Victor and Josh did an excellent job. They were very professional and worked until they were completed. Very happy.
He was on time earlier than I expected.
Good fast Service, technician explained the service he was about to perform and kept me informed of routine operations.
Perfect service The technician was very knowledgeable deserves to get a raise lol.
This is NOT company you want inside or around your home. The sales people are professionals. But the installers are way below par. They don’t show up at their scheduled time. They lack any respect or professionalism on site. Taking personal calls, talking slang and cursing aloud while they listen to music. Just to let you know during COVID while most are working from home and taking meetings, you can not have your installers answering calls saying “what’s up Bimbo?!”. Furthermore, they do not wear booties or face masks when they are inside your home. I expected for the price they’d be more respectful. I would NEVER recommend them to anyone EVER!
Daniel showed us all the photos of the maintenance his done. Explained in details. There was lots of mouse poops on the attic...Daniel offered to spread mousetraps for me. Since he said I'm up here right now. Might as well..He didn't have to do those extras. Had those mousetrap for awhile, very helpful young man, and friendly. Cool Air Solutions thanks for hiring your very best technicians...so far, every tech that you sent to my house are very knowledgeable. Im satisfied. Thank you! .
Our technician was incredible. Fixed the problem and took time to explain what he was doing every step of the way. Truly outstanding service.
Installation of a Lennox Single Stage 16 SEER A/C with Coil, Secondary Safety Switch, clean up, removal, and haul away.
Arrived on site to diagnose a 2000 units original to home. Client stated to start is not cooling home. He had had som repairs done in past as he last replaced a part last summer. Cycled unit and system was not operational and tripping breaker. Advised client I would inspect unit. Found secondary motor control is completely dead and when turned on wood trip breaker as compressor kept trying to turn on but wouldnâ€™t. Also found primary burnt up and pitted due to age and condition. Secondary completely bad. Fan motor has been leaking oil in past as motor is covered in oil and pulling max amps. Compressor starting up hard. Recommend compressor booster kit to help keep start ups low. Run apps pulling 15 and max rated at 24. System is cooling hole at 20 degrees. No protection on unit and recommend adding surge protectors to unit to protect from electrical surge and power outages. Went over all findings and recommendations with client and areas of concerns. Client is aware of how system is r
Technician arrived on site, found 1 hvac system. Unsure of age and size due to the data plate being faded. Service panel on the condenser is missing. Cleaned coils and checked charge. It was low. Temp split is 15. Amperage on fan motor and compressor are high. Cap is barely within range. Scheduled a consultation with a CA for tomorrow.
Upon arrival performed maintenance on Hvac system. Indoor motor and wheel are in good condtion. Heating order of operation in range. Dusted off all electrical. Burners cleaned. Circuit board and electrical connections good. Client declined membership, since we did tune ups today. Open e up entire outdoor system and cleaned coils. Amperages on compressor and fan motor in range. Refrigerant levels good. Disconnect good. Secondary motor control on fan side is out of 5% range. System passed inspection.
Arrived on site to perform spring tune on a 2004 comfort maker system. Condenser located in back yard. Furnace and evaporator coil located in attic. Client stated no issues and that he know system is old but is still operational and cooling. Washed condenser inside and out. Condenser was rebuilt last time out. Primary, secondary and fan motors are all good. Unit also has a compressor booster kit as well. Compressor start ups are low and good. Run amps is still working really hard and he is aware as itâ€™s pulling 22 amps and max rated at 27. Lennox n a hot summer day Thai compressor can over work and even fail. Pressure are stable and cooling home at 20 degrees. No protection on unit. Inspected indoor unit. Filter is dirty but client will replace him self. Blower assembly is dirty. Motor is good. Secondary motor control is good as well. Evaporator dose have debris from past years of dirt entering system. Drain do not have any over flow safety switches. Would recommend adding one to p
Technician arrived on site. Call was for low airflow upstairs. Unit had been replaced about 3 years ago. Along with the ducts. Downstairs is cooling great. Upstairs is getting almost no airflow. Found a 12 in duct supplying the entire upstairs. As a result there is no airflow. Talked about relocating the unit to the attic. Need to get field supervisor out here to do a job walk and provide estimates.
Performed maintenance on 16 year old Trane equipment. Homeowner states that he had a company maintenance the equipment a couple months ago and they told him everything was fine. Wanted to take advantage of special and check the unit again before summer time. Cycled system for cooling. Checked indoor and outdoor unit electrical and system components. Temperature splits is in range and system is cooling correctly. Checked outdoor unit electrical and system components. Pulled condenser fan motor off and thoroughly washed out condenser coil inside and out. Concerns are as follows: 1. No secondary drain line coming off of evaporator coil in attic. Even more concerning there is no safety condensation switch to prevent any water Damage in the event of a clog. 2. Amp draws for outdoor compressor are extremely high and unit is working hard and very inefficiently. 3. Condenser fan motor is also over amping and has also started to leak some oil. 4. Unit is operating on r-22 refrigerant, which ha
Upon arrival performed motor and secondary motor replacement. Programmed motor to correct hp and rpm. Tested system and verified it works.
Arrived on site to perform spring tune up on 2 2009 carrier units. Both condenser located on side of home. Other furnace and Evaporator coils located in attic. Clients stated no issues. Replaced filters. Washed condenser coil inside and out. Both units good. Checked electrical compartment and components. Found both primary and secondary motor controls are good and both in range as these parts have been replaced in past. Fan motor on upstairs is good and new and downstairs is original and leaking oil from working at max amps. Checked compressor start amps on both and are good. Run amps on both units are in range at this time. Checked pressure and are good and cooling upstairs at 22 and downstairs at 20 degrees. Advised client no protection on oth units. Inspected indoor units. Blower assembly are good upstairs motor is leaking oil and high on amps. Downstairs motor is good amps are good n range. Both secondary motor controls for both motors are bad and out of range. Recommend replacin
Performed AC maintenance on 11 year old carrier unit. Cycled system for cooling. Checked systems electrical and components. No safety switch on condensation line. Blower wheel is starting to accumulate dust. Checked outdoor unit electrical and system components. Amp draws for compressor are within range. Condenser fan motor amp draws are within range but on higher end of range, and has already starting to slightly leak oil. Primary motor control is in good condition. Secondary motor control is within range. Pulled condenser motor and thoroughly washed out condenser coil inside and out. Refrigerant levels are in range and system is producing proper temperature split. Went over findings and recommendations with homeowners. Homeowners fully aware of condition of system and any concerns. Renewed ESA maintenance program, would like to keep it on yearly program. Cycled system, system is operational upon departure.
Upon arrival performed maintenance on ac system. Refrigerant levels in range. Primary nd secondary motor control good. Hardstart kit in working order. Replaced filter client provided. Disconnect Iâ€™m great condtion. Opened up and washed outdoor system. Dusted all electrical connections. Wiped down furnace cabinet. Client stated he heard a clicking noise on heat, ran heat did not hear anything checked wiring or lose components.
Performed AC diagnostic on 2007 Ducane Condenser. Upon my diagnostic Mario stated that just a couple months ago The heater had issues with the circuitboard and it needed to be replaced and now the AC doesnâ€™t turn on. The first place I went was to the thermostat and turned the system on to cooling and there was a tremendously long delay. Removed thermostat and jumped out cooling and everything fired up. Proceeded to the addict define that the system is a dedicated horizontal Ducane Inspected the circuitboard and found multiple burns and heat spots. Also found that the indoor blower motor was leaking significant oil from the bearing. Inspected outdoor unit and measured refrigerant pressures to find that the system has major air Restrictions. Refrigerant charge checked out although it does have a Phased out refrigerant called R22. Measured duel secondary motor control that powers compressor and fan and found that it was weak on the compressor side. High-voltage relay was also pitted on
Performed tune up for the cooling system. Replaced filter up bulb and catalyst. Recorded temperatures and voltages. Measured amp draws. Tested controls. Cleaned condenser coil.
Collected 7000 deposit. Balance due paid with 6.99% apr will be 6126
Installed daikin 1 thermostats and translating hubs. Manually configured thermostats for operation.