be replacing both of them with 15 seer Amana systems next week.
Complete: 1 System: ICP split heat pump: homeowner said it was not blowing. Found Thermostat working intermittently. Replaced the Tstat. Found fuse blown in the AH. Found a short in the low voltage wire running to outside unit which fried the transformer inside AH. Replaced transformer and placed inline fuse. Repaired short in the outdoor unit. Cycled system and the unit is working great at this time.