Another service company stated that one of my Heating/AC units needed to be totally replaced, when Anthony examined it, it was the Circuit Board, which he had on his truck! The Unit is back up and working perfectly, keeping my Tenant well heated! Anthony explained everything in detail from diagnosing the problem to the repair and he was courteous and honest. He made sure that every screw was in its place, that all were accounted for, and the work place was very neat and clean. I Highly recommend “ComfortMaster Heating & Cooling Services”!!
Great experience over all
We had a bit of an emergency, the young lady on the phone was very helpful and the technician was at our house very quickly. After a quick diagnosis, the repair was done quickly. Very happy with the experience.
Pleasant techs. Very polite.
As always Bob is efficient and professional. All questions were answered and suggestions made for future service.
Response from ComfortMaster Heating & Cooling Services:
Thank you for giving Mike a 5 Star Rating, and the kind words!
Tune up on Crown Aruba gas boiler, Amana A/C system and Rheem water heater. Checked safeties and electrical. All functioning at this time.
Carrier Heatpump not working. Found tripped low voltage circuit breaker. Removed several wires from control board and tested for short circuits or grounds. Found short in the reversing valve coil circuit. Also found defective defrost control board and replaced. Tested operation. Recommend unit have annual maintenance, cleaning, and testing in the spring.
Peerless Oil Boiler Tune Up. Running good, all components operational except bad zone valve end switch. Tested for Nest Thermostat compatibility but 2 zones only have 2 wires (Den & Master Bed), so need to run new wire to allow a WiFi thermostat to function.
Upstairs zone over heating, found failed Honeywell zone valve on Burnham oil fired boiler. Drained boiler and replaced valve, purged air out of the lines and started boiler. All working at this time.
Tune up on Armstrong condensing gas furnace with matching air conditioning coil and condenser.
No heat to second floor radiators. Found Honeywell zone valve motor head stuck. Replaced, rewired and tested operation, all functioning at this time.
Replaced leaking boiler piping.
Tune up on gas fired Peerless boiler mini
Cleaned out clogged drain on A/C unit.
Furnace annual service.
Gas furnace with AC tune up.
No hot water
Luxaire air conditioning system tune up for optimal efficiency and reliability throughout the cooling season. Replacing air filter checking refrigerant level inspecting duct work and electrical flushing drain line and cleaning indoor and out door coils.
Carrier gas fired furnace with Air conditioning coil and condenser tune up for optimal efficiency and reliability throughout the season
AC system check and seasonal inspection