Great service, team was very neat and clean
It was absolutely a wonderful experience, fast and friendly answered all my questions and concerns. I was left with a feeling of reassurance and no worry.
Mr. Garcia, fixed my cooler and did a clean job . He waz very efficient too. Thank you much.
Very professional and helpful!
On time, called ahead to confirm appointment, very detailed and informative. Would continue to use Cool Air Solutions and suggest others to call them for their HVAC needs.
Very informative abs helpful
Daniel is very knowledgeable, he carefully explained everything and is honest, he will not try to force you to buy something that you don’t need, unlike other companies, will request him to do my maintenance all the time, he’s an exceptional employee.
Upon arrival found upstairs to be getting most of the air flow. Advised client dampener would help fix that solution. Client wants to try premuim registers before anyth8mg else.
Performed diagnostic on 1989 carrier unit. System is leaking water onto the garage and platform. Noticed it a couple days ago. They just moved in two months ago and do have a home warranty. Cycled system for cooling. System turns on and is cooling. Blew out and Tested primary drain line with water to ensure proper draining from system to the outdoors, water flowing correctly. While system is operating there is slight condensation coming out of outdoor pipe, but there is also water leaking through the inside of the system. Conducted all the tests necessary to determine that primary drain pan is compromised which is allowing water to leak out through the inside of the unit. Furnace does appear to be rusted inside which is indicative that this has been on going for a while. Sealed up primary drain line. Also inspected ducts in attic and found some connections coming off as well as a compromised transition box that it allowing air to leak into the attic. Went over findings and recommendati
Arrived on site to diagnose a 1991 furnace found a 2005 condenser she stated she just replaced last year. Upon arrival client stated they just had solar done and now unit will not produce airflow now. Found outdoor unit iced up from the indoor unit to the whole out door unit. Inspected indoor unit and found blower motor completely dead. Secondary control was bad. Found filter in unit and has been in system for almost 2 years. Whee is covered of dirt and build up. Build up is creating stress and making motor work hard. Advised motor and secondary need to be replaced and needed cleaning. Advised unable to inspect full system due to bad motor and not working properly So she is aware unable to tell her if that is her only issues this is just a start to get system running. Client is aware and stated she is interested in system replacement and would like to go over options as she dose not want to put money in to old units. Turned call over to mateo as he came out to give system replacement
Arrived and cycled unit in cooling mode. Turned turbo o and let system cycle. Checked pressure and are good. Client stated she did not feel airflow. After system ran for 15 minutes pressure were good and she was happy with the airflow now and how unit was cooling. Advised client I did nothing to improve cooling or airflow but she was happy advised client on hot summer days manufactured home retains heat and system is working good and the best it can. Cycled system to ensure system operating. System is operational and cooling upon departure.
Tech arrived on site. Found secondary motor control to have failed. Starter is pitted. Fan motor is leaking oil. Schrader core is leaking refrigerant. Client said they are moving and wanted a bandaid repair without membership. Replaced secondary motor control. Compressor started up and drew LRA. compressor amps are high. Fan motor amps are okay. Unit has high super heat. Unit is operational upon departure.
Installed blower motor with new battery cap. Service finance #3059856
Performed AC maintenance on a Lennox system. Units cooling temperature split is 26 degrees. Condensate lines are clear and equipped with a safety switch. Indoor blower is clean and amping ok. Filter is dirty. Outdoor unit was dirty and chemically washed today. Compressor bay and service panel were washed. Compressor and fan amps are in range at this time. Electrical components are ok. Refrigerant levels match manufacturers spec. UV protection was added to the outdoor unit. System was running at the end of appointment. Customer needs to talk to wife for decision on the comfort club.
Cut and cleared condensate drain. Safety switch had water on arrival, cleared line of rust from previous system, verified drainage with water.
Total after all rebates would be 14000.
Inspected system for operation. Tested pressures and temperatures. Replaced filter. Inspected ducting in the attic space as well.
Tested system for faults, found defective fan motor run component.
Upon arrival performed diagnostic on hvac system. Clients grandson booked the call. Client said breaker was in a weird position in electrical panel. Found filter to be extremely dirty. Outdoor coil is completely covered. Found secondary motor control was out of range, replaced and retested system. Disconnected compressor wires and system kicks on no problem, once compressor is added instant short. System is non operational. Client grandson will speak to grandpa.
$11,203 due upon completion. After Lennox rebate total $10,803 0-Down $129 per month
Performed AC maintenance on a Goodman condenser. Cooling temperature split is 21 degrees. Condensate lines are clear and do have a safety switch. Evaporator coil in the attic does not have a drain pan, customers are aware. Indoor amp draws are in range. Outdoor coils were chemically cleaned. I applied a UV resistant wax to the condenser. Starter had heavy pitting, this part was replaced today. Compressor and fan amps are in range. Refrigerant levels are ok. System was cycled before leaving.