Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Luis was prompt and thorough in his work. He gave me a verbal report upon his completion.
Very efficient and pleasant representative of DiBiase we have used them since we moved into our home in 2005 always very professional
Very helpful re problem thank you
On time and efficient.
Everything explained easily
We’ve always been very satisfied with the service work DiBiase workers have done for us.
Performed propane gas furnace check up/inspection check electrical low and high ok also replaced air filter 16x25x1, cleaned flame sensor and check burners ok low and high stage ok performed combustion test cycle check supply and return temps ok, cycle furnace. Provide an estimate to install whole house air purifier
Maintenance Plan 2021-2022 Performed propane gas furnace check up/inspection check electrical low and high ok replaced humidifier pad with service, also replaced air cleaner 413 cleaned flame sensor and check burners ok low and high stage ok performed combustion test check airflow temp rise ok, cycle furnace, presented indoor air quality air purifier to customer, something they will consider in the future.
Performed Quality Assurance Inspection on Amana Gas Furnace/AC System. Reviewed installation with homeowner. Completed Checklist Form in System. This Install did not pass the QA Inspection. **Need to schedule a Follow Up Visit to fix the Exhaust Vent Pipe. Will need 3â€ PCV Fittings, 5â€™ of 3â€ PVC, 3â€ - 2â€ PVC Reducer, and 5â€™ of 2â€ PVC. This is a one technician job for a normal 2 Hour time window. All PVC parts we have in stock at the shop. System is working right now, but this could cause heating issues.**
Reclaimed and removed old ac and coil. Removed furnace and installed a new amana gas furnace that is converted to propane. Installed a new amana coil on top of furnace and installed a txv. Flushed copper lines and brazed and leak checked with nitro and bubbbles. Used existing supply metal and taped all joints modified flue piping as needed. Modified drain piping as needed and insulatated it. Installed an ez trap and wired it into unit. Installed a wet switch and checked for condensate leaks before wrapping up. Installed a new amana ac unit in a new plastic pad with crushed stone underneath. New disconnect box and electrical wiring to unit. Tested unit in both heating and cooling. Collected check for remaining balance.
Heat Tune Up for 100K BTU 2 stage propane furnace. Checked filter. Cleaned flame sensor. Checked hot surface ignitor ohms. Measured inlet and out let gas pressures. Verified thermostat operation. Inspected vents. Checked all left and components. Performed combustion test. Completed Gas Furance Inspection Form. Provided estimate for REME Whle Home Air Purifier. Replaced 35 Humidifier pan and cleaned housing. Left bypass damper open. Set humidistat to 35%. Furnace is operating safely at design conditions at the time of this maintenance.
Performed propane gas heater miller type furnace, check ignition filter, low and high electrical ok check supply And return air temp ok check gas pressure....performed room co test, reading 0 ppm cycle canâ€™t performed combustion test on furnace.
Found flame sensor pitted, replaced flame sensor. Also performed precision heat tune up on American standard gas furnace. Replaced 16x25x1 air filter. Checked all electrical conections and components. Blew out condensate drain. Checked temperature rise. Tested blower capacitor. Furnace is getting older and will need replaced in the near future but is working ok at the time of service.
**THIS JOB WAS NEVER COMPLETED***. Had to be completed due to the refunded money to the customer. Due to the wrong readings given to the customer, the repair was no longer needed. Disconnect and remove existing LP Pressure Regulator at the Wall Entry. Pipe in a new Regulator and leak test fittings. Put Furnace into operation and measure inlet Gas Pressures. Adjust Regulator as needed to ensure correct pressure. Perform Combustion Test of Furnace up completion.
Found incoming lp gas pressure at 12.3 w.c. With no draw on the tank. Gave gas furnace a call for heat and found on the manifold side only 2 w.c. With 11 incoming to the gas valve. Adjusted the low fire to 6 w.c. And high fire was at 10 w.c. Performed a combustion test. Regulators are functioning properly at time of service, gas valve just needed adjusted.
Performed precision heat tune up on amana high efficiency propane gas furnace. Replaced Aprilaire 413 air filter. Checked all electrical conections and components. Cleaned flame sensor. Blew out condensate drain. Checked gas pressure. Performed combustion test. Tested humidifier, pad is clean. Checked temperature rise. Gas furnace is working fine at time of service, no recommendations at this time.
Performed gas heat tune under service plan, check electrical low and high voltage connections ok replaced filter, cleaned flame sensor and check burners check gas pressure performed combustion test check blower motor and capacitor cycle furnace ok. Set up consultation visit for system system replacement option this upcoming Friday at 11 am
Six month Inspection for 60K BTU 2 stage propane furnace/ 3 Ton AC. Checked burners and heat exchanger. Replaced filter. Checked humidifier operation; left humidifier damper open. Checked gas pressure. Performed combustion test. Checked temp rise. Checked all electric motors and components. Completed Gas Furnace Inspection Form Checked AC temperature split. Checked refrigerant pressures. Checked outdoor capacitor. Checked voltage at outdoor equipment. Checked compressor amps during cooling cycle. Both the AC system and furnace are operating safely at design performance at the time of six month inspection.
Found inlet Gas Pressure of 2 stage 120K BTU propane furnace to be 3.00 In. W.C. Checked tank capacity. Gauge reads 75%. Cleaned flame sensor. Filter ok. Electric motors and components ok. Temp rise is low. Combustion test proves that system is running low on propane pressure. (3.96% CO2) Regulator has failed. Called Mrs. Saladinoâ€™s propane service provider with Mrs. Saladino. As of yesterday they no longer service regulators as a company. Recorded info of regulator to provide estimate for replacement. Urgent. Provide quote for replacement of regulator. Furnace will operate safely but with severely reduced efficiency until regulator is replaced.
Maintenance Plan Renewal 2021-2022 performed gas heat tune up check electrical low and high voltage connections replaced filter cleaned flame sensor and check burners check low and high stage performed combustion test ok cycle furnace ok.
Performed propane gas heater tune up check electrical low and high voltage connections ok cleaned flame sensor check burners replaced filter performed combustion test cycle furnace ok