Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
The DiBiase Team is very responsive, and continually provides excellent - professional services. I would continue to highly recommend their services to others, as I have done. Tony - Realtor/Residential property owner (multiple properties)
We recently had the benefit of services provided by Kurt on two recent occasions: one for a 'diagnosis', and another for an install/repair need. The repairs were performed under very difficult weather circumstances. The services provided were timely, comprehensive, fair in price, and with utmost respect and courtesy to us. Valuable education was also provided too. Thank you Team DiBiase!
Joe DiBiase and his team have been servicing my system since I moved here in 2007. Their responsiveness, quality of work and professionalism has always been first-rate. A survey question asks how I rate their cost/pricing ... with the quality and level of service they provide, I've never seen a reason to check pricing.
Just had our oil fed furnace stop working due to previous owners neglect. I called DiBiase on a recommendation and they sent someone to assess and fix the problem just a couple hours later. Luis, the tech, was thorough and didn't stop until the problem was fixed. He explained what was happening, why it was happening and had all the parts he needed on hand to finish the job. I was impressed with everything about this company and signed up for their yearly maintenance program as a result.
I woke up to no heat and Dibiase was out within 2 hours to restore my service! I could not be any happier!
Peco shut off heater, flames did not seem ok, upon arrival found heater off, test and run heater, noticed some change on co. Performed heat exchanger test, run hester with blower on and with blower off, high changes on oxygen, carbon monoxide, and excess air, heat exnchager failed test, unit should remain off until necessary repairs are done. Unit is 19 years old, would recommend replacing system, at this time unit remains off as peco left it, also noticed water from water heater it is slowly leaking from bottom
Performed precision a/c tune ups on 8 systems. Found Air handler in gym area with a weak capacitor, replaced 12.5 mf cap and tested all a/c"s. All systems working fine at this time (5) 20x20x1 air filters, (6) 20x20x2, (6) 16x20x2.
Performed Quality Assurance Inspection on newly installed Heat Pump and Air Handler.
Installed new Furnace coil and out door new pump new vinyl and new copper line for humidifier pumped down to 230 microns ac was not able to be tested nest thermostat would not allow it to kick on under 60 degrees outside temp. Pump tested drain and humidifier tested as well
When I arrived pulled off chimney cap at furnace exhaust and found it to be clear. Then pulled off coil door and did a visual inspection of the heat exchanger and found no cracks. Also pulled apart vent pipe at furnace and it was pretty clean. Did a combustion test and furnace is running fine at time of service. Talk to homeowner about replacing 20 year old detectors the might be faulty them selves. Do not see a safety issue with furnace that would be causing an issue at this time.
Estimate to move the Air Conditioner from the side of the house to around the corner to the back side of the house. Please see attached estimate for the detailed work to relocate the Unit.
6 month inspection, check electrical low and high burners gas pressures ok, combustion test ok, 413 ok test Humidifier ok cycle heater ok check split ok noticed air scrubber light not on, air scrubber is malfunctioning burning out transformer, tried new transformer but keeps burning them, need to order new air scrubber under warranty installed new air scrubber under warranty wire a 40 va transformer to air scrubber, cycle heater, air scrubber light is on
When I arrived homeowner had mentioned that the aux heat is not working. Tested aux heat at indoor air handler and strip heat was drawling 20.7 amps and duct was at 85 degrees discharge temp with aux heat running by itself. Replaced contactor only at outdoor heat pump , homeowner does not like Titian brand. Then performed precision heat tune on Goodman heat pump. Checked all electrical conections and tested all components and checked refrigerant pressures. Also washed out washable filter.
Performed ac check up, check electrical low and high ok replce filter, flushed drain, draining slower, informed customer, also no wet switch in installed, to prevent water damaged in case drain blocks, indoor coil needs deep cleaning as soon as posssible, we will try to removed coil without disconnecting pipes, if we have to disconnect pipes we need to add for pumpdown and vacuum, also blower wheel needs deep cleaning, recommend installing ez trap and wet switch as the unit gets older average life is between 12 to 15 years, Removed blower compartment and clean blower wheel. Also clean indoor coil very dirty, would try with out disconnecting coil if we canâ€™t clean it correctly without disconnecting coil extra work will applied to bill, pumpdown and pull vacuum, made all necessary repairs to clean coil and blower wheel, pressure test at 250 psig, ok evacuation re check r 22 test ok, flushed drain ok check ac and heat mode ok,
Performed 6 month inspection ac side, check electrical low and high ok replace filter, 16x25x1 flushed drain ok check outdoor unit 410 all electrical outside ok cap and contactor ok
Performed quality assurance inspection of new system installation. All looks good.
Performed ac check up, check electrical low and high voltage ok replce filter, flushed drain ok add tabs, check outdoor unit 410 pressures ok contactor and capacitor ok, cycle heat pump ok installed ecm motor protector indoor and on outdoor unit,
Performed ac check up, check electrical low and high ok replce filter 16x25x1 flushed drain ok, noticed has no ez trap and wet switch, recommended installing both safetyâ€™s, check outdoor unit, r22 seems to be ok, contactor is pitted, burnt contacts, and capacitor is reading 45x2.9 rated at 50x3 quoted fore repairs, Replace capacitor and contactor and also installed wet switch
Water in the pan every time they use the ac, run ac unit for more than one hour did not see any water/condensation coming from unit, outdoor temp is 49 and indoor temp is 68, recheck drain, hoses ok, still canâ€™t find out where water is coming from, we need to return, outdoor temp has to be at least 70 outside for to check ac unit correctly, with current temps it is very hard to check system there is not much load in the house,
Performed 6 month inspection on amana gas furnace and a/c system. Checked electrical conections inside gas furnace , and outdoor a/c system . Ran furnace in heating mode checked air filter and tested gas furnace operation. System is performing well at this time. Checked delta t of gas furnace in heating mode and it was return 72 degrees and supply 117 degrees , 45 degree delta t very good. Also performed combustion test. Then cycled on a/c all working fine at this time.