Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
On time, did what they committed to, professional job, left job site clean
Excellent service and knowledgeable people!
Prompt polite Found a gas leak and repaired same for which I was grateful
Very efficient, on time , and thorough.
Very good service by the technician.
Christopher Boas is an asset to your company courteous and very knowledgeable thank you for sending him
Performed Quality Assurance inspection on a newly installed gas furnace and air conditioning system as well as a new hot water heater. Checked over entire systems. All wiring proper and secure. Proper pitch on venting. All penetrations duct connections sealed. No trash found. Outdoor unit and disconnect level. No gas leaks and no water leaks at water heater. System looks great. Working great at time of QA Inside temp split - 112/68
Performed Quality Assurance inspection on a newly installed gas furnace and air conditioning system. Checked over entire system. All penetrations sealed and wiring proper and secured. No gas leaks and no condensate leaks. Outdoor unit and disconnect level. Made slight correction in humidifier wiring and now humidifier working properly. System working great at time of QA
Performed precision Heating Tune Up on Rheem Oil Furnace. Air Filter had recently been changed and was in good condition. Replaced Oil Filter, Oil Nozzle, and pump strainer. Found electrodes were very worn. Replaced Electrodes and set positioning. Cleaned Heat Exchanger and flue piping. Visually inspected Heat Exchanger. Inspected chimney base to ensure it was clear. Tested Transformer on Oil Burner. Put system in operation and performed a combustion Analysis, draft test, and smoke test. Measured Air Temperature Rise on system. Set Humidistat control to setting 3 as per homeowner. Oil Furnace is about 31 Years old and the AC system is about 9 Years old. Due to the age of the Oil Furnace, planning for replacement of the Furnace is recommended.
Installed a new amana gas heater on existing return box. Installed amana coil on top of heater and adapted all duct work as needed. Relocate humidifier and ran a new drain and water line to hum. Ran new copper lines from indoor coil to new amana ac unit. Brazed and leak checked with nitro and soapy bubbles. Ran new vinyl tubing over to discharge. Installed a ez trap and pump and wired it into unit. Installed a new Bradford white hot water heater. Adapted piping as need put hwh on bricks and ina drain pan. Installed ac on pump up feet and on a new plastic pad. New disconnect box and electrical wiring to unit. Tested unit in all modes and unit is running great.
Performed gas heat check up check electrical low and high ok cleaned flame sensor check gas pressures low and high ok replaced air filter, performed combustion test cycle furnace ok both zones are working ok
Performed gas heat tune up on propane furnace, check electrical low and high ok cleaned flame sensor, replace filter, check burners ok performed combustion test cycle furnace ok check temp split ok
Day1 installed a new Bradford whit shot water heater in existing location. Install hwh in a drain pan and on bricks. Connected piping as needed and installed a new expansion tank. Tested hwh and set thermostat to 120. Day2 installed a new amana gas heater in existing location with a amana coil on top. Converted furnace to propane. Ran new copper lines from indoor coil to new amana ac unit, brazed and leak checked with nitro and soapy bubbles. Ac is on a new plastic pad and has a new electrical box and electrical wiring. Ran heater and ac condensate to sump pump and installed a new ez trap and wired it into the heater. Adapted all ,teal as needed and installed a HE filter under heater. Taped and sealed all duct. Modified flue piping as needed. Tested unit in heating mode. And made sure ac fired on .
Performed gas heat tune up check electrical low and high ok cleaned sensor and burners, check gas pressure low and high replaced air filter, performed combustion test ok, insulated furnace drain and also ez trap, cycle furnace ok
Performed propane gas furnace, attic unit check electrical low and high check filter, cleaned sensor and check burners, gas pressures low and high ok performed combustion test test and cycle safeties system is working with in manufacture specifications
Performed heating maintenance on heat pump, replaced air filter. Checked v, amperage and electrical connections. Tested electric back up heaters. Started heat pump, found only outdoor fan running. Checked run capacitor ok. Checked contactor ok, checked compressor. Found open winding on common and run. Compressor has failed. Recommend replacing heat pump, 25 year old air handler and a 7 year old 13 seer 410A heat pump.
Checked no heat complaint the outdoor unit breaker tripped. Checked air filter ok. Started heat pump, checked temperature rise, only getting 6 degree rise. Checked refrigerant charge, found a restriction somewhere. Found restricted line set. The refrigerant lines are pinched at the unit where it looks like the unit was pushed back and pinched the lines. Will need to pull unit away from the house and repair the damaged line set. 11/13/20. Found inside unit that power wire was bear and shorted to small true suction line and there was an electrical burn mark which made a hole in copper pipe. Repaired rubbed wire a soldier hole shut on true suction line. Cut out kinked lineset from homeowner hitting unit with mower. Installed new section of copper line set and pressure tested at 200 psi nitrogen. Vacuumed down system to 500 microns. Checked temperature split in a/c mode it was exactly 20 degrees. Added 16lbs 30zs of refrigerant to system. Recommended to homeowner to have an a/c tune up do
Performed precision heat tune up on nordyne heat pump. Aprilaire 501 air filter and Aprilaire #35 humidifier pad are clean. Blew out condensate drain. Checked operation of emergency heat. Checked temperature rise in heat pump mode. Checked all electrical conections and components. Checked refrigerant pressures and temperatures at indoor and outdoor units. Heat pump system is working fine at time of inspection.
Found hot surface igniter broken. Replaced with igniter Han on the truck and performed precision heat tune up. 16x25x1 air filter is clean. Checked all electrical conections and components. Checked temperature rise. Blew out condensate drain and tested condensation pump. Cleaned flame sensor. Checked gas pressure and performed combustion test. Gas furnace is working fine at time of service.
Cut out and replaced flue piping for heater. Caulked and sealed all penetrations into the house. Capped old flue piping going threw the wall.
Performed propane gas furnace, check electrical low and high voltage, clean sensor, impact burners, noticed there was some delay on flame carry over, removed burners and clean burners, two of the burners the carry over was very corroded, would recommend replacing burners, check low and high stage manifold propane pressures ok replaced high efficiency filter, and service humidifier, test humidifier set to 35%, cycle furnace 5 times and all burners came on with no delay, performed combustion test cycle furnace ok