James did a great job. Was very thorough and checked every aspect of the system to make sure we wouldn’t have any additional problems. System is running great now.
Very courteous and smart
13/10 would recommend
Tech did a nice job troubleshooting and replacing parts.
He was thorough and knowledgeable!
We had a very knowledgeable, helpful technician!
Very nice and professional service man. Explain the problem and fixed it.
Top notch and very thorough Technician
Changing out new 90% furnace with ac and coil in attic. Current system is 3 ton and undersized. After proper load calculation was performed a 4 ton will be installed with zone system
Complete two systems, worked on downstairs unit. Found system was freezing due to being low in refrigerant and added 1 lbs of r410a. System is operating properly at this time.
Complete two systems, downstairs. Found bad capacitor and replaced. System is operating properly at this time.
Cleaned condenser coil on trane outdoor unit
Change swollen capacitor on trane compressor
Worked on Trane heat pump
Worked on Goodman air conditioner
Bad nest changed out with programable tstat
Replacing pressure switch on York gas furnace.
Trane Heat pump with intermittent problem.