The Comfort Master team was very efficient, respectful and professional. Sue and Anthony were very professional and efficient in answering my questions and setting up my appointments. Bob, Mitch & Shawn did a great job explaining the process and replacing our whole HVAC system including the ductwork. They also added zoning to the new unit which works out great for us. They were very professional, knowledgeable, and courteous. They took the time to answer our questions and explain the operation of the systems. Not to mention they left the area in impecible condition when they were through. I highly recommend Comfort Master services to anyone who needs HVAC system replacement.
From meeting Robert, the sales rep, through the installation of my furnace and water heater, I felt Comfort Master was the right provider for me. I found they offered expert and professional service that I can rely on for years to come.
Bob was very professional and did an excellent job explaining everything. I’m very satisfied with the completed job.
Bob from ComfortMaster was friendly, and he provided a truthful evaluation of my aging air conditioning unit. I trust that his advice was in the best interest of the customer.
Installed antifreeze in System 2000 oil boiler to protect against frozen pipes in crawl space. Also performed tuneup and tested operation. Found wide pressure swings during burner operation due to defective expansion tank. Replace tank, and installed webstone isolation valve to allow for future testing without draining heating system.
No heat Utica Gas Boiler. Found pilot not lighting, due to it being wet from water leak at expansion tank. Replaced expansion bladder tank, as well as air vent, and relief valve. Dried pilot assembly and relit pilot, after refilling and purging boiler. Tested for draft and carbon monoxide in flue to chimney.
Utica Gas Steam Boiler repairs. Added water boiler treatment, installed new steam gauge, pressure control, pressure relief valve, and steam vents in mains and radiators. Also replaced drain valve at bottom of boiler.
Weil McLain Oil Boiler tuneup. Found defective clean cut oil pump and replaced. Adjusted burner for maximum efficiency.
System check on Amana gas furnace and A/C
Tune up on Carrier oil furnace with matching Heat Pump and Boch oil water heater.
Weil McLain P468 Oil Boiler Tune up
Oil Burner Tune up of a Weil McLain P468, with Beckett Burner.
Replaced old defective Emerson thermostat with new Honeywell T4 thermostat
Energy Kinetics System 2000 repair. Replaced air vent and relief valve.
Amana Gas furnace with ac tune up.
Tune up on Amana air handler and Amana two stage heat pump
System check of Goodman air handler and Ruud condenser.
Tune up on Peerless Gas Boiler.
Replaced leaking boiler piping.