David reset the hard lockout and explained what to do if it should happen again. We appreciated his expertise.
Great job, very good experience
Renee is a great professional sales representative
Very professional and knowledgeable. I’m very pleased with service that I received from Mr. Saucedo and his counterpart. I will recommend to others.
Install crew was fast and informative, Thanks Comfort First
I have enjoyed the costumer service I have received from with Bill Smith and Skyler Hunter. They both were very professional.
Will refer Comfort First to others!
They went to work as soon as they arrived, it was apparent that they knew exactly what they were doing. Couldn’t ask for a more competent crew, not only did they work as quickly as possible they cleaned up and explained everything before leaving. Omar and Carlos are definitely a great team.
Bradley did an amazing job. This is the second time I’ve had my HVAC inspected and this time by your business. He was able to quickly identify a leak in the coil and provide information. He was very upfront with timelines and cost for the repair to ease any concerns.
Tune up on a Goodman heat pump
performed leak search on Goodman heat pump split unit AC
replaced capacitor and added r22 refrigerant to Goodman heat pump split unit AC
added r22 refrigerant to Goodman heat pump split unit AC
performed diagnostic on Amana heat pump split unit AC
replaced zone damper and motor
cleared drain line on Goodman heat pump split unit AC
performed cooling maintenance on Goodman and Amana heat pump split unit AC
Complete two systems lower, Carrier heat pump split. Found emergency pan full of water and drain line clogged. Replaced p-trap and cleared out drain line. System is operating properly at this time.
Complete two systems, lower Lennox heat pump pack. Found two pole contactor not passing power and replaced it. Preformed balance of system check. System is operating properly at this time.
performed diagnostic on carrier heat pump AC split unit
repaired wiring on Goodman heat pump split unit
cleared drain line on heil heat pump AC split unit
performed diagnostic on Trane heat pump split unit
replaced contactor on Lennox heat pump pack