Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Very efficient with times and service
Luis was very polite and efficient, took his time and checked everything, I have always had good service from your company
Very courteous. Great explanations
Luis did a good job noticing a problem and applying a quick fix. I know that companies need to make a profit, but 6 times the cost of parts (found on the Internet) is extremely high, especially since the replacement/fix took about 30 minutes.
On time and work completed as required. Service Tech was very professional and answered all the questions I had.
Performed precision heat tune up on American standard gas furnace. Replaced Aprilaire 401 air filter. Checked all electrical conections and components. Checked gas pressure and performed combustion test. Blew out condensate drain, and cleaned flame sensor. American standard gas furnace is working fine at time of service. Also gave homeowner a quote on a replacement water heater. Recommend to start thinking about replacement do to age.
Found humidifier pad in need of replacement, replaced #35 pad and tested operation. Also performed precision heat tune up on American standard gas furnace. Replaced 16x25x1 air filter. Checked all electrical conections and components. Blew out condensate drain. Cleaned flame sensor. System is working fine at time of service.
Found water on floor from water heater relief valve, check water heater no signs of other leaks, check water pressure and is at 45 psi, quoted for new relief valve customer ok with price, installed new relief valve and check for leaks no leaks, also bleed air from hot side faucets, would recommend installing flood stop to prevent this kind of damage, emailed proposal customer will call office when ready
Performed gas heat propane heater check up, check electrical low and high ok gas pressure ok combustion test split ok cycle furnace ok clean sensor and burners blower cap ok
Performed propane gas heat tune up, check electrical low and high ok gas pressure ok combustion test ok recommend replacing inducer transition and flame sensor quoted for repairs customer ok repairs installed both parts and cycle heater combustion test ok
Performed propane gas heater check electrical low and high clean sensor and check gas pressures low and high ok combustion test cycle heater ok check split, also service humidifier replace humidifier pad,
Performed propane heater tune up, check electrical low and high ok check manifold gas pressure set to 9.5 wc, clean flame sensor, cycle heater ok performed combustion test ok also check blower cap, ok clean burners ok cycle heater ok customer will take care of humidifier currently does not have a pad,
Performed propane heater tune up, check electrical low and high ok check blower cap ok when checking flame sensor, found rod in bad shape quoted for new flame sensor and also to service humidifier customer ok with pricing, installed new flame sensor and new humidifier pad test and cycle humidifier ok, check gas pressure and performed a combustion test on heater ok cycle heater ok
Found pitted flame sensor . Replaced sensor. Also performed precision heat tune up on American standard gas furnace. Replaced 16x25x1 air filter. Checked all electrical conections and components. Checked gas pressure and performed combustion test. Checked temperature rise, and blew out condensate drain and pressure switch hoses. Furnace is working fine at time of service.
Performed two ac check ups, attic and basement units, replace filters flushed drain test pump ok check split electrical low and high ok capacitor and contactor ok check refrigerant pressures ok cycle both units ok, both units running to standard
Water leak, found condensation drain blocked, quoted for repair, also quoted to replace some flue pipe and elbow, customer ok repairs, made necessary repairs and also performed furnace oil tune up, clean exchanger flue pipe, replace nozzle and oil filter .75x80A and RF-1 replace air filter, smoke test and combustion ok cycle heater ok, also service humidifier replace pad and set up for winter
Performed ac check up, check electrical low and high ok filter ok check split flushed drain test pump ok check outdoor unit electrical found very low reading capacitor and contactor making buzzing sound, quoted for repair customer ok repairs installed new capacitor and contactor cycle and test unit r22 pressures ok cycle ok
Performed cooling maintenance, checked media air filter. Inspected cooling coil. Cleaned condensate drain. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started air conditioner, checked refrigerant charge and temperature drop across coil.
Completed Quality Assurance On recently installed Amana AC and Coil. Reviewed Installation with Homeowners. Tested Safety Devices on System. Completed Checklist Form in System.
Checked no cooling complaint, set thermostat to cooling, blower comes on but no outdoor operation. Have voltage and a call, checked run capacitor, found open. Replaced dual run capacitor. Started air conditioner, checked refrigerant charge and temperature drop across coil.