Dry professional and knowledgeable. Excellent job
Shamari was fantastic today in servicing my air conditioning unit. He was intelligent in troubleshooting several options and because of this he got it working quickly and kept me informed the entire time on what was happening. I am very pleased and couldn’t of asked for better service on such a hot day!
Fast, efficient, and friendly!
Shamari was very knowledgeable about what he was doing. He was informative and very helpful. I appreciate his urgency in the matter and he was able to replace my motor quickly. I would highly recommend this company and I would highly recommend Shamari for his wonderful service.
Needed a fliue pipe licked and supported
Justin was extremely professional and knowledgeable. He was timely, friendly, and had a great attitude. He was able to diagnose my issue and fix it within minutes.
Shamari was great and fixed our problem very quickly!
Prompt repair, great technician!
Brad did a fine job, very professional , on time. Solved problem and had unit up and running in no time. Thanks Brad.
System not cooling properly. Cleaned condenser coils
Ac not cooling properly
Fixed control board an blower motor
Complete. 1 system. Did not install TXV. system does not have a TXV inside indoor unit (Pic in docs) I re-diagnosed the system. System not cooling due to restricted piston and, having 2 filter driers on the liquid line further restricting refrigerant flow. I removed indoor filter drier, blew lines clear and, cleaned piston. System operating properly at this time with a 20 degrees temperature drop inside from return to supply register.
Replaced failed light switch.
Replaced failed condenser fan motor
Repaired gas leak.
Not cooling. AC not coming on. 1 system. System not cooling due to a low voltage shortage. I tracked shortage, rewired outdoor unit and, replaced blown 5amp fuse. System operating properly at this time.
Air conditioner not cooling, not working. 1 system. System not cooling. Found compressor not running due to singed compressor wires. Rewired compressor to the contactor and, replaced capacitor. System operating properly at this time.
Added freon to Carrier system
Not cooling. Not working. Complete. 1 system. System not cooling due to broken cfm. Replaced cfm. System operating properly at this time.
Fixed flue pipe on furnace
Fixed a,c lines