Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Great service, prompt and friendly and well knowledgeable 5 star service!
Your technicians noticed and addressed points overlooked by previous service from another company.
The technician was knowledgeable and did a great job!
Same as above.
Performed cooling maintenance, checked media air filter ok. Inspected cooling coil, cleaned condensate drain and pump. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started air conditioner, checked refrigerant charge, found low on charge. Topped off refrigerant charge, balanced by sun cooling. Checked operation and temperature drop across coil ok.
Performed Precision Air Conditioning Tune Up on System. Checked Washable Air Filter. Filter was clean and in good condition. Cleaned Drain Line and EZ Trap. Inspected and tested Electrical Components on System. Put system in AC Mode and measured Refrigerant Charge. Refrigerant levels were to standards. System is operating to standards at this time.
Performed Precision AC Tune Up on Lennox Heat Pump System. Replaced 16x20x1 Air Filter. Cleaned Drain Line and Condensation Pump. Filled and tested operation of Pump. Had recommended previously to replace the Dual Capacitor and Single Pole Contactor for the Outdoor Unit. Installed a new 45/10 Mfd Capacitor and Single Pole 24V 40 Amp Contactor onto the Outdoor Unit and put system in operation. Measured Refrigerant Charge on system. System is operating to standards at this time. Please note you have a PECO Box Installed onto the unit. PECO May disrupt AC service during the summer temporarily, which would cause the AC to not run. This usually does not last more than 5-10 Minutes.
Performed Precision AC Tune Up on system. Replaced 16x25x1 a Air Filter provided by Homeowner. Cleaned EZ Trap and reviewed with Homeowner how to clean the EZ Trap. Inspected Electrical Components on System. Put system in AC Mode and measured Refrigerant levels. System is operating to standards at this time.
Performed Precision AC Tune Up on system. Replaced the 16x25x1 Air Filter. Inspected Indoor and Outdoor Coils to ensure they were clean and in good condition. Cleaned EZ Trap and blew through Drain Pipe. Inspected Electrical Components on System. The Dual Capacitor which the Compressor and Outdoor Fan Motor utilize is testing within rating but is starting to get close to the lower end of its rating on the Compressor Side. The Capacitor is rated for 35/5 Mfd and is testing at 33.5/5.0 Mfd. Measured Refrigerant Charge on system and recorded Supply and Return Air Temperatures. System is operating within standards at this time. Average life for these systems is between 8-12 Years. This unit is about 10 Years old. Would recommend begin planning/saving for replacement of the system in the future.
Performed Precision Air Conditioning Tune Up on System. Replaced 16x25x1 Air Filter. Inspected Electrical Components and Control Board for System. Cleaned EZ Trap and cleared Drain Piping. Measured Refrigerant Charge on system. Measured Supply/Return Air Temperatures and recorded Amp readings on system. System is operating to standards at this time. System is about 10-11 Years old. Average life for these units are between 8-12 Years. While the system is operating to standards currently, would recommend begin planning/saving for replacement.
Called Mary to discuss options over the phone. Resent revised proposal for American Standard equipment.
Performed peco heat pump tune up. Replaced 20x25x4 air filter with a 20x25x1 air filter. Checked all electrical conections and components. Checked refrigerant pressures and temperatures at indoor and outdoor units. Blew out condensate drain. System is running to manufacture specifications at time of service. Customer needs a copy of the invoice sent form the office.
Performed Precision Air Conditioning Tune Up on Carrier System. Replaced 20x25x1 Air Filter. Cleaned Condensation Pump and Drain Line. Inspected Electrical Components on Indoor and Outdoor Unit. Measured Refrigerant Charge on system. Checked Amp readings of compressor and Outdoor Fan Motor. System is operating to standards. When the AC System First turns on, a dimming of the Lights was noticed from the basement. If this is happening throughout the house it is a result of the Outdoor Unit drawing some extra power upon startup. A Hard Start Kit would be recommended to correct this issue. Spoke with Homeowner about an issue with the Hallway being very hot in the summer. The Whole House Fan is located in the Hallway. This is not insulated and the Heat could be leaking through into the house. Would also recommend looking at the quality/level of insulation in the Attic as well.
Noise from unit, found noise coming from blower motor, removed chassis and also removed blower wheel, tried to align wheel and motor, coils not get to work, needs new blower motor and wheel, also found thermostat not responding to commands, replace thermostat currently a mercury stat replace stat with digital T6 thermostat, units were installed in 2017.
Performed ac check up/tune up, replace filter, flushed drain with 2 gallons of water ok add tabs to pan, check electrical low and high ok, found both capacitors very low, quoted for new capacitors and also to install high spike connector for surge protection customer ok repairs, installed new 35/5, 7.5 for blower and also spike connector for electrical side incoming into unit, cycle and check split ok
Performed ac tune up on trough the wall ac unit, check electrical low and high ok replce filter, flushed drain ok used 2 gallons of water to flush drain ok add tabs, check capacitor and contactor ok check split ok cycle unit ok
Performed ac tune up, on trough the wall package gas heat ac unit, replce filter, check electrical low and high ok make sure drain line is clean, flushed drain trap with 1 gallon of water ok draining ok add tabs to pan, check r22 pressures ok cap and contactor ok would highly recommend installing an reme purifier
Performed a/c tune up on thru the wall package a/c unit. Blew out condensate drain , checked all electrical conections, and tested amp draw of compressor. Also checked 410a refrigerant pressures and temperatures . A/c system working fine at time of service.
As per Condo Association, installed new EZ Trap Drain onto Condensation Drain Pipe. Removed old Trap and section of Drain. Repiped Drain Line with EZ Trap Installed. Wired EZ Trap into the 24 Volt Power of the system. If the Drain Trap becomes clogged, it will trip the internal Switch in the Trap and shut the system down.