Billy was very knowledgeable and honest about the issue we were having in our crawl space. He gave great advice and obviously cares about his work. Thank you!
Billy E was very professional and answered all of my questions. He was also in protective gear do to the COVID. Outstanding individual who represented not only Comfort First but himself as well. Great job Billy E I really appreciate your customer service.
Billy was very professional and took the time to explain everything to us. I put average for cost/pricing bc they need to come out to give me an estimate.
Billy is awesome. I loved his professionalism and he is the consummate professional. I am switching dromAHS to comfort because of billy! I only want him at my house...so comfort of you read this, I’m switching to you and please o my send billy to me house! Sincerely, Sam Davis Retired Marine and loving comfort!
The HVAC Tech was very courteous and kind. Took time to explain all the different options and scenarios with our unit. He was prompt and on time. I appreciated that he had a discussion with us about our different options going forward and things to consider as our unit is a little older. He was very supportive and not pushy but just communicating good information. Overall great experience
Ronnie is a great tech. His knowledge and expertise is assuring.
Complete 2 Systems 2 Heating Maintenances: DS Trane Duel Fuel System: Checked tstat and air filter. Checked Blower Motor amp Checked electrical connections. No CO detected. Burners are clean. Flame Sensor is clean. Checked amparage on draft motor. All safety switches are on great condition. System is running great at this time. Checked HP Side: Checked compressor and cfm amp draws. Checked dual cap. Checked all wiring at the condenser. Checked pressures. Cleaned condenser coil. System is running great st this time. US Trane HP split System: Checked heat strips and made sure they were on. Checked blower motor amp draws. Inspected evap coil. Checked all wiring at the AH. Checked run cap. Found it weat. HO said he will call AHS. Checked compressor and cfm amp draws. Compressor is overamping. HO said he will call AHS and ddress this issues to them. Checked dual cap. Checked all wiring at the condenser. Checked pressures. Tested defrost board. Cleaned condenser coil. System is running gr
Complete 3 Systems 2nd Floor York Straight A/C: came to test previously installed compresor. Compressor is running great. Checked pressures. System is running great at this time.
Trane heat pump completed EPA heating maintenance and cycled system working at this time
Goodman equipment cooling maintenance
Goodman hp....an ac low charge basement unit 1bl
Worked on Carrier humidifier
Work on gas furnace
Worked on Goodman gas pack
Goodman gaspack no heat
Goodman gas pack checked system found high gas pressuer at inlet side of gas valve need to get gas company to check gas pressure at meter
Worked on Goodman gas pack.
Worked on Goodman gas furnace.