Michael Pierson was outstanding. Very professional. Highly recommend!
Supervisor Darrin was very knowledgeable about the product and and helped us to determine was packaged was best for us
The service tech Jimmy was very helpful and explained all of our options on repairing our AC unit!
Your technician Michael represents your company well. He takes great pride in his work and I appreciate that
Technician (Jimmie) On time, with details of the complete repair. Started right away with complete clean up.
Tyler is the best explained all my options for my repair and really kind
On time and informative.
The tech was very informative n pleasant to speak with. Shared in detail the workings of my system.
Performed AC maintenance on two systems Goodmans 15 years old. Upon my maintenance I came across a few points concerns and they are- Upstairs 3 ton- 1. Found the condenser fan motor is leaking lubricant from bearing and shaft 2. Found that battery Is weak on hermetic side terminal due to compressor pulling high amps 3. High voltage rely showing signs of pitting on contact point 4. Found the compressor was pulling 10 A on 70Â° day this can be a problem once the summer hits and put the system in a higher risk of failing 5. Fan motor was also over ramping due to lubrication leaking out 6. System extremely low on R22 refrigerant Downstairs 3 ton- 1. Found the condenser fan motor is leaking lubrication from bearing shaft as well 2. High voltage really showing signs of pitting on contact point 3. Fan terminal on the battery cap Rating 5.2 this is considered out of range on data plate 4. Compressor also pulling high amps at 10 also
Arrived on site to perform spring tune up on a 2016 Lennox system. Condenser located in back yard. Furnace and evaporator coil located in attic. Client stated no issues just wanted to get system hacked up on and replace filter. Client tune cooling on. Thermostat was good. Did indoor nit inspection. Insulation is good. Found filter to completely clogged and restricting air flow to system. Advised this is really bad and need to be replacing filter about every 2 months Due to home surrounding by dirt fields. Blower wheel is dirty due to lack of filter change out. Build up is creating stress on motor. Blower motor is good and oil free. Found secondary motor control for blower motor is bad and out of range. Recommend replacing before completely gives out and system will not have any air flow. Evaporator coil is clean at this time. Drain lines are good and clean and draining. Temperature split is in range and cooling. Cycled system to ensure system operating. Washed condenser coil inside an
Drop off room ac
Pre job walk
Replace existing system complete with listed equipment, seal all supply cans and install high flow register set. Seal return air base and skin platform with sheet metal. Permits and HERS included
Cancelled at the door. No show.
Diagnostic is waived, customer opened up system yanked out wires no schematic. System is doing a very loud buzzing noise coming from primary distributor. System is 1987 customer is having financial problems, she will follow up this is her moms house and will see if she can qualify for new system. Waived diagnostic did not touch system system was already opened.
Performed AC maintenance on 14-year-old 5 ton in 2 1/2 ton condensing . unit. During my meetings I came across a few points or concerns that were addressed and documented. 5 ton- 1. Found the disconnect terminals melted into line voltage and load keeping system under 120 volts on one leg on contractor. 2.5 ton- 1.System contains R22 refrigerant which was phased Jan 1 2020 2. Disconnected not contain any fuses or surge protection 3. Contactor showing signs of pitting on contact point 4.Fan motor pulling below amps and compressor 5.System appear to be overcharged slightly
2 system ac maintenance
Checked system for functionality. Replaced filters. Tested thermostats. Inspected indoor unit and condensate drain line. Tested cooling and measured indoor temperatures. Measured outdoor system voltages and motor amp draws. Checked electrical controls. Replaced line set insulation. Cleaned outdoor condenser inside and coils. Verified refrigerant charge.
Replaced low voltage fuse in furnace circuit board. Helped customer with new thermostat, checked filters. Tested system on cooling and measured temperatures. Verified charge. Tested voltages and amp draws. Replaced line set wrap.
Performed AC maintenance on 2016 Lennox Package unit. Cycled system for cooling. Checked package unit electrical and system components. Indoor blower motor secondary motor control is within Range. Compressor and condenser fan motor secondary motor control is within range. Primary motor control is in good condition. Evaporator coil is starting to get dirty, recommended replacing filter more frequently. Pulled off condenser fan motor and thoroughly washed out condenser coil inside and out. Washed exterior of unit. Replaced 1 inch filter. System refrigerant pressures are in range and system is producing a perfect temperature split. Went over findings and recommendations with homeowner. They wanna hold off on the maintenance program for now, but will be calling us in the winter to have us come out and do the heater maintenance and sign up on the ESA Maintenance Program. Cycled system, system is operational upon departure.
Doing a repair out here in Lake Elsinore
Performed AC tuneup on 3 ton two system condenser. Upon maintenance found that downstairs system suction line was icing up due to indoor blower failing. Downstairs 3 ton aire-flo 1. Found the indoor blower failed causing suction line to ice up and form ice with an evaporator coil. 2. Hardstart no longer supplying proper micro reading to support Lock rotors on start up 3. High-voltage really responsible for starting system showing signs of pitting on contact point along with high ohms on low voltage coil which can lead to shorts or popping fuses in attic 4. System may be low on R22 refrigerant Not for sure until indoor blower is fixed to check pressures 5. Suction line insulation falling off 6. Disconnect did not contain any fuses or surge protection Upstairs 3 ton 1. Found the compressor failing on lock rotor start ups while under a load, Is causing compressor not start when called for this can be intermittent 2. Found that system was pulling 12 A on an 85Â° day this amperage will inc
Returning Friday at 10