Very professional took care of problem and I Would highly recommended him for another job if needed Wore mask and shoe Covers A plus Thanks
Good customer service
Justin was so helpful and had great customer service. He took his time explaining the issue and what he saw as well as possible fixes for the future. Was so detailed in his explanation and he actually took the time to ensure I understood. Thank you Justin!
Shamari Baker was the best service provider of any type we've had in a long, long while. He not only fixed our AC issue, but he took the time to explain the issue, the solution, and future considerations in patient detail. Hope y'all appreciate him, Comfort First. Excellence personified!
Justin the service technician that was assigned to my work order did an amazing job, he kept me up-to-date with the progress in repairing my Ac unit and let me know when the job was completed. This is what you call outstanding customer service.
the guys that came to 5205 eagle Creek drive they did an outstanding job I will give them to 10 stars to anybody that come to here they did number 10 job plus 10 thank you
Everything was handle correct
Ac not working second opinion
Epa heating maintenance
Ac unit not cooling
Ac with issue of water in pan.
Fixed a/c unit
Ac not cooling due to contactor malfunctioning. Replaced contactor, capacitor and added hard start to system. Unit is cooling properly at this time.
Replaced collapsed ductwork and restrapped ductwork that had fallen
Repaired service port, line drier, contactor, 5 amp fuse. Charged system with 7 pounds of r22 and system is cooling properly
Complete. 2 systems. Worked on downstairs system. System draining from secondary drain due to clogged primary drain line. I cleared drain line for both systems and vacuumed water from downstairs secondary drain pan. System draining and, operating properly at this time.
Ac drain leaking water. Cleared drain line and recommended Epa maintenance agreement
Ac not cooling due to broken condenser fan blade. Changed blade and checked pressures. Unit is cooling properly at this time
Ac not cooling. Changed out compressor, line drier and capacitor. Charge system with 6 pounds of r410a. Unit is cooling properly at this time.
Ac not working. Replaced condenser fan motor, liquid line sensor and ambient sensor. Unit is cooling properly at this time.