Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
If you're in the West Chester, Chester County PA area and need HVAC work done - I can't recommend DiBiase highly enough! They were, and are, expertly skilled at what they do, extraordinary communicators before/during/after the install, and a pleasure to work with. The team were all complete professionals. I have high expectations but they exceeded all of them!
Knowledgeable and polite as always. All questions thoroughly answered. Excellent service provider that we will stick with.
Kurt was very informtive on everything did not delay in his job a perfect gentleman
Barry fixed the thermostat and carefully explained what had gone wrong with the outdoor temperature sensor.
Our Spring service was today with Brian and it was another great experience with DiBiase Heating and Cooling. I really appreciate Brian showing up just as scheduled, explaining the service, and being respectful of our home. We are now set for the summer!
Kurt was professional and thorough.
Kurt did a great job servicing the HVAC unit. No issues. ALl done very well.
Another great experience
Really know how to fix things.
Removed old evaporator coil and condenser. Alone with lineset condensate pump vinyl tubing and pvc. Install new 4 ton heat pump with evap coil with new lineset 8wire Vinyl tubing condensation pump, ez trap, made Tranzitions in between oil furnace and coil. Taped and seal all holes. Installed new high temperature evaporator pan in new coil. Tested out all stages of heating and cooling
Found system running thermostat was set to 75 degrees and was at 83 degrees inside temperature. Homeowner showed me were he was getting water at and had already dried up water prior to my arrival. Went over System and found system was low on charge. Only the air handler was replaced ( not the heatpump or lineset). Recommend to homeowner to add refrigerant and leak dye to get the system working for now. Then return and try to locate leak dye in about 30 days. Or replace the outdoor heat pump to match the indoor and replace the lineset. Homeowner want to check for the leak dye fist before making a desicion.
Performed routine ac tune up, upon a arrival found outdoor unit not running, error code showing #3 pressures switch issue, checked indoor coil, checked indoor panel, checked and cleaned EZ trap, checked temp split, checked outdoor unit, capacitor check, checked outdoor coil, checked refrigerant pressures and voltages outside ok, filter was super dirty that was the issue on why the outdoor unit was not running, would recommend replacing filter monthly.
Installed new daikin mini split in basement and attic bedroom. Installed new lineset and linehide for each unit. Installed new outdoor unit on bracket. Installed new 20 amp breaker and wire for unit. Installed new drain line and communication wire for units. Made all refrigerant connections and pressure tested to 475 psi and evacuated below 500 microns. Made all necessary high and low voltage connections for each unit. Tested system in heating and cooling, system working properly.
Arrived to do ac maintenance, Checked thermostat for operation, checked filter, primed and cleaned EZ trap, checked blower motor amp draw, tightened all electrical connections, checked temperature split. Went outside and checked compressor amp draw, condenser fan motor amp draw, checked dual capacitor and refrigerant pressures. System is working correctly at this time.
Performed cooling maintenance on main system an six month quality checks on the 2 new air conditioners. Cleaned condensate drain. Checked air filters ok. Checked voltage, amperage and electrical connections, measured capacitor values. Checked new unit setup. Started air conditioners, topped off charge on new air conditioners. Balanced by sub cooling. Checked operation and temperature drop across coil.
Ductless system leaking water, check indoor head removed cover and inspect drain, noticed drain line not pitch correctly adjust drain, pour water on drain pan, water flowing correctly, explained to customer is issues continues to happen, we need to removed head and check behind ductless. We would quote as needed.
Plan member AC maintenance for 3 Ton System: Replaced 20x20x1 Filter Measured temperature split and static pressure. Checked wiring, controls, electric motors and components. Both indoor and outdoor coils are in good condition. Checked refrigerant pressures and diagnostics. Water softness/hardness test Results: 20 gpg CaCO3>> Very Hard. Provided (2) Estimates. 1 for NOVO Water Softener 1 For Water Softener and Filtration System. Air conditioner is operating well at the time of this maintenance.
Performed precision a/c tune up on trane a/c system. Replaced Aprilaire 201 air filter. Checked all electrical conections and components. Cleaned out ez trap. Checked temperature split. Checked refrigerant pressures and temperatures at indoor and outdoor units. Heat pump system is working fine at time of service.
No ac, found system off upon arrival asked customer to turn the ac on, noticed compressor does not start. Check capacitor Reding very low, tried installing new capacitor still did not came on, tried hard start assist and compressor started, customer does not want to spend any money in this current system, would prefer system replacement option, home comfort consultant to come out on Monday between 1 and 3 pm
Six month Inspection for 3 Ton AC and 100KBTU propane furnace. Completed maintenance for both AC and Heat. Aprilaire 413 filter ok at this time. Cleared EZ trap, checked drain and tested condensate pump. Turned powered humidifier humidistat to OFF Temperature deltas in both heating and cooling: Good Wiring, controls, electric motors and components: Good Combustion test:Good Refrigerant pressures and diagnostics good. System is operating well at the time of six month inspection.
Pumped down heatpump. Recovered refrigerant left in lineset and evaporator. Removed old amana evaporator. Installed new Bosch evaporator. Reconnected lineset and condensate drain. Reconnected and sealed supply plenums. Pressure tested system with nitrogen. Pulled vacuum on system. Tested operation of system in cooling. System running upon completion.
Arrived to do two ac maintenanceâ€™s one in the attic for an ac only and a heat pump in basement. Attic system: Checked thermostat for operation, checked and changed filter, primed and cleaned EZ trap, checked blower motor amp draw, tightened all electrical connections, checked temperature split. Went outside and checked compressor amp draw, condenser fan motor amp draw, checked dual capacitor and refrigerant pressures. System is working correctly at this time. Basement system: Checked thermostat for operation, checked and changed filter, primed and cleaned EZ trap, checked blower motor amp draw, tightened all electrical connections, checked temperature split. Went outside and checked compressor amp draw, condenser fan motor amp draw, checked dual capacitor and refrigerant pressures. System is working correctly at this time.
Performed cooling maintenance, replaced air filter. Cleaned eztrap and drain. Updated cool cloud software. Checked voltage, amperage and electrical connections, measured capacitor values. Started air conditioner, checked refrigerant charge. Checked operation and temperature drop across coil.
Noise from system, found blower making some noise, found tree leaf inside wheel making noise, removed leaf and noise went away, check supply and return air ok, would recommend system replacement, we just replaced furnace, would highly recommend replacing ac unit before it goes, please reach out to customer regards new ac system, tony should have all the info needed.