I’d recommend them if they did a good job.
All other technicians would put covering on their feet before entering my home. This technician did not. He asked about the thermostat and lowered my temperature. Did not return it back to original temperature I had it set on. The technician also left the light on under our house and we didn't notice it until Sunday, so the light was on for several (5) days.
I was referred to your company by a coworker and so far I pleasantly pleased with the courteous and honest service my wife and I have received. Beth and Renee have been a pleasure to work with.
Great Service Friendly Technicians
Nice, courteous staff
We would definitely recommend Dennis to others; a top-notch HVAC technician! Thanks!
Jon was very knowledgeable and courteous during the service call.
Worked on Goodman heat pump replace common wire Cycle System running properly
Incomplete: two systems: worked on upstairs system: Goodman, split heat pump. Found breaker tripped on outside unit. HO said he tried to flip it back on and immediately flipped off. At the heat pump checked capacitor and it was low, checked to see if there was refrigerant in the system and there was. At the compressor terminals compressor ohmed out on all 3 terminals. Compressor grounded. Informed HO of findings. He said he wanted to order part of it was available. Called Baker. Part on Order.
Worked on Goodman heat pump need to return with new condensing fan motor blade
Complete main level Goodman split heat pump replaced defective condensate pump remove water from secondary pan Cycle System running properly
Worked on Carrier heat pump replace compressor replaced filter drier replaced 45 + 5 microfarad capacitor added 8 lb refrigerant Cycle System running properly
replaced x13 blower motor on Payne heat pump AC split system
clean drain line and replaced pan switch on carrier heat pump AC split system zoned
performed diagnostic on trane heat pump AC split system zoned
added r410a refrigerant to heil heat pump AC split system.
performed leak search on Goodman heat pump AC split system.
adjusted air flow on 2 zone heat pump AC split system zoned
Found blown compressor order new compressor returning when it comes in
Worked on two systems replaced thermostat downstairs and capacitor made low voltage wire repair for upstairs both systems running properly
Clear drain line replace P-trap system running properly
performed diagnostic on Goodman heat pump AC split system