Mr. Preston helped me out tremendously with my concerns about my HVAC system.
We had a great experience with our a/c service request. We were notified of the service call window and 30 minutes prior to the tech heading our way. The tech was knowledgeable and informative.
He did a great job. Very professional.
Really nice. Explained why he made the changes. And again, fast and efficient!
Billy was extremely thorough and explained everything thing to me in great detail and so I can understand it. He went above and beyond and even explained to me the best filters to use in the home.
Replaced condensation pump an checked air conditioning
Installing new ac and coil and fixing some other return issues to help the new system last longer. Amana 2.5 ton ac with 10 year labor warranty, 10 year compressor warranty, and 10 year parts warranty
Ac and coil replacement
Complete one system, attic. Preformed heating maintenance checked operations, cleaned flame sensor. System is heating properly at this time.
Complete one system. Found duct not all the way open and opened manual damper. Air flow is good. Checked system pressures and they were good. System is operating properly at this time.
Complete two systems, worked on upstairs and downstairs. Upstairs system no coming on due to water in drain pan and clogged condensation drain line. Removed water from the drain pan and cleared out the drain lines. Systems are operating properly at this time.
Complete one system, outdoor unit. System not working due to bad capacitor and replaced it. System is operating properly at this time.
Completed two systems, worked on upstairs and downstairs. Upstairs, found unit low of refrigerant and added 1 lbs of r22. Downstairs, found bad capacitor and replaced it. Systems are operating properly at this time.
Complete one system, main. Found bad contactor and replaced it. System is operating properly at this time.
Complete two systems, worked on both downstairs and upstairs. Downstairs system, found clogged drain line and cleared out. Upstairs system, found low in r410a and added 2 lbs of r410a. Systems are operating properly at this time.