Sean is a good conscientious worker.
This is the source for tankless water heater service. The technician knows the product inside out and will tell you what he's doing every step of the way.
Finally knowledgable and professional service.
Sean did a nice job replacing my garbage disposal and re-working the faulty plumbing. He took time to show me what he was doing and how he was making the repairs. He was very efficient, polite, and completed the installation without having to go back to the shop for parts. Overall, a good experience and I would use them again.
Great service and had my water back in the same day.
Proceeded to cut open concrete and determine issue with kitchen sewer line, upon exposing the pipe noticed the pipe was deteriorating and had collapsed. Cleared enough for a snake to get in the line but went 30 feet and would go no further. I have determined that the kitchen line to the main is bad and needs to be replaced. Left two estimates with the customer to do partial repipe of sewer or get it all done. Customer will contact us when they decide what they want to do.
Found a small pinhole leak in the solder joint located at the tee for the hose bib. repaired the leak and tested for additional leaks. re-taped pipe and made sure water is back in the on position
Customer is going to get other estimate
Returned with smaller snake, tried to get the camera down the line but itâ€™s still full of water. Provided an open ended estimate in case work gets more extensive, emailed to Anita and waiting for approval.
Tenant has slow draining hall bathroom tub, and clogged kitchen sink with exterior cleanout. Upon snaking the kitchen line the snake would not go down, felt like a break in the pipe and there was dirt in the line. Snaked the hall bathroom and cleared a bunch of hair out of the line, filled the tub and drained with vortex. Schedule with dispatch in the morning to get Sean out here with a smaller camera or borrow it and camera myself.
Performed ac diagnostic, found system wasnâ€™t working again because of the moisture switch in pan. After I got the system up and running and tested, found pan dry... could be bad switch moved location. Ran system for good amount of time. Then performed furnace tune up. System fired right up. Ran system thru itâ€™s stages. System running ok at this time. Cleaned burners and flame sensor. Variable speed blower motor ok. Electrical looks good. Ducts in attic are silver flex sealed. Checked filter ok for now will most likely need to be replaced next visit. Heater working well at this time. Want to watch out for rodents. See if it gets worse.
Performed ac diagnostic Citrus Heights. on high efficiency carrier infinity system, found system tripped moisture meter again. Pan doesnâ€™t have water in it at this time. Tested system, the switch didnâ€™t reset as quick this time. Moved switch to different part of pan. Also noticed some evidence of rodents in attic.
Customer has one or three angle-stops he wants installed after he had a hard time installing the ones he already has done. The angle-stops were leaking but since have stopped and he is hoping they stay that way, we did no work and advised that he have a professional install then for fear of water damage. Customer will give the estimates to his brother to approve.
Thereâ€™s a leak in the original enclosure will have to replace unit to repair drain line issue will also install new moen single handle shower valve new pan 60+32 LH drain base in white back wall and end walls height of walls same will have to remove tiles to get old unit out unsure of condition of drain pipe additional Watkinsâ€™s may be needed to resolve house is on slab. Need to know if we are going forward with this job so shower can be ordered arrival unknown at this time installed new enclosure tested pan no leaks job completed ready for paint
Performed ac diagnostic, unit is original. Found unit leaking water and water was coming out of the left side... drain on the right side. Resloped unit, for better drainage and system appears to be better. Maintenance to go back out and reseal the unit tomorrow. Now that the unit isnâ€™t leaking as bad. Canâ€™t guarantee fixed. But better. If problem consists will need to retrofit unit. po50-307
Installed new 1 inch pressure regulator valve on main water line, rebuild main riser with new tea, hose bib, Ball valve with secondary ball valve for irrigation line insulated pipe,checked pressure and set for 60 PSI.
Performed ac diagnostic on unit found system low on refrigerant. Inspected system for refrigerant leaks, no oil stains or residue. Charged system with client supplied refrigerant. If problem consists will need to dye system with uv dye to try and find leak Po 50-307 Need to properly charge system. Checked system for big leaks everything looks ok. No oil stains or residue. Properly charged system see before and after photos.
Would remove old equipment and replace with customer supplied equipment.
Performed quality check and installed 1 20-25-1 filter inside unit. Sealed up insulation around coil unit. Unit making slight noise at high speed air conditioning. Noise got better with filter inside unit.
Found unit not working breakers off, turned on breakers and turned on dissconnects, tested for power had air handler turning on, on its own. And had heat pump outside not getting low voltage. Fixed outside units low voltage. Re wired unit and system came on when it was suppose to. Cleaned up around heat pump. Put everything back together. And tested refrigerant. Apt was at 75 cooled unit down to 71. Turned off portable unit. And shit sliding door.