Anthony throughly assessed our system and addressed our problems with our 15 year old air-conditioning system. He gave us an estimate for fixing it. We asked about the possibility of us buying a new system and the cost of a new system. We felt confident with his service and knowledge.
Anthony was very thorough in his review of the cooking system in my new home . He scheduled the repairs/ maintenance appointment quickly and completed the work in a timely manner . The end result of our newly maintained system is phenomenal.
Exceptional service! Called as a new client Monday morning because our AC units stopped working and Anthony came within an hour! I was shocked for such quick service. Anthony was extremely knowledgeable, professional, and friendly. He fixed both our units during the visit. I would definitely recommend them and will be using them in the future for any services/needs!!
Anthony was very clean, respectful and knowledgeable. Very happy with the service he provided!
Anthony came out to fix our AC as soon as possible. Sue was amazing too!! Great service! Thank you!
Quick Response. Friendly Service Methodical Approach to identify cause of a problem with complex System 2000 heating hot water system, Cost-effective: Replaced parts, avoiding replacement of equipment. Followed up to confirm success of the repair.
Very knowledgeable and courteous.
Anthony is always friendly and courteous when he is servicing our heating/cooling equipment. They always respond quickly whenever we have a problem. He is very trustworthy. It’s a pleasure to deal with him.
🌟🌟🌟🌟🌟very good service
System 2000 gas boiler annual heating check.
Trane AC system not cooling. Found outdoor coil extremely dirty, and restricted r22 metering valve.
Lennox gas furnace with r22 ac condenser. Annual maintenance tune up
Amana gas furnace with ac maintenance tuneup. Replaced UV Bulb in Air Purifier
Goodman unit fan not turning and running hot. Found and replaced defective dual capacitor. Also checked freon level.
Bock water heater no hot water. Needs to keep resetting burner. Found nozzle and electrodes need to be replaced.
Lennox Air Conditioning not blowing cold air. Found defective capacitor for Compressor and teplaced.
Carrier AC system leaking. Found systems in need of deep cleanings, and performed maintenance services, and several repairs.
Water leak through ceiling. Found leak from condensate pipe fitting and repaired. Also found zone damper actuator sticking closed and could've cause excessive condensation.
Tempstar AC systems not cooling. Found both outdoor units not running, but indoor units working. Tested and found bad capacitors. Replaced and tested operation and freon levels. Systems are old and in need of deep cleanings.
Amana Heat Pump System Check/Annual Maintenance
Heil AC icing up. Found system very dirty and low on freon. Cleaned unit and added refrigerant.
Tempstar Gas Furnace and central air system, with bedroom zone not cooling. Manually opened defective zone damper to allow cooling until new control is installed.
Lennox Heatpump not cooling. Found low pressure alert code on circuit board but system pressures were not low. Had to remove refrigerant to get proper freon level.
No AC Amana central air conditioner. Not blowing cold air. Found bad capacitor, and replaced. Also performed ac annual maintenance.