Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Mike and Andy completed the removal of our old mini split system and installed a new unit in less than a day. Work was performed in an extremely neat and meticulous manner.
Very efficient with times and service
Luis was very polite and efficient, took his time and checked everything, I have always had good service from your company
Very courteous. Great explanations
Luis did a good job noticing a problem and applying a quick fix. I know that companies need to make a profit, but 6 times the cost of parts (found on the Internet) is extremely high, especially since the replacement/fix took about 30 minutes.
On time and work completed as required. Service Tech was very professional and answered all the questions I had.
Found after putting thermostat on fan on found oil furnace psi motor trying to run , but not coming on. Found bad 115 volt blower motor and bent wheel. Called distributer and we should be able to get blower motor, wheel, and motor mount to secure it. Replace blower motor, wheel and mount. Removed blower assembly, removed motor, mount and wheel, installed new motor , mount and wheel. Installed new motor capacitor. Wired blower. Checked direction. Started oil furnace and checked operation, motor running at7.2 amps on high speed.
Found lp American standard gas furnace locking out on a code 3 pressure switch error code. When you remove the 3â€ intake pressure switch code went away and furnace will ignite. Used a borescope camera and could not see what was in the pipe. Used a shop vac and tried to pull a vacuum ethier way to vacuum out what is in the pipe. Was not able to remove the clogg vent pipes are in drywall. Furnace is working fine without the intake connected. Talked to homeowner about issue and is ok with solution does not want to cut drywall at this point.
Completed Quality Assurance on Amana Gas Furnace/AC System. Completed checklist Form in system. Reviewed installation with homeowner. When we come back in the spring for the AC Tune Up bring a bag of stone and fill in under the pad and try to level.
Returned to site and removed the old Condensation Pump. Vinyl Tubing was very dirty also. Removed the old vinyl tubing and ran new Tubing from the Condensation Pump to the Wash Sink. Filled Pump multiple times to insure it was pumping and draining properly. Installed an Ecobee SI Thermostat and programmed for the system. Tested operation of system. Set Heat Differential setting on the thermostat at 2 Degrees. Reviewed thermostat operation with homeowner upon completion.
Performed Precision Heating Tune Up on Gas Furnace system. Checked 16x25x1 Air Filter. Filter was clean and in good condition. Inspected Electrical Components and cleaned Furnace Drain Lines. Inspected Heat Exchanger and burners. Heat exchanger has heavy rust forming inside of its chambers. No visible signs of the heat Exchanger being damaged were found at this time, but as the metal continues to rusts it can cause damage to the Heat Exchanger. Burners are in good condition. Performed Combustion Analysis on Furnace. While noted on a previous visit, the Water Heater is about 12-13 years old. Due to the age, would recommend replacement of the Water Heater before any issues occur. Thank You for renewing your Service Membership with us today!
Completed Quality Assurance on American Standard Furnace. Reviewed installation with homeowner. Completed Checklist Form in system. Homeowner wants a thermostat that has the â€œTemperature Overswingâ€ feature. Need to verify if the Ecobee 4/Ecobee Lite have this feature. Need to follow up with customer about installing a new Thermostat, and what pricing would be involved since we just installed the T6 Pro during the install.
Preformed precision heat tune up upon arrival the heater was working fine, upon further review I saw that the burners were rusted out and would start to cause issues, burners are ordered at Johnstones supply under dojka customer paid balance in full and will need to be scheduled for installation Replace burners. Shut off gas, removed gas valve and manifold, removed burner box. Pulled burners and installed new burners. Aligned burners. Installed burner box. Installed gas valve and manifold. Cycled furnace and checked operation ok.
Performed propane gas heater tune up, check electrical low and high ok replace high efficiency filter and also replaced hu pad and serviced humidifier, clean sensor inspect burners ok, check low and high stage on furnace combustion test cle furnace ok emailed price to add red link indoor sensor if customer is interested, master bedroom seems to be hotter than rest of the house
Checked no heat, found no ignition, found power to ignitor but it will not heat up. Checked ignitor, found open. Need to replace ignitor, I do not have the correct ignitor need to return with correct part. Returned with the correct igniter patr# 903758 and replaced. Furnace fired right up and is back in operation with a temperature rise of 42 degrees.
When I arrived found American standard gas furnace locked out on a code 3 pressure switch lockout code. Check each spade terminal to ground off of pressure switch and had 27 volts going thru switch . Unplugged molex conection at control board and pushed back in and it made connection and came on. Control board has a loose conection on the board suggested replacing board and switch in cas conections inside switch are wearing out. Furnace is working for now but told them it wonâ€™t probably stay working.11-7-19 luis installed new control board for furnace and also new pressure switch calibrated switch to close at 1.15 WC test and cycle furnace ok performed combustion test cycle ok,
Performed Six Month Inspection on Amana Furnace. Replaced 16x25x1 Air Filter. Inspected System and checked Furnace Drain Lines. Put system in operation and performed Combustion Analysis on Furnace. Measured Manifold Gas Pressure on system. System is operating to standards at this time. The Air Filters supplied by Homeowner are slightly larger than the Air Filter that was installed even though they are the same size of 16x25x1. Was unable to fit the other Air Filters into the Filter slot. Filter we installed is a PrePleat Brand 16x25x1.
Found pitted flame sensor, replaced flame sensor. Performed precision heat tune up on American standard gas furnace. Replaced 16x25x1 air filter. Checked all electrical conections and components. Blew out condensate drain. Checked gas pressure. Performed combustion test. Gas furnace is working fine at time of service.
Performed precision heat tune up on American standard gas furnace. 16x25x1 air filter is clean. Found transition piece between inducer motor and heat exchanger leaking water. Found pitted flame sensor. Also found heat exchanger very rusted and corroded. Recommend replacing both furnace and a/c together. Also checked gas pressure and performed combustion test. Set up appointment with office for bill to give estimate on replacement.
Found pitted flame sensor, replaced flame sensor. Also performed precision heat tune up on American standard gas furnace. Replaced 16x25x1 air filter. Checked all electrical conections and components. Blew out condensate drain. Checked gas pressure, and performed combustion test. Gas furnace is working fine at time of service. Also recommended replacement of lp gas water heater due to age of tank.
Installed new propane furnace and air conditioner replaced old line set and ran new line set customer requested we moved the thermostat so we did to his desired location with new wire. New pad whip and disconnect installed for outdoor unit. Pressurized to 342 psi for ten minutes and holding triple evacuated and pumped down to 248 microns and held 10 minutes 1.9 ounces added for charge. Tested for gas leaks set low and high gas pressure and did combustion analysis everything was up to factory standards. Customer was provided with instructions. Tested water at 9 grains hardness. Filter 16x25x1