Great! Promote him and double his pay
Trevor was extremely helpful in fixing the condenser drainage pipe on our AC unit. He fixed quickly and now we no longer have any water pooling near our house. Trevor also replaced our filter, cleaned out our condenser coils, and outside unit. He was very thorough and took the time to answer all of our questions. Excellent service and we are very happy with his work!
Arrived on site to perform main on a unknown age system. Upon arrival spoke over with client and she stated she just moved in and wanted system inspected. She stated another company came out as was unable to service system due to the type of system and no access to work on system. Inspected and house only has heater and no Ac. Over all found system is a hydronic heater and we would not be able to not service this type of system due to the type and no access in attic for air handler. Client cycled heating and system was operational. Client is aware no work was performed just was able to educate client with the type of system it is. Client is aware why were unable to service this system. System is operational upon departure.
Arrived on site to inspect issues with thermostat. Condenser is in back yard. Furnace and evaporator coil located in garage. Client just moved in as previous owners transferred all over information to current owners. Client is having some issues with setting of thermostat and unable to used remote access on there phone. Client bought nest thermostat recently and replaced other systems with it and would like to replace S30 with a nest thermostat. InspectEd system and thermostat and advised client due to the type of equipment he is unable to use nest thermostat since his equipment is all communicating and is not compatible with wiring up a nest thermostat. Client is aware and ok but would like for me to help him reset all equipment so he can enter correct email and account info so he can use remote features from phone. Was able to factory reset equipment and got current Owners information in thermostat. Client is now able to control system from phone. Set thermostat and cycled cooling mo
Upon arrival performed maintenance on 2 furnace systems. Replaced bad secondary control on ac system. Was gonna replace disconnect on non operating unit. Found fan motor to be seized. Indoor motors are in very good standing. Evap coils are both very clean. Blower wheels are very clean. Replaced all 4 filters. Circuit board and ale tricks connections in very good condition. System is in very good condition. Home owner does not use systems very often. Systems were reset tested and fully functional upon departure.
Upon arrival performed maintenance on 2 Lennox ac systems. Refrigerant levels and temp splits in very good condition. Secondary motor control control and primary in range for 3 ton. Refrigerant levels very good. Filters dirty. Amperages throughout system good. Condenser fan motor in good condition. Start amps and run amperages good. 2nd system, refrigerant levels very good. Temp splits have been recorded and are in range. Secondary motor control out of manufacture range. Customer declined to do repairs. Primary motor control good. Compressor start amps beginning to climb higher. Compressor running higher then 80 percent manufacture rating. Condenser fan motor good. 3rd system. Could not maintenance due to no disconnect plug. Returning tomorrow to replace all filters finish maintenance and repairs.
MAINTENANCE X2. Found systems operational upon arrival. Replaced 2 16x25x1 washable filters. Ductwork is original from 1988-1990. Certain areas are weak and may collapse. Connections are not sealed. Ductwork is not strapped and hung for better design. Customer approved duct replacement with redesign and new cut in return. Appointment set for September 25th, 2020 to replace and install new ductwork. Blowers are dirty and leaking oil. Evaporator coils are getting build up from dirt bypassing filters. Freon levels are within range but the freon is discontinued r22 and may not be available soon. Both condenser motors are leaking oil which is a sign of motor overheating. High voltage line switches are showing burning and pitting. Motor controls are within range at this time. Comfort advisor set to come by after 4pm to go over replacement options as well. Collected deposit and maintenance charges today. Units operational upon departure.
Upon arrival performed maintenance. Indoor motor is in good condition. Secondary and primary motor control good. Salt water causing terminals to corrode. Temp splits very good. Refrigerant levels are very good. Circuit board and electrical connections in very good condition. System has a lot of corroded parts due to so close to salt water. Filter was replaced. Recommend adding hardstart kits and surge protections to keep system healthy. System was reset tested. Closed home no one was there. Finished maintenance. System is operational upon departure.
Upon arrival performed spring maintenance. Indoor motor is in very good condition. Blower wheel very clean. Replaced 14x25 filter. Refrigerant levels in very good standing. Temp splits very good. Amperages throughout system very good. Recommend adding surge protections to keep circuit board and electrical components in healthy standards. Indoor system was dusted off making sure there is no dust on terminals or circuit board. Outdoor system was washed off, made sure coils were clean and in very good condition.
Lowered the cfm for the blower motor at the thermostat to reduce the sound of the air moving through the return vent. Tested the system on both stages of cooling to confirm the change.
Install listed Lennox 3-Ton cooling system to existing furnace. Install customer supplied nest wifi thermostat. Run new copper refrigerant lineset, 220V 30 Amp electrical and Condensate lines in customer provided trench underground. Asbestos abatement, add volume control dampeners to force more air upstairs and re-insulate exposed garage ducts
Performed routine fall maintenance on comfort pro furnace in encanitas
Emailed client 5 ton upflow gas furnace in garage with seal platform included.
Need to open up call for Andrew to email quote to customer, to approve system replacement .
Upon arrival performed diagnostic. Switch was tripped checked system, running good replaced filter. B vent is good. System was reset tested and fully functional upon departure.
Furnace tune up in Encinitas, Ca.