Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Will do. I'm happy with your prompt reply and professional work. Once you submitted the pictures and diagnosis online as required, please let me know. I can follow up. Thx
Very good! Extremely satisfied with Luis. Thank you
He was amazing, polite and professional, the quality of service provided by Luis was exceptional. I will be using Dibiase hvac again because of Luis and Angie in the office who was also super to deal with. Thank you, Dave Rucker
will recommend DiBiase to other neighbors.
Chris was on time, very efficient and thougher
Chris was great. Friendly extremely knowledgeable
Very cordial, helpful, and most cooperative -Will return to replace frame for outside outlet
Luis was great, clean,meticulous and helpful. My system was shot but he did his best. Appreciative of the effort.
Remove humidifier from unit and panned area and sealed openings. Measured airflow from 2 upstairs bedrooms after humidifier removal. Front bedroom was measuring 76CFM and the rear bedroom was measuring 52CFM. Sealed all return air ducting in basement area that was accessible using mastic. Install new booster fan 10" on duct run feeding 2 bedrooms on right side of home. Tested fan in low and high speed and left on high speed. Measured CFM at front bedroom at 158 CFM and rear bedroom at 128 CFM.
Performed ac tune up check electrical low and high ok filter ok, check drain line ok flushed it with water, check temp split, blower cap and motor ok check outdoor unit refrigerant pressures ok capacitor and contactor ok cycle unit ok
Performed cooling maintenance, checked air filter ok. Cleaned condensate drain. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started air conditioner, checked refrigerant charge and temperature drop across coil.
Performed Quality Assurance inspection on a newly installed gas furnace. System running great at time of QA.
No ac found thermostat se to 72 room temp is at 82 check blower operation ok blower cap and motor ok, check outdoor unit found power to outdoor unit but nothing is working, found compressor tripped on high head, check coil and found condencer fan motor not working, found open run cap for both sides quoted for repairs once we installed new cap we will check refrigerant pressures to make sure levels are ok
Performed cooling maintenance, checked air filter. Blew out condensate trap and drain. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started air conditioner, checked refrigerant charge and temperature drop across coil
Performed ac tune up check electrical low and high ok replaced filter chck and flushed drain line ok, check temp split blower cap and motor ok outdoor unit refrigerant pressures ok capacitor and contactor ok cycle unit ok
Checked no cooling complaint, blower runs but no outdoor, checked run capacitor, found weak run capacitor. Replaced run capacitor. Started air conditioner, checked refrigerant charge and temperature drop across coil.
Service call that the Heat Pump water heater was not working properly. Found system operating on arrival. Viewed Fault Code history and found the Clogged Condensation Drain error. Removed drain pipe and cleaned. Inspected the internal drain connection. Drain was clean and clear of any debris. Called Technical Support about error code. Technical support stated that the internal sensor could get tripped due to condensation or moisture in the Air. Unit is operating to standards.
Performed cooling maintenance, checked air filter. Blew out condensate drain. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started air conditioner, checked refrigerant charge and temperature drop across coil.
Returned to site to connect Honeywell T10 Thermostatto Wifi. Attempted Wifi connection multiple times. Called Honeywell Technical Support and cycled Powered to the Main Router in the basement to change IP Address on the thermostat which then connected to the Wifi. Walked through setting the App up on the phone. On arrival, system was set to cool but outdoor unit was out on the E04 Error Code again. Checked Line Voltage at 239 VAC. Cycled power to System and restarted. Showed homeowner how to turn power off to system if issue occurs again. If a continued problem we will need to install a power monitor to verify if there is an incoming power voltage issue.
No ac found tripped on wet switch, noticed some water inside auxiliary pan, reset wet switch and check drain line, flushed drain line with 1 gallon of water and is draining ok, pour water on primary pan and is also draining ok, check refrigerant charge 410 hgh side and low side ok supply air 60 return air 80 system is working ok, Insulated ez trap noticed some sign of water dripping from trap, insulated trap with line set insulation and heat tape cycle unit ok no charge for todayâ€™s visit
Performed cooling maintenance, checked air filter, found clean filter. Blew out condensate trap. Checked voltage, amperage and electrical connections, measured capacitor values, found failed dual run capacitor on outdoor unit. Replaced capacitor. Started air conditioner, checked refrigerant charge and temperature drop across coil.
Reclaimed and removed old equipment. Installed new leveled pad, disconnect, whip, line set with low volt wire, and Amana condenser. Brazed in with nitrogen and connected low and high voltage wiring. Installed new Amana evaporator coil and brazed in with nitrogen. Pressure tested to 300 and evacuated down to 147 microns. Installed new ez trap and pump and ran vinyl to discharge. Wired in low volt and safetyâ€™s to break r circuit. Released refrigerant and tested system in cool. Adjusted charge. Tested pump. System working well at time of install.
Performed gas hat check up and AC tune up, check electrical low and high ok replaced air filter check drain ok, cleaned flame sensor and inspect burners, check blower motor and wheel ok, noticed cap reading 36 rated at 40 check ,amigos gas pressure combustion test on furnace ok, check outdoor unit refrigerant pressures r22 ok contactor ok capacitor has major rust reading just under 6 % tolerance cycle unit ok Furnace and ac are working ok at this time