Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Second opinion on system repairs, customer has 100000 btu trane two stage furnace with 4 ton trane 2 stage heat pump, found unit running upon arrival, check supply air and return delta 18F, check outdoor unit found two wires terminals going to low stage compressor in bad shape, also open 5 mfd second stage compressor capacitor, quoted to repair electrical terminals and replacement of capacitor for 2 stage compressor customer approved repairs, check operation of first and second stage from communicated trane thermostat and fist and second stage came on with no issues, check refrigerant pressures 320/140 18 delta, cycle unit ok
Performed cooling maintenance, checked media air filter ok. Cleaned condensate trap and drain. Checked voltage, amperage and electrical connections, measured capacitor values. Started air conditioner, checked refrigerant charge and temperature drop across coil. Checked up light, old service experts biofighter light, found both bulbs failed. Recommend replacing up assembly
Performed heating maintenance, checked attic media filter ok. Replaced basement standard air filter. Blew out condensate trap and drains. Cleaned burners and flame sensors. Inspected heat exchangers. Checked voltage, amperage and electrical connections. Started gas furnaces, tested limit and safety switches. Measured fuel pressures. Performed combustion test. Checked operation and temperature rise.
Performed cooling maintenance, replaced media air filter. Checked voltage, amperage and electrical connections, measured capacitor values. Cleaned condensate trap and drain. Checked condensate pump ok. Started air conditioner, checked refrigerant charge and temperature drop across coil.
Performed cooling maintenance, replaced air filters. Cleaned condensate drain and trap. Checked voltage, amperage and electrical connections, measured capacitor values ok. Started heat pumps, checked refrigerant charge and temperature drop across coils.
Disconnect Power and remove wiring and failed control board. Install new OEM Control Board for Furnace. Complete all wiring connections. Remove Ignitor Assembly and Wiring Harness. Install new 120V Ignitor Assembly and Wiring Harness. Program Control Board as necessary. Restore power to system and test operation of Furnace. 1/28/20. Installed new control board and igniter. Performed combustion test and checked temperature rise. Furnace is working fine at time of service.
No heat, found blower not running, ecm motor, test ecm ok, check board and board is not sending 24 volts to motor, we would have to get pricing and have to call customer with proposal
Checked complaint about water on the floor around the air handler, cleared condensate drain, cleaned condensate pump. Started air conditioner, checked refrigerant charge, found under charged. Topped off refrigerant charge, balanced by sub cooling. Checked operation and temperature drop across coil. Signed up for cooling only maintenance plan please start in spring 2020
Performed quality assurance inspection of systems. Need to cut new trim and go back and repair trim and install new hatch.
Needs control module for outside new furnace, coil, outdoor,pad, whip, disconnect must add additional charge to outdoor unit. Replaced downstairs added humidifier drain line was re routed from outside to discharge line
Provide estimate on ac and furnace options. Recommend hybrid system.
Performed two propane heat tune ups, check electrical low and high ok new filters, inspect heater burners and exchanger, down stairs heater in bad shape, even know passed combustion test, visual inspection is really bad, burners and exnchager cells are al rusted/corroded and metal is thin by now, can lead to faster cracks, on second floor heater blower on and off test was very different o2 difference there was 2% difference with blower on and off, also inducer making loud noise, bearings are starting to go bad is just time for the inducer to go bad completely, overall recommendations to replce both heaters due to condition and for human safe,
Evacuated system and charge with Refrigerant. Add Leak Dye to the system and replaced Capacitor. Tested system and system is running to factory standards.
Arrived onsite to perform AC Tune Up on system. Was informed that the First Floor system was not cooling the home. After testing system, found the system was completely flat of Refrigerant. Pressurized system to 250 PSI. Used Leak Bubbles to check all connections on the Indoor Coil and Outdoor Unit. Isolated the Indoor Unit by closing the Service Valves and the pressure held at a constant level. Opened the service Valves to reintroduce the Outdoor Unit into the system and the Pressure began to drop. Opened Lid of the Condensing Unit. Inspected Connections and leak checked all visible tubing and connections. Sprayed coil with Leak Bubbles wherever the fins on the Coil were bent or damaged. Was unable to determine the source of the Leak. The Leak is coming from the Condensing Unit, but the exact source of the leak is not known at this time. Need to return to evacuate the system and recharge with Refrigerant. Recommend adding Leak Dye to the system as well to help determine Leak point.
No heat call in Thornton. While troubleshooting, found feathers and remnants of a bee's hive in the Intake Pipe. Had to cut open the Intake Pipe to access. Found a large bees nest causing the airflow blockage in the Intake.