Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Service call that the Wall AC Unit for the Kitchen was not Cooling. System was turned off upon arrival. Turned System to Cooling and Measured Air Temperatures across the Coil. Unit was not producing any cooling. The Compressor and Fan was operating. No error codes were present. Checked Air Filter and Coil to ensure no Blockage of the Air Flow was occurring. Removed unit from Wall to inspect. System does not have any Refrigerant Ports. The system has lost its Refrigerant Charge due to a leak in the system, and is unable to cool. Due to condition, recommend replacement. We will follow up with an estimate to replace the Unit with a higher Grade Unit.