Finally knowledgable and professional service.
Sean did a nice job replacing my garbage disposal and re-working the faulty plumbing. He took time to show me what he was doing and how he was making the repairs. He was very efficient, polite, and completed the installation without having to go back to the shop for parts. Overall, a good experience and I would use them again.
Great service and had my water back in the same day.
I was very happy with the quick response and the friendly, professional service technician. Tim had my AC up and running quickly on a very hot day! Would definitely recommend Crystal Blue Plumbing, Heating & Air!
Sacramento ca AC service diagnostic AC not working Perform diagnostic on AC system found no low voltage power at outdoor unit determined it was caused by thermostat. replaced thermostat tested unit operation found no other problems at this time.
Called don will get on sch when material arrives
Performed diagnostic. Found system working inside not working outside, newer r22 system. Has leak. So we dyed system with uv dye to try and find leak. Charged system back up with customer supplied r22. Pressures NOT holding for now. Went thru system inspecting for dye at connection points/brazes. And at coils inside and outside. Found two leaks outside at the Schroeder core on the suction side. And inside the coil found leak at bottom right side. Po 33584 Quoted for system replacement with customer supplied equipment, emailed quote over.
Performed ac diagnostic. System not operating at all. Tested system and found tstat not doing anything. Changed tstat with customer supplied one. And system turned on. Airflow appears weak, but system is on and cooling at this time. Tested ac system now that itâ€™s up and running, found unit low on charge. Po50-307
Provided estimate customer is gettin 3
Sent estimate to customer called no answer no approval. Will have to remove trap and reinstall pop up it appears that itâ€™s missing a anti friction ring which is not allowing you to tighten the pop up to the sink. Will try to make it work properly with existing parts. Thereâ€™s a broken nut on trap will need to be cut out and replaced. Tested no leaks
Install new 1/4 turn shut off valves for irrigation and house main, and install pressure regulator. Irrigation system has several leaks at rain heads. Checked water pressure to determine cause of issues. Found water pressure to be at 98 psi, pressure is too high and needs to be reduced. Need to install pressure reducing valve and two new 1/4 turn ball valves. Installed 1 3/4 inch ball valve, 1 1 inch ball valve and a 1 inch pressure reducing valve to fix leak as stated by inspector. Let male adaptor glue joint cure before testing for leaks, no leaks.
Performed ac diagnostic on split. 8 yr split carrier infinity system. Found clogged primary drain. With the type of unit you have I recommend annual maintenance to ensure drain line is clear yearly. We need to try and vacuum drain line out. If that doesnâ€™t work need to try and blast drain line out from above in attic. Once line is clear verify draining. Draining ok at this time.
Switching the breaker to the correct size for the unit it is 30 amp 20 amp should be 35 amp 20 amp. installed new breaker and tested system. Let system run to see if anything else is going on. All good at this time. In removing breaker found a hot spot on old breaker. That could have been the problem.
Performed diagnostic on our install of there equipment. Found outside unit frozen in places, see pictures. Thawed system. And then charged system. Numbers we a little all over the place. Could be from a few factors. Got low side above freezing and high side was very high. Numbers seemed to stabilize. Also drain appears to be working correctly. Unit cycled off on its own. Could not get into unit, no keys.
PO:50-307. Remove old equipment per EPA regulations and install 2 Ton self supplied heat pump.
Call and went over price increase. Patrice is now ok and ready to move forward tomorrow
#no Remove old equipment per EPA regulations and install 2 Ton self supplied heat pump. Need filter drier. They have disconnect and whip. We Will supply thermostat.
Performed ac diagnostic Citrus Heights, found ac not turning on. From badly burnt wire to contactor, that burnt up contactor. Replaced contactor and tested system. System running on departure.
Performed ac diagnostic, Unit has refrigerant not low at this time, and power both low volts and high volts. Compressor wonâ€™t kick on. When compressor tryâ€™s to kick on pulling amps not pumping refrigerant correctly. Megohmed compressor winding read bad. Need to replace outside unit or compressor, my recommendation would be to replace the unit. Due to age and cost of repairs. Po 50-307