Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
I made a call on Saturday morning for a water leak and I was very happy to see Bryan at my home 2 hours later. Great service, very professional and take time to explain the problem and provide solution. Thanks so much!
Barry is an excellent, knowlegeable technician who is happy to explain the steps in the tune-up process. Highly recommended.
Everyone I’ve met so far is polite, professional and personable.
Tech was professional & thorough in checking out water softener & explained everything!
Efficient and friendly
Hybrid system, furnace side only work on low stage Amana two stage furnace with heat pump, system is from 2011 and it is communicated, found furnace only running on low stage second stage would not come on, error code E9, check vacuum on inducer pulling -.89 switch is rated at -.70 wc. Check venting pressure hoses drain ok, after couple resets inducer was pulling -1.35 wc. And it worked for minutes tried to reset to see if it would come back normal and it sit not error code E9 was present, power is Applied on high stage black wire and pulling .7 amps, would recommended replacement of inducer, informed customer about situation could also have a intermittent problem with board every once in while. Customer is aware. Home comfort consultant to come tomorrow for proposal on hybrid system and also on regular heat pump with air handler
Performed six month quality, replaced air filter. Updated cool cloud. Started gas furnace, tested limit and safety switches. Cycled air conditioner. Checked operation and temperature rise.
Replaced water sensor for rheem heat pump water heater, after new sensor was installed check operation water heater ran fine, water heater heat pump is working under normal operation. No charge
Performed heating maintenance, replaced air filter. Cleaned burners and flame sensor, inspected heat exchanger. Checked voltage, amperage and electrical connections. Started gas furnace, tested limit and safety switches, measured fuel pressures. Performed combustion test and checked temperature rise
Heat Tune Up Trane Natural gas furnace 80% Checked filter. Checked gas pressure. Cleaned flame sensor. Checked HSI ohms and checked for cracks. Measured temp split. Verified thermostat operation. Combustion test: passed. Checked all electric motors and components. System as it is struggles to heat basement in winter. 3 supply grilles in basement were shut. I opened them for heating season. Dimensions of room are 35â€™x24â€™x10.5â€™. MiniSplit to supplement is an idea. Provided estimate to level outdoor unit using river rock stone. Completed Gas Furnace Inspection Form Furnace is operating well at the time of this maintenance.
Customer not home payment not collected! Installed a new spirit oil furnace in existing location modified a piece of metal between duct and furnace. Installed a new oil filter and modified copper line as needed. Installed new 5â€ flue piping with a new draft control damper. Tested unit in heating and cooling and unit is working as it should.
Performed two gas furnaces tuneup/cleaning, check electrical low and high voltage connections, check blower ecm motor speed ok, cleaned flame sensor and check manifold gas pressure low and high stage ok performed combustion test check supply and rerun air temp ok cycle both furnaces both systems are working ok, customer takes care of filters and also humidifiers.
Performed Quality Assurance on Amana Gas Furnace/AC System. Reviewed installation with homeowner. Completed Checklist Form in system. Performed Combustion Testing and Gas Pressure tests on system. Tested Wet Switch Safety Device. This did not pass the QA, see notes below: Indoor Unit has some issues: The Auxiliary Drain Pan was not replaced during the install. This was part of the Job and a new Pan was with the equipment. The old pan is rusted and not in good shape. No Combustion readings on Install Report. Checked Combustion and Gas Pressures. No Combustion Testing was done on the Install. Gas Pressures were set to 4â€ WC when I started the heat up. Performed Combustion Test and measured Gas Pressures.
Found that beacause of how tight the room is where the water heater And the furnace were located filter was hard to remove out the front of the filter rack. Explained to the homeowner that the only real option we have it to take metal snips and remove the top of the filter rack to be able to remove filter out the top of the filter rack. Modified filter rack and showed homeowner how to remove and re- install the 16x25x1 air filter.
Performed heating maintenance, checked air filter ok. Blew out condensate trap and drain. Cleaned burners and flame sensor inspected heat exchanger. Checked voltage, amperage and electrical connections, measured capacitor values. Started gas furnace, tested limit and safety switches, measured fuel pressures and performed combustion test. Checked operation and temperature rise.
Heat Tune Up for 80K BTU natural gas furnace. Replaced filter. Cleaned flame sensor. Checked hot surface ignitor ohms and watched for hotspots during start up. Checked burners and heat exchanger. Measured gas pressure. Measured temperature rise. Checked thermostat operation and all wiring. Opened bypass duct on humidifier, checked pad and tested operation. Combustion test: passed. Checked all electric motors and components. 10 uF blower capacitor reading 9.21 uF. Strongly recommend replacement. ST-5 Expansion tank for hot water heater is internally compromised. Water heater Relief valve is opening from time to time. Strongly recommend replacing expansion tank. Furnace is operating well at the time of this maintenance but the weak capacitor could fail causing a no heat/ no cooling situation. Relief valve of hot water heater will continue to open periodically if expansion tank is not replaced I attempted to call Jay to discuss recommended work but He did not respond. Left emailed
Performed precision gas furnace tune up amana gas furnace. Replaced Aprilaire 413 air filter. Serviced Aprilaire humidifier with #35 humidifier pad. Checked all electrical conections and components. Blew out pressure switch tubing. Cleaned flame sensor. Tested operation of humidifier. Checked temperature rise, and performed combustion test. Gas furnace is working fine at time of service.
Performed heat pump check up, check and test back up heat 20 amps each element, check temp rise, cleaned filter, service humidifier test and replaced pad, set humidifier to winter 35%. Check outdoor unit refrigerant pressures capacitor and contactor ok cycle heat pump ok. Provided an estimate for whole house air purifier
Heat Tune Up 110 BTU Natural Gas Furnace; Communicating; Modulating. Replaced filter. Opened humidifier damper and checked pad. Checked burner and heat exchanger. Cleaned flame sensor. Checked hot surface ignitor ohms and checked for hot spots during start up. Checked all electric motors and components. Checked pressure switches and hoses. Checked wiring. (Communicating) Made call from heat from first floor stat. Checked temp rise. Checked static pressure. Combustion test: passed. Completed Gas Furnace Inspection Form Furnace is operating well at the time of this maintenance.
Performed heating maintenance, checked air filter ok. Blew out condensate trap and drain. Cleaned burners and flame sensor, inspected heat exchanger. Checked voltage, amperage and electrical connections. Started gas furnace, tested limit and safety switches, measured fuel pressures. Performed combustion test and checked temperature rise.