Good service how would you rate your
Jorge was very polite and very informative.
Great service, team was very neat and clean
It was absolutely a wonderful experience, fast and friendly answered all my questions and concerns. I was left with a feeling of reassurance and no worry.
Mr. Garcia, fixed my cooler and did a clean job . He waz very efficient too. Thank you much.
Performed AC/furnace maintenance on 2020 Lennox systems. Perform safety inspection on heater. temperature rise are is at proper level. 5 inch Merv 11 filter is heavily plugged up in restricted recommend this is swapped out immediately client says that they are ordering one off of the Internet. Performed AC maintenance. Clean the condenser coil due to high amounts of debris building up. This needs to be done once a year just before the summer to ensure proper efficiency and maintain warranties on Lennox unit. Refrigerant levels are in range. Compressor and fan Are pulling the proper amperage. At this time system is in great condition and recommend to keep this unit at a standard Maintenance is done twice a year to get the longest life out of it. Client stated that his wife is working at the moment and when she gets home he will go over maintenance plan and itâ€™s about a few days to think about. Left maintenance program brochure It will be following up soon. Upon departure System Is ful
Arrived on site to perform diagnostic. Homeowner just took back possession of home after it being a rental for a couple years. Heating is not operating. He had someone else come out and told him that there were wires that were cut inside the furnace. He does have his insurance company coming out on Monday to look into this issue as well as other issues in the home. Cycled system for heating. Unit is completely unresponsive. Went into attic to inspect unit. Opened up unit and found that several wires have been pulled off from circuit board as well as ignition board. Ignition board looks like it has been replaced and all the wires are a complete mess. Unit Is not recieving command from thermostat due to disconnected wires. Went over findings and recommendations with homeowner. He wants to hold off on any repairs until his insurance company comes out on Monday. Also wants to hold off on any maintenance work as the home is going to be for sale. Closed unit back up. Unit is not operational
Performed AC/heater maintenance on mini split five head Lennox unit. Upon arrival client stated the downstairs system on mini split A Who is not working to performance as stated by the tenant living below. Initially asked the tenant she stated the system has no problem right now. temperature split checked out properly with a 30Â° delta split on downstairs head. Cleaned up condenser coil and electrical compartment. Amperages are in range for compressor and fan. All filters were clean by client. system is cooling and heating properly at this time.
Performed AC maintenance on a pair of carrier condensers. Downstairs unit is cooling over 20 degrees. Condensate lines are clear but have no overflow switch. Battery cap for the blower motor is failed and causing damage to the motor. Burned diodes on the control board. Outdoor unit was deep cleaned. Starting components were measured and verified ok at this time. The battery and starter and fan have been swapped on this unit. Surge protection was also added previously. Refrigerant levels are ok. Upstairs unit is cooling over 20 degrees. Condensate lines are clear but have no overflow switch. Battery cap for the blower motor is failed and causing damage to the motor. Burned diodes on the control board. Outdoor unit was deep cleaned. Battery cap for compressor needs replacement. Refrigerant levels are ok. Compressor amps are high. Homeowners are very busy with work. The husband is aware of the condition. Both systems were operating at end of appointment.
Arrived on site to perform diagnostic on 10 year old package unit. Homeowner states system is not operational at all, fan is not even turning on and he believes there is a blown fuse up on unit. Went on roof and Checked package unit electrical and system components. System is recieving proper high voltage power, but no low voltage power present. Found a bad 5 amp fuse on circuit board not allowing system to turn on at all. Replaced fuse and tested unit to check for any electrical short. System cycled on and started running, fuse no longer blew out. Homeowner made comment that his system does not cool very well in the summer time. The system was here when he purchased the home. Performed thorough evaluation of system to figure out why system does not cool correctly. Upon attic inspection, found that ductwork is in horrible condition. Actually found that the return duct had completely came off the unit, and system is pulling all the air in from the attic and not from inside of the home,
Performed furnace maintenance on 16-year-old Gibson furnace. Upon my maintenance I went to thru a safety/electrical inspection. I found a couple points of concerns that were addressed with homeowner. Furnace- 1. Indoor blower motor has significant oil leakage coming from bearing. This can lead to the motor locking up or overheating. Indoor blower motor supplies air for both heating and cooling in the home 2. Flame sensor was slightly oxidizing from wear and tear over the years 3. Inducer draft motor is over amping at 2.86 A When it is rated for 1.5 A. Inducer draft motor is using too much power 4. Blower wheel is covered in dust and debris Discussed full condition of system with homeowner and she understands where it is at the moment. Advised her that indoor blower motor is leaking oil along with the inducer draft overamping at the moment. At this point any repair done to the system itâ€™s just a band aid. Client understands and does not want to put money into a 16-year-old system rath
Arrived on site to perform diagnostic on 2004 Lennox system with new Condenser Coils. Homeowner states his thermostat just went blank and is not turning on. Heâ€™s checked for power at the thermostat and not recieving any power. Also went into attic and checked unit. Re-checked power at thermostat to confirm and there is no power present. Went up into attic and checked system electrical and components. Unit is receiving proper power. Found that unit has a safety switch installed that was tripped, and secondary drain pan was full of water. Primary drain line appears to be clogged and needs to be cleared. Went over findings and recommendations with homeowner. Homeowner is pretty handy and will be taking care of the repair himself. No other work performed aside from diagnostic. System not operational upon departure
Performed AC maintenance on a 2007 Air temp condenser. Cooling temperature split is 20 degrees. filter is very dirty. Condensate lines are clear. Condensate pump is in good working condition. Systems return is very small causing restriction. Duct runs have been replaced recently. Indoor blower is very dirty. Blower motor is slightly leaking oil. Battery for the blower is in range .Outdoor unit was deep cleaned. Fan motor is leaking oil. Battery cap is out of range on both terminals causing the fan motor seal to break. Compressor start and run amps were recorded. Refrigerant levels were off. System was running st end of appointment. Homeowner knows the condition of his equipment wants to hold off on repairs due to a long list of other home repairs.
Tested system operation and inspected for problems. Found evaporator coil very clogged, this is causing the system to ice up and fail to operate o warmer days, the filter is missing as well - this works to protect the evaporator coil. There is heavy amounts of water in the ducts under the floor, this needs to be drained and a sanitizing system should be installed to clean the vents as much as possible. Due to the age of the coil and the rust in the drain pan it is likely that the water is bypassing the pa and leaking straight into the ducts. Replacing the equipment is the most practical option at this point.
Arrived on site to diagnose a leaking unit in attic. Spoke to client and she stated she lived in home for a a couple years and was told unit is 2 years old. Inspected unit and found unit is from 2015 Goodman. She showed me drain line out side was draining but unit dose coil good. Inspected attic and unit and found drain lines was clogged up. Advised would need to cutt and clear line. Furnace and Evaporator has have no emergency drain pan. Drain lines have no safety overflow switches on either line and recommended adding one at least to primary line. Advised under sink can be clogged and she stated she doesnâ€™t have plumbing issues. Blew and vacuum line from top to bottom. Cleaned under sink as well and is clear. Client saw line were really backed up. Water tested and lines are cleared now and draining. Connected safety switches and reconnected lien and is good. Cycled unit is operant good. During connection time was connecting line and found copper line that goes under sink was corr
Found chewed wiring inside the lineset flashing. Spliced the wire to the pump and tested the unit with water to confirm pump is operational.
Upon arrival performed maintenance on 1 year old system. Took out clients standard filters, she was not aware that she had upgraded filtration with system. Showed home owner was filter looked like and explained how filter works and gets swapped. Outdoor coils were extremely dirty. Washed and and made sure system is now clean. Refrigerant levels are in very good standing. Amperages throughout system good. Circuit board and electrical connections good. Ducting is good. Thermostats in working order. Temp splits in range. System is operational upon departure.
Performed AC and heating maintenance on a Lennox condenser. Heating temperature split is a 36 degrees. Indoor amp draws are good. Filter was dirty and replaced today. UV bulb is glowing well. Ignitor and flame sensor were cleaned and verified in range. Duct runs are sealed. Cooling temperature split is 22 degrees. Condensate lines are clear. Safety switch was loose and repaired. Outdoor unit was extremely dirty but washed today. Refrigerant levels were verified ok. System was running at end of appointment.
Arrived on site to perform spring tune up on a 2019 lennox package unit. Client stated no issues. Cycled both heater and Ac. Unit is operational. Washed condenser coil inside and out. Checked all electrical compartment and compartment. Primary starter is good. Secondary motor control is good. Inducer motor is good. Fan motor is good as well and in range. Blower compartment is good and clean. Evaporator coil is good and clean. Drain lines is draining. System is cooling at 21 degrees and good on charge. Advised filter needs to be replaced and they do so every month. She stated she order more and will replace once they get here due to being a odd size. Cycled heater and was operational. Unit is heating home good. Advised no protection on unit and recommend if they get power outages. To protect from electrical surges and power outages that can damage or even short out systems and components. Cycled unit and went over all findings. Client is aware how unit is running and conditions. Client
Arrived on site to perform spring tune up on a 2020 carrier unit. Condenser located in back yard. Furnace in attic. Replaced filter as it was dirty. Advised keep doing so as needed every 2 months. Washed condenser coil inside and out. All components are good. Fan motor was good and in range. Checked start up and run amps. Both are good. Checked pressure and are good and cooling hole at 22 degrees. No protection on unit. Advised and recommended adding surge protectors to protect from electrical surges and power outages that can damage or even short out systems and components. Went over all findings and areas of concerns with unit. Advised maintenance is highly recommended even if unit is new. Wife was only home and went over all recommendations. She is aware of how unit is running. Client did want to go forward with renew of ESA. Client did renew monthly. Cycled system to ensure system operating. System is operational upon departure.