Great service, Jimmy took his time and explained everything. The staff when I’ve called have been amazing as well. Thank you!
Luis was very courteous and excellent at communicating the work to be accomplished and making sure all my questions are answered then reviews the end product with me (and I can say this about every employee in this company I have worked with!).
George is friendly, incredibly knowledgeable, honest and an overall great person! You’re lucky to have a man like this on your team!
Professional, knowledgeable technician that took the time to explain what he acid and why.
Technician, Jimmy, was most helpful. Very professional as he went through the service steps then met with me to go over findings and observations. Appreciated his knowledge and advice.
Michael did an excellent job describing our systems and the work needed for improvement. Plan to sell house in next year so only reason we didn’t move forward.
I think Michael and Daniel did an amazing job, very thorough. Michael explained everything to where it was easy to follow along with what he was saying. Both of them were kind, courteous, helpful and patient. Cool Air Solutions, Thank you very much!
Installation of a new HVAC system went very smoothly and efficiently. New system appears to be working well.
Performed combo tune up on 5 year old carrier system. Cycled system through heating and cooling modes. Checked indoor and outdoor units. Checked system electrical and components. Pulled off condenser fan motor and Thoroughly washed out condenser coil inside and out. Indoor unit does not have any condensation safety switches on condensation lines, and door switch is no longer operating as it should. Outdoor condenser fan motor has started to leak oil, and secondary motor control has fallen out of range for fan motor. Disconnect box does not have any fuses inside of it for electrical protection. Went over findings and recommendations with homeowner. Signed homeowner up on monthly ESA maintenance program. He wants to take care of some repairs in the near future, will give us a call when he is ready to move forward. Cycled system, system is fully operational upon departure.
Combo tune up provided with install Technician arrived on site and began combo tune up of new Lennox system. Started with the furnace. Had green check across the safety sheet. Only item that needed attention is the filter. All motor amperage are good. Ignition components were good Ignition components were good. Safety switches are good. Everything is up to code. Went outside to the condenser and found the coil pretty dirty. Cleaned it with Chemicals. Checked all motor amperage. They are good. Temp split is 20 indicating a perfect charge. All readings are documented in the job photos.
Install Heatpump condenser on garage side of the home. Route refrigerant lines and electrical under the house to the indoor locations ( no exterior lines) Install Coleman downflow furnace in place of gas furnace. Modify cabinet for proper fitment. Relocate supply register in back TV room and abandon/seal supply under the couch. Financing available
After $1350 Lennox rebate total $24,350 Cash discount applied
Performed furnace maintenance on 6 year old Amanda furnace. Cycled system for heat. Verified proper heating sequence of operations. Temperature rise across heat exchanger is within range. Cleaned blower compartment as well as heating compartment and components. Indoor blower wheel is clean. Secondary motor control is out of range for indoor blower motor. Also system does not have any condensation safety switches. Filter was just replaced. Cycled system, system is operational upon departure. Emailing recommendations to owner.
Technician arrived on site and started performing combo tuneup on one HVAC system. Filter was completely restricted. And blower and electrical cabinet was dusty. Cleaned out the compartments. Ignition components were okay. Flame sensor and igniter are good. Blower cap is failing. Blower is over amping. Return is was to small and the static reflects that at .8 Unit tripped on high limit while service was going. Even without the filter. Blower wheel is caked with dirt. Temp split is over the rated amount. Recommend replacing unit as itâ€™s failing. Went to the condenser and cleaned the coils. Once cleaned started checking the electrical. Data plate was faded and couldnâ€™t pull ratings off. Compressor on start up was drawing high amps even with the hard start. Refrigerant charge is low. Suction line is icing up. Customer declined all recommendations at this time. Will possibly schedule repairs if the home inspector dings his unit.
Arrived on site to replace U.v light and catalyst kit in system. No work done on system itself and client is aware we just returned just to replace kit. U.V light is operational and lit. System is operational upon departure.
Performed AC/furnace maintenance free with install. Maintained AC system and heater inspection on 2020 Lennox system. Upon my maintenance I found that the condenser located outside was completely covered in dust and debris from the surrounding environment this was heavily restricted can cause complications and cooling if left in this condition and not cleaned off every year. Refrigerant pressures checked out properly and compressor amperage and outdoor fan motor were in range. Clean condenser coil as well. Further in the maintenance I performed a heating inspection/maintenance found everything checking out properly. Measure static pressure in range. Flame sensor was cleaned igniters is in proper resistance rating. Filter was swapped out recommend every year. Zone damper controls opened up on command. Indoor Blower motor good condition no oil leakage. Discuss full condition with Chris and recommended that he signed up for a maintenance plan to keep the system at a standard if condenser
Ordered parts found inducer draft motor fan to be rubbing plastics ordered from united refrigeration.
Performed furnace maintenance on 2 2008 York furnaces. Cycled furnaces for heat. Verified proper heating sequence of operations. Temperature rise across heat exchangers is within range. Cleaned furnaces exterior as well as blower assembly and heating compartments. Ran systems through 20 point inspection checklist. Went over findings and recommendations with homeowner. Homeowner wants to hold off on any repairs as she does want to replace the system soon. Asked if we work with Costco, advised that we do not work with Costco but we can price Match accordingly. Left replacement filters. Cycled system, system is operational upon departure.
Arrived on site to perform combo tune up on a 2013 Trane system. Furnace located in garage and condenser located in back yard. Upon arrival client stated she is having issues with thereâ€™s heater is not turning off. Advised I could diagnose and face fee and see what her issues. Cycled her thermostat in heating mode 3 times and system system was operating properly and fan dose have a delay after they shut off thermostat and their fan stays running to cool system down. Continue to do maintenance. Washed condenser inside and out checked all electrical compartment and components and wiring. Fan motor is okay condition. Primary control is starting to get pitting and dark discoloration on contact points. Secondary motor control is good and in range. He led amp drawls on compressor and fan motor. Compressor start up amps is almost at max as itâ€™s pulling 109.8 and max rated at start up is 120. Run amp are up pulling 8.0 amps and max rated at 14. Recommend adding a compressor booster kit to
Perform furnace maintenance On 2001 Lennox Heater. Did a safety inspection and electrical maintenance on heater. During the maintenance as I came across a few points of concerns that were addressed with the new homeowners. Furnace- 1. Found that thermostat was firing up in heating mode incorrectly by turning on the indoor blower first due to it being swapped into electric heat pump mode rather than gas mode. This is caused by the gas mode relay not working properly 2. Found single secondary motor control itâ€™s rating at 41.78 ÂµF +-5%. This is coming incredibly close to 42 and will be considered a weak motor control and will not be able to fire up or potentially cause the motor to over amp and overheat 3. Gas line did not have drip leg to increase life of gas valve. Not up to code. 4. Indoor blower cabinet was covered in dust and debris 2 to 1 inch filter not being swapped out consistently enough 5. Evaporator coil did not have secondary flow switch to prevent flooding that may occur
Replace existing system with listed equipment. 60 Month 0% interest or 144 months 4.9%
Tested and serviced both heating and cooling system. Replaced filters. Tested all components and cleaned both systems.
Upon arrival performed heating maintenance. Indoor motor is leaking oil, has some dirt and debree build up. Secondary motor control out of range. Blower wheel slightly dirty. Gas valve and shut off in working order. Dusted off all electrical connections. Circuit board and electrical connections good. Amperages throughout system good. Temp split at 50 degrees. Undersized ducting, restricting a lot of airflow system is currently performing at a 2 ton system. Ducts are not sealed at joints, there is a lot of air flow leakage. Could not do maintenance on other systemmas it is not functional, will follow up with client for part replacement. There is no emergency drain pan under coils. Heat exchanger has heat spots. System is operational upon departure.