Bradley did an amazing job. This is the second time I’ve had my HVAC inspected and this time by your business. He was able to quickly identify a leak in the coil and provide information. He was very upfront with timelines and cost for the repair to ease any concerns.
I’d recommend them if they did a good job.
All other technicians would put covering on their feet before entering my home. This technician did not. He asked about the thermostat and lowered my temperature. Did not return it back to original temperature I had it set on. The technician also left the light on under our house and we didn't notice it until Sunday, so the light was on for several (5) days.
I was referred to your company by a coworker and so far I pleasantly pleased with the courteous and honest service my wife and I have received. Beth and Renee have been a pleasure to work with.
Great Service Friendly Technicians
Nice, courteous staff
We would definitely recommend Dennis to others; a top-notch HVAC technician! Thanks!
replaced capacitor and defrost sensor on carrier heat pump AC split system
replaced blower control board on Goodman heat pump AC split system
performed diagnostic on carrier heat pump AC split system zoned
found compressor faulty on Goodman heat pump AC split system
performed diagnostic on carrier heat pump AC split system
performed leak search on heil heat pump AC split system
performed heating maintenance on Amana heat pump AC split system.
replaced capacitor on carrier heat pump AC split system
Complete: 1 System. Amana Split HP: Helped complete change out. Wired system, set up nest Tstats and started system. All looks good and working great at this time.
Help complete Change out of new Amana heat pump.
performed diagnostic on Goodman heat pump AC split system air handler
InComplete: 2 systems worked on US system. HO said was blowing out Heat in cool mode. First of all they had the units labeled wrong outside. Both were running and I went by the label instead of double checking the system to see which was US and DS so I spend 30 min working from US AH to DS HP frustrating. When I got it rt the wiring to DS was not getting enough common 24v through contactor to energize reversing valve. Changed contactor. Secondly found Nest Tstat bad. Informed HO that AHS would not cover replacement of a nest and I could put a Tstat on the wall for 137.00 ...... he said he would go get a new nest and put it up himself. It sure if he believed it was a Tstat issue so u told him it would be a recall if he put it up and still didn’t work but if it was still a nest issue that he would be denied and have to pay. System not working correctly at this time.
Estimate for replacing heat pump system
Goodman repaired main drain
Goodman heat pump checked system found water in secondary drain pan due to stopped up primary drain line and cleared and cycled system working at this time