Jaime came back to install a fan motor in my furnace. The other ones we sass an original (18 yrs old). He also cleaned the blower blades. Now, I just have to let it kick in, run, and heat my house. If for some reason something goes wrong (it’s never happened) I know one call will get him back to trouble shoot and fix the issue (at no charge).
The crew was thorough and professional. Every aspect of the job was explained in detail with no surprises. A company you can trust.
Michael was very professional, gave me the straight poop on the condition of the heating system. We talked options, there was no pressure just a factual discussion. I very much appreciated working with him. Plus he likes cats!
We had to call for update for arrival time. No apology. Very disappointed!
Had a heating problem. Tyler showed up did his inspection/ testing on the unit located the problem, provided a clear/ detailed explanation of his findings and the solution then replaced a faulty component in no time. Tested the unit to ensure proper operation then cleaned up the work area. He answered all of my questions and before leaving he asked if there were any other questions? I didn’t, he was very thorough with his answers. He is very professional and has a positive attitude and it was a pleasure to someone that takes pride in their work. Great Job!!
The service tech was knowledgeable, he kept me updated on everything he was doing, he was very thorough in the work he had to do to get our extremely dirty furnace and air conditioner clean. He was also friendly, polite and followed COVID rules.
Hats off to George - top technician. Conscientious, great explainer ,should be valued employee.
Representatives were polite and informative.
Arrived on site to perform fall tune up on 2 2005 Lennox units. Both furnace located in attic. Upon arrival spoke to wife and she stated units have yet to be maintenance since they have lived there and would like system inspected. Advised to client I would be inspecting both unit for proper operation and efficiency. Cycled both units in heating and found unit thermostat was not operating properly due to being bad. Wife did want to replace both thermostat just to prevent future is or not operating. Upstairs was good. Filter were all replaced and supplied by husband. Found black flex ducting used and okay condition on both systems. Found blower as dirty from lack of maintenance in past years. Recommend replacing every 3 months to reduce amount of dirt from entering system. Wheel are both dirty creating high stress on motors. Recommend cleaning both blower assembly to reduce high amp drawls and run more efficiently. Both motor are starting to develop oil from over working. Down stairs is
Arrived on site to perform Fau maintenance on 2 17 year old comfortmaker units. Cycled systems for heat. Verified proper heating sequence of operations. Verified and tested heating components. Temperature rise across heat exchangers is within range but slightly higher than what we would like to see. Ran systems through 20 point inspection checklist. Systems are operating, but concerns with individual units are as follows: Upstairs Unit -indoor blower motor is leaking oil, amperages are slightly high -secondary motor control is out of range for indoor motor -inducer motor is working hard and is close to over amping -no sediment trap on gas lines -system ducting is not set up correctly and is not producing the capacity that it is capable of. This is causing unit to work a lot harder, and it is causing a lot pressure build up in the unit. - heat exchanger is starting to form a crack. Has not fully blown through yet, but indentation has started to form. This is a big concern as if it we
Arrived on site to do repairs on a 2001 Lennox unit. Came to replace a inducer motor and perform a blower assembly and wheel cleaning. Replaced inducer and cycled heating to ensure system is operational in heat mode. Pulled and cleaned blower assembly and installed again blower back in system and cycled cooling mode to ensure system operating properly. Cycled system with client in heating and cooling to ensure system operating and system is operational. System is operational upon departure.
Upon arrival performed maintenance and diagnostic. Client stated they lost power a few times last night. System did not turn on for heat after that. Replaced secondary motor control as it was low and out of range. Installed surg protector to protect electrical components. Blower wheel dirty, client denied to clean. Cleaned inside of furnace cabinet and dusted off all electrical. Gas valve and shut off in working operation. Circuit board in good condtion.saftey switches in working order. System was reset tested and fully functional upon departure.
Performed maintenance and cleaning for the heating equipment. Tested electrical loads. Measured temp splits. Inspected filtration. Tightened fittings. Verified refrigerant charge. Cleared condensate lines.
Performed furnace maintenance On 2010 Lennox system. Upon my maintenance there were a couple points of concerns that were addressed with homeowner. 1. Found that water leakage may have been coming from collector-box or secondary He change it also did not find any signs of cracks on the plastic or within the heat exchanger this could be from the past 2. Air restriction is very high on the system due to it being zone and itâ€™s only a one stage 90% furnace. Typically itâ€™s recommended to have a two-stage furnace when you have zoning due to airflow problems 3. Found the indoor blower motor is beginning to over amp due to oil leakage from bearing this may cause the motor to lock up or over heat. 4. Single secondary motor control is becoming weak due to motor using too much power 5. Scroll wheel is becoming kicked in dust and debris due to 1 inch filter is not filtering out dust particles efficiently recommend that filter rack is installed to increase filtration
Quality control check
Upon arrival found thermostat to be faulty. Does not engage for heating, replaced under warranty and installed a honey well T6 pro WiFi, replaced filter. System is operational upon departure.
Replace existing furnace with listed equipment. Remove existing asbestos vent pipe and replace with new metal double wall B-Vent. New gas and electrical connections. Install new digital thermostat. High Flow 5â€ filtration included. 3% cash discount or 18 months 0% interest available All manufacture and labor warranties apply to open box products
Installed ecobee thermostat on heat pump system. Charged for labor for one hour. System is fully operational and compatible with new thermostat. Recommended the system is maintain due to age.
Arrived on site to perform maintenance on 18 year old Rheem heat pump. Cycled system for heat. Checked systems electrical and components. Temperature split is in range, refrigerant levels in range however System is operating on r-22 refrigerant that has been phased out. Indoor blower motor has leaked out a significant amount of oil and amp draws are fairly high and inefficient. Primary motor control has some burning and pitting on contact points. Comrpessor amp draws are also high and condenser fan motor is leaking oil as well. Performed coil clean. Blower wheel is slightly dirty. Replaced 1 inch filter. Ducting is in very poor condition. Attic has enough space for a possible relocate in the future. Went over findings and recommendations with homeowner. She is fully aware of the condition of the system and is aware that she will have to replace in the future. She has gotten quotes in the future And have an idea on what a project like that would consist of. Offered to have someone come
Arrived on site to perform fall tune up on 2 2009 carrier furnace. Both Furnace located in attic. Client stated no issues. Cycled heating mode on on both. Both systems operational. Advised client I would be inspecting proper operation and efficiency and safety as well. Advised the summary of findings are as followed. Downstairs furnace 1. 2009 carrier furnace. 2. Found black flex ducting used and in ok condition. 3. Furnace Airflow is restricted as not enough airflow is entering system. 4. Filters are dirty and client supplies and replaces his own filters. 5. Blower assembly and wheel has dirt build up creating stress on motor. 6. Motor is now leaking oil and starting to leak oil in wheel from over working. Motor is pulling 7.1 and max rated at 10. Just indicating motor is working hard and if continues motor could possibly fail in future. 7. Secondary motor control is now weak. Recommend replacing before component completely fails and motor will not operate in heating and cooling.
Cash discount applied
Upon arrival performed maintenance. Inducer motors are close to factory specified max amp draws. Indoor motors are still leaking oil. Secondary motor controls are low and out of range. Flame sensors have a lot of corrosion does not clean off. Circuit boards have burn marks on terminals. Filtration is 1 inch filters, only filters about 30 percent. Systems need extensive cleanings. Distribution box is made from insulation, over time can deteriorate. Replaced both filters. Heat exchangers have a lot of heat marks, heat marks are signs of weak metals and metals that get to hot, did not identify any damages itself or broken stamps. Gas valve and shut off in working order. Heating order of operations good. Cycled heating system on and off. Cleaned and adjusted burners. 1. Blower wheels dirty 2. Indoor motors leaking oil 3. Secondary motor controls out of range 4. Circuit boards have burnt terminals 5. Systems have no water float switch 6. Heat exchangers have heat impingement 7. No s
Performance tune up on the heating equipment. Tested all electrical components. Measured temperatures. Wiped burner assembly and internal cabinet. Cleaned flame sensor and tested ignitor. Replaced filter.