Cody and Elmer were very professional and I would highly recommend them. Extremely happy with their service.
He was very professional and very knowledgeable about everything he was doing to the air conditioner
Installing a new Goodman unit
Routine maintenance on a Goodman heat pump
Complete: 1Systems: EPA Maintenance Goodman Split Heat Pump: Air Handler: Checked Amp Draws on the Blower Motor and Heat strips, and checked blower wheel. Inspected Evap coil. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. And washed system. Added one UV light and reconnected disconnected wires. Left spare Light.Also found condensate pump no longer working. Need to bring new condensate pump on next visit out. System looks good and running Great at this time.
Replaced a contactor on an American Standard heat pump
Routine maintenance on an Amana heat pump
Complete: Goodman Split HP: Found compressor not running. Checked Capacitor and it was bad. Changed Cap and compressor came on. Checked Amp draws and they were good. Checked charge and Delta T. System looks good and running great at this!
replaced condensate pump on Goodman heat pump AC air handler
Goodman split hp no cooling
Amana Heat Pump, Replaced Heat strips
Heating maintenance on a Goodman heat pump
Performed diagnostic on Lennox heat pump
Working on carrier heat pump
Working on Rudd unit