Louie was pleasant and efficient explaining the issue other he A/C
Arrived on site to perform diagnostic on 1 year old or less mini split. Homeowner had system installed by another company and has not been cooling for a couple days. Has been trying to get a hold of the company that installed it but has not heard back from them. Unit is not cooling and inside head unit is showing an F0 error code, which is associated with refrigerant. Hooked up gauges to unit and found system low on refrigerant which is causing outdoor unit to go into lockout mode. Went over findings and recommendations with homeowner as far as Adding refrigerant and locating a possible leak. While on site, the company that installed it finally gave the homeowner a call back and they said they will be sending someone out on Friday to see whatâ€™s going on with the unit. Homeowner wants to hold off on any repairs with us for now until the company comes out to see if they take care of it. System is not operational upon completion.
Repaired refrigerant leak. Pressure tested and vacuumed refrigeration system. Charged with fresh refrigerant by weight. Opened valves and found condenser coil leak. Called manufacturer and approved new unit to be picked up for installation. Left disconnect upside down.
Client will be purchasing system outright with a CHECK. If failure to pay for systems in check, and card purchase is decided then pricing will result to $30,290 taking away the $1,514 Cash/Check Discount.
Arrived on site to diagnose a unit that is shutting off and tripping breakers. Upon arrival spoke over withe client and she stated unit run but after a few minutes Ac breakers start to trip only for upstairs. Client cycled unit and unit turned on. Advised I would inspect unit. Found start up amps high and run amps where pulling at 22 amps and max is at 28 and advised on a hot summer day compressor is under more stress and could pull more or over max amps and trips breakers. Primary Starter is burnt up and pitted on contact. Secondary control is boarder line good and in range. Fan secondary control is good in range. Fan has been leaking a lot oil and and is Gunn a fail soon. Pressure did look in range but unit uses r22 and is no longer in production. Client stated another company came and did repairs adding booster kit and found out compressor booster kits where never added. Advised client compressor is bad and other unit could be in same condition if not getting to the same condition
Arrived on site and performed ac and heating tune up. Condenser had a lot of build up for its age. Cleaned it all off. Checked start components. They are good. Charge and temp split are good.
Inspected system low voltage wiring and re wired system circuit board.
Replaced old white icomfort thermostat with new S30 thermostat
Installation of Lennox Single Stage ML14XC1 A/C reaching a 16 SEER, including running of refrigerant lines and electrical 208/230 circuit. Permits Included Financing is $102/mo, if client chooses a paper payment they will receive additional 3% discount.
We will replace existing heater with a new one configured for propane including an emergency drain pan with furnace stands
Performed Furnace diagnostic on 2017 Goodman heater. Upon my diagnostic customer Had stated that he has had nothing but problems with the previous company that has been doing the contracting work for his house. He was told that his heat exchanger has a crack, that why the Carbon monoxide detectors are going off. Upon my diagnostic I first found the exhaust vent had been completely pulled off along with nothing but soot coming out of the vent. The reason for the high amount soot Was caused by a failure to convert natural gas set up to propane. This has caused the propane to form into this clogging up the heat exchanger. With the condition of the heat exchanger being filled with soot this is extremely unsafe and has ran like this since 2017 without being converted. Found that there was also no emergency drain pan, they disconnected primary line coming off of the evaporator coil along with none of the duct work being sealed up on the supply take offs. System was installed poorly and unsaf
Arrived on site to perform maintenance on 18 year old Rheem heat pump. Cycled system for heat. Checked systems electrical and components. Temperature split is in range, refrigerant levels in range however System is operating on r-22 refrigerant that has been phased out. Indoor blower motor has leaked out a significant amount of oil and amp draws are fairly high and inefficient. Primary motor control has some burning and pitting on contact points. Comrpessor amp draws are also high and condenser fan motor is leaking oil as well. Performed coil clean. Blower wheel is slightly dirty. Replaced 1 inch filter. Ducting is in very poor condition. Attic has enough space for a possible relocate in the future. Went over findings and recommendations with homeowner. She is fully aware of the condition of the system and is aware that she will have to replace in the future. She has gotten quotes in the future And have an idea on what a project like that would consist of. Offered to have someone come
Performed warranty. Found That gas pressure was dropping too low on systems when they would both kick on gas heat at the same time. Adjusted gas pressures on both units while they were both running in gas heat. Cycled systems together and individually. Systems are operating as they should and alternating between electric and gas heat accordingly. Systems are operational upon departure.
Arrived on site to perform warranty on system. Homeowner states they tried to turn on the heat and they got an error code and it didnt work. Error code 270 was displayed on both units, which is error code for no flame sensed on unit. Systems are both dual fuel units. Upon inspection of units found that settings are not set correctly on circuit board for dual fuel. Settings call for jumper W951 on circuit board to be cut in order for unit to recognize that it is a heat pump dual fuel application. Cut jumpers on both systems circuit boards, and reset systems for them to update changes. Cycled systems for heat. Systems came on and started heating, no error codes displayed on either unit. Noticed that thermostats were not connected to WiFi. Helped homeowner hook up both thermostats to WiFi and link them to her phone app. Ensured thermostats are communicating with phone applications. Cycled system, systems are operational upon departure.
Collected 700 deposit. Balance due will be 6253
Waived diagnostic, Mr.Russo considered furnace replacement and install will take place tomorrow