Complete: 2 System: Goodman Split Heat Pump: Air Handler: Checked Thermostat and Capacitor, Filters and Amp Draws on the Blower Motor, Inspected Evap coil. Replaced P-Trap, checked condensate line. Heat Pump: Checked the charge, and the capacitor. Check the Amp draws on the fan and compressor. Cleaned Unit. Washed Coils System looks good and running Great at this time.