Great! Promote him and double his pay
Trevor was extremely helpful in fixing the condenser drainage pipe on our AC unit. He fixed quickly and now we no longer have any water pooling near our house. Trevor also replaced our filter, cleaned out our condenser coils, and outside unit. He was very thorough and took the time to answer all of our questions. Excellent service and we are very happy with his work!
Performed maintenance on a Lennox condenser and a Carrier condenser. Both units were chemically washed. Filters are clean. Continued maintenance was setup. Both units are operational at end of appointment.
Arrived on site to perform combo tune up on a new lennox unit. Cons in back yard and furnace located in garage. Cleaned out door unit for inspected electrical compartment all electrical is good. Fan motor as well. Checked company draws and are good. Pressure are good and holding charge and cooling at 19 degrees. Filter was dirty. Cycled heating. All safety switches are are good. Both motors are in range of amps and heating home goods. Drain lines are good. Temperature split is good and heating home. Cycled unit and went over unit and recommended client did declined filter and ESA maintenance plan. As she didnâ€™t think she needs one yet as unit is new. Unit is operational upon departure.
Performed furnace maintenance on 2013 Lennox heater. Upon arrival homeowner stated that system has had no issues and has been working properly. During the maintenance I did find out the single secondary motor control Will be coming week on the indoor blower motor. Also the single second remote control on the inducer motor was leaking a ton of oil. Temperature rise checked out properly. Flame sensor was cleaned and hot surface igniter is in proper range. Client will swap out Merv 16 filter during the summer. System was not equipped with surge protection. Burning flames appeared healthy and upon departure system is fully operational and heating
Upon arrival performed repairs. System is operational.
Upon arrival performed maintenance on on Goodman system. System is 2017 very new still. Dusted off all electrical components. Indoor motor and wheel in range. Circuit board and electrical connections in range. Filter is dirty, client ordered some on Amazon. Surge protector in range. Static pressures on system in range. Flame sensor cleaned. Gas valve in working order, system is operational.
Upon arrival performed maintenance . Found inducer draft motor to run higher amperages that are needed. Flame sensor has a lot of oxidation build up. Inspected heat exchanger through blower compartment, seen a stamp that looked like a crack. Advised home owner I cannot see it completely fine. Asked for approval to pull exchanger out. Got approval pulled exchanger and found crack on first chamber and plenty of stamps that look like they formed a crack. Client did not want to replace system, would like to replace defective parts. System is not operational for heat. Have gas shut off.
Upon arrival performed light installation, found entire ballast to be out and not operational. Replaced whole entire kit. System is now operational .
Performed AC maintenance on a 2011 Amanda condenser. Cooling temperature split is 21 degrees. Condensate lines are clear but platform shows signs of overflow. Recommending a safety switch. Indoor unit is not protected. Duct runs are sealed. Outdoor unit was chemically cleaned. Compressor bay and service panel was cleaned. Starting components and amp draws are ok. Compressor run amps are high. Refrigerant levels are ok. System was cycled before end of appointment.
Upon arrival performed maintenance on hvac system. Client signed up other system for plan as well. Wel will be servicing second unit for master bedroom. UV light is out and not operational. Indoor motor and wheel good. Circuit board and electrical connections good. Refrigerant levels good. Temp splits good. Filter was replaced client provided. Washed outdoor coils and inside of condenser cabinet. Tested system on and off. System operates at standards. System was reset tested and fully functional upon departure. Ordering UV light
Returned to perform repairs. System was basically flat on refrigerant on arrival. Recovered remaining refrigerant from system as it was too little to be pumped down. Unwelded existing line drier, rewelded new line drier in to system. Pressurized unit with nitrogen to ensure no leak, as well as bubble tested welds. Removed nitrogen and put system on a vacuum. Vacuumed down to 560 microns. Recharged system with 10 pounds of R410A refrigerant. Refrigerant pressures are back in range and system is operating as it should. System is fully operational upon departure. Homeowner approved to charge card on file for remaining balance over the phone.
Performed diagnostic on 5 year old unit. Homeowner says unit is not cooling. It is blowing air but it is not cold. Checked outdoor unit electrical and system components. Checked refrigerant pressures and found unit to be low on refrigerant. Performed leak inspection and found leak at outdoor liquid line drier. Line drier needs to be replaced. Unit is also low on refrigerant from leaking and will need refrigerant. Went over findings and recommendations with homeowner as well as the process for replacing liquid line drier and all the steps involved with that process. Homeowner would like to move forward with repair. Collected $169 as down payment, remainder to be collected when we return to perform work. System is not operational upon departure.
Performed diagnostic. Tenant states that system is making a weird noise. Tenant was not on site and was not able to get a hold of him via phone, unsure what noise he was hearing. Checked system thoroughly and started unit up various amounts of times. Unit started up normally every single time. No weird noises coming from the unit. System amp draws are within range and temperature split is cooling correctly. Replaced filter with customer supplied filter. Let property manager know everything is in working order. System is operational upon departure.
Performed AC diagnostic on two year old Goodman system. Upon my diagnostic client stated that system is not able to drop temperature throughout the day and was able to get to 67Â° in the past and now it doesnâ€™t get below 75. Found at the outdoor condensing unit to do a secondary motor control has become Defective on the hermetic side terminal which means the compressor wasnâ€™t on. Installed new duel secondary motor control system is cooling with a 15Â° split differentials and refrigerant pressures look good at this moment. Part was covered under warranty and upon departure system is fully operational and cooling.
Performed AC maintenance on a Armstrong air condenser. Systems cooling split is 20 degrees. Condensate lines are clear. Indoor blower is amping ok and spinning freely. Outdoor unit was chemically cleaned. Coil fins have a a good amount of corrosion due to the salt in the air. Copper line set have also been effected with corrosion. Refrigerant levels are ok. Compressor and fan amps are ok at this time. Corrosion inhibitors were installed at this location and his house down the street as well.
Performed AC maintenance on a Comfort Pro condenser. Cooling temperature split is 21 degrees. Indoor blower motor is amping in range. Condensate lines are clear. Outdoor unit was chemically cleaned. There is slight corrosion on the copper refrigerant lines due to the salt in the air. I am recommending adding a corrosion inhibitors to halt any further corrosion. Compressor and fan amps are in range at this time. Refrigerant levels are low.