Great! Promote him and double his pay
Trevor was extremely helpful in fixing the condenser drainage pipe on our AC unit. He fixed quickly and now we no longer have any water pooling near our house. Trevor also replaced our filter, cleaned out our condenser coils, and outside unit. He was very thorough and took the time to answer all of our questions. Excellent service and we are very happy with his work!
Emailed client 5 ton upflow gas furnace in garage with seal platform included.
Need to open up call for Andrew to email quote to customer, to approve system replacement .
Upon arrival performed diagnostic. Switch was tripped checked system, running good replaced filter. B vent is good. System was reset tested and fully functional upon departure.
Furnace tune up in Encinitas, Ca.
Refrigerant recharge for a Maytag system in Encinitas, Ca.
Lennox system diagnostic and repair in Encinitas, Ca.
Fall Maintenance 12/28/2018
SDG&E assessment in Encinitas
Performed routine fall maintenance on Amana furnace
Installed whole home Hepa air purification system.
Air conditioning airflow assessment in Encinitas
Drain pan replacement in Encinitas