The service tech showed up timely, was very professional and friendly.
Louie was pleasant and efficient explaining the issue other he A/C
Performed diagnostic on a 2011 American standard heat pump. Customer reports no heat. Filter were extremely dirty. Outdoor unit is shutting on and off on low pressure. 4lbs of refrigerant was added to the system along with leak dye. System is running at heating at end of appointment. Return visit is needed.
Tech arrived on site, performed ac tune ups on 2 4 ton units. Cleaned condenser coils and checked refrigerant charge. Changed out both filters. Flushed drain lines and checked static. Hooked up both thermostats to Wi-Fi. Units are operational upon departure.
Performed heater diagnostic on 2020 Lennox Unit. Upon arrival homeowner stated that just about a week ago he noticed that the system continuously runs in fan mode and does not produce heat. During the troubleshooting I noticed initially that to the burners Appear to be orange and not burning properly. Also noticed rat droppings inside of the Furnace closet area. At this time it appeared that oxygen was not being supplied properly to the propane burners Resulting in a hard lockout causing rollout switch to be tripped. Previously the original Heater was also clogged up due to rats making it their home and stuffing debris inside of the heat exchanger Resulting in a similar problem. Also main door that covers up the furnace has no air circulation for oxygen the flow recommend that Louvers are added to increase Airflow to Heater. At this time burner Flames look healthy and blue. System is Heating upon departure
Performed heating maintenance on a 2020 Lennox SL280. Homeowner turned system on inside, unit started normally. Heating temperature split is 47 degrees. Filter had insulation and debris on it, homeowner wants to source his own filters. I cleaned the filter best I can. Sensors and switches were cleaned and tested. Gas valve was tested. Blower wheel and motor are clean and in range. Combustion blower is within spec as well. System is not electrically protected. Homeowner was briefed on the condition and signed up for scheduled maintenance. System was running at end of appointment.
Found outdoor system breaker left off by electrician. Reset the breaker and reset the low voltage power at the outdoor control module. Tested he equipment and the system is working properly again.
Technician arrived on site and performed ac tune up on 3 systems. Cleaned coils with chemicals. Cleaned out inside of condenser. Installed new wire management systems in electrical cabinets. Cleaned out electrical cabinets. Tested electrical components. Everything checked out. Outdoor fan motor on downstairs unit is failing. Most likely next year or sooner. Refrigerant charge is okay. Filters were changed. Drain lines were flushed out. Indoor units are dirty. Could not access the downstairs furnace at this time. Units are operational upon departure.
Repaired condensate overflow safety switch and glued properly with pvc glue. Re-installed a supply register in the guest bedroom which had fallen off. Programmed the thermostat for Ac from heat pump.
Tech arrived on site. Guest house has a Fujitsu mini split with 4 Cassette head units. coils were dirty and temperature split was low. Added 3lbs of R410A to the condenser. Cleaned coils. Temperature split increased and pressures looked better. Client said units had to be recharged before, indicating the unit has a leak. Did leak detection outside at the condenser but didnâ€™t find anything. To find the leak we would need to do an isolation test to determine which system is leaking. Units are operational upon departure.
Arrived on site to perform diagnostic on 1 year old or less mini split. Homeowner had system installed by another company and has not been cooling for a couple days. Has been trying to get a hold of the company that installed it but has not heard back from them. Unit is not cooling and inside head unit is showing an F0 error code, which is associated with refrigerant. Hooked up gauges to unit and found system low on refrigerant which is causing outdoor unit to go into lockout mode. Went over findings and recommendations with homeowner as far as Adding refrigerant and locating a possible leak. While on site, the company that installed it finally gave the homeowner a call back and they said they will be sending someone out on Friday to see whatâ€™s going on with the unit. Homeowner wants to hold off on any repairs with us for now until the company comes out to see if they take care of it. System is not operational upon completion.
Repaired refrigerant leak. Pressure tested and vacuumed refrigeration system. Charged with fresh refrigerant by weight. Opened valves and found condenser coil leak. Called manufacturer and approved new unit to be picked up for installation. Left disconnect upside down.
Client will be purchasing system outright with a CHECK. If failure to pay for systems in check, and card purchase is decided then pricing will result to $30,290 taking away the $1,514 Cash/Check Discount.
Arrived on site to diagnose a unit that is shutting off and tripping breakers. Upon arrival spoke over withe client and she stated unit run but after a few minutes Ac breakers start to trip only for upstairs. Client cycled unit and unit turned on. Advised I would inspect unit. Found start up amps high and run amps where pulling at 22 amps and max is at 28 and advised on a hot summer day compressor is under more stress and could pull more or over max amps and trips breakers. Primary Starter is burnt up and pitted on contact. Secondary control is boarder line good and in range. Fan secondary control is good in range. Fan has been leaking a lot oil and and is Gunn a fail soon. Pressure did look in range but unit uses r22 and is no longer in production. Client stated another company came and did repairs adding booster kit and found out compressor booster kits where never added. Advised client compressor is bad and other unit could be in same condition if not getting to the same condition
Arrived on site and performed ac and heating tune up. Condenser had a lot of build up for its age. Cleaned it all off. Checked start components. They are good. Charge and temp split are good.
Inspected system low voltage wiring and re wired system circuit board.
Replaced old white icomfort thermostat with new S30 thermostat