Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Initial Installation made a mistake in not having the 2 stage A/C engage correctly. Luis found the mistake quickly and made the necessary changes so that it works as it's supposed to.
Kurt (as well as our experience with the other service technitions in the past) was great! He took the time to explain the problem to us and gave great advice on our options. Thank you!
Chris was thorough in inspection and quoted remedies
Luis diligently performed the tasks of the job very well and advised on some future issues. We feel good about being a member of DiBiase H&C. Thank You!
Water leak, found bad condensation pump quoted to replace pump customer approved repairs, installed new pump and wires safety, test pump operation also cycle furnace ok, also test humidifier ok no other leaks present.
Performed heating maintenance, checked air filters ok. Blew out condensate trap and drain. Cleaned burners and flame sensor, inspected heat exchanger. Found rust and pits throughout the heat exchanger. Started gas furnace, tested limit and safety switches. Measured fuel pressures. Performed combustion test. Furnace failed combustion test very high co reading. Recommend replacing furnace.
Replaced Need nut and ferrule for humidifier solenoid test and check operation of humidifier ok, check wiring for humidifier and humidistat all wiring is correct. Customer will run on humidifier when is time currently is off.
Performed heating maintenance, replaced air filters. Cleaned burners and flame sensors, inspected heat exchangers. Blew out condensate trap and drain. Checked voltage, amperage and electrical connections, measured capacitor values. Started gas furnaces, tested limit and safety. Performed combustion test. Checked operation and temperature rise.
Heat tune up for 100K BTU natural gas furnace. Replaced 20x24x1 filter. Cleaned flame sensor. Checked hot surface ignitor resistance. Inspected burners and heat exchanger. Checked temp rise. Performed combustion test. Completed gas furnace inspection form. System is operating safely at design conditions at the time of this maintenance. Solenoid inlet fitting is broken. Humidistat is not able to control humidifier. Need to schedule service to wire humidistat and fix solenoid inlet. (Need nut and ferrule for 1/8â€ copper. Humidifier is not working.
Sucked back old ac unit. Cut out old airhandler and installed a new amana airhandler on existing drain pan. Modified supply metal as needed and taped and sealed all duct. Brazed and leak checked with nitro and bubbles. Vacuumed and cracked charge. Installed a new ez trap and ez trap wired into system. Tested heatpump in ac and heat.
Customer was trying to replace filter, by accident shorted wires, found open fuse 3 amp, replaced fuse and test operation ok cycle unit supply air 53 return 71
Return visit to replace and add panning on return duct, also we will sealed all gaps on return duct between bay and existing paning for the main two connections. We will add piece of panning to connect two return bays right now there are not connected and blower is getting return air from basement check all worked performed and went over with customer, now all return air is mostly coming from first floor, would recommended leaving master bedroom door open to circulate air from that room.
Performed quality assurance on recently installed system, system is zone 3 zones and it is using a Arzel system, noticed system is going off on low supply temp limit, system would only work for about 5 minutes would cycle on low temp limit, with one or all three zones calling, supply temp 40 turned down limit to 35 and check operation refrigerant pressures ok noticed return air is 68 F...first floor temp is 74. System is pulling return air from basement found gaps and one open return informed customer about findings would recommend sealing the gaps of main return truck using silicone and also replace 3 pieces of paning so we can sealed return duct connections.
Found bad ECM Blower motor. Need to find availability and price. Will reschedule to replace blower motor.
Checked no cooling complaint, set thermostat ro cooling and the air conditioner started and cooled. Checked refrigerant charge ok. The thermostat is a old mercury bulb thermostat with mechanical switches. Replaced thermostat. Set up thermostat. Pro framed thermostat. Cycled and checked operation ok.
PECO Heat Pump Tune Up. Tested AC. 16F temp split. Replaced filter. Tested all electric components. No trap at drain; coil on negative side. Tested condensate pump. High Superheat Low suction pressure during cooling. Tested for leaks using IR leak detector. Indoor coil should be replaced. Ran System in Heating. Strip heater is not energizing on call for HP. Checked heat pump. temp split. Checked amp draw and temp split during emergency heat cycle. Completed PECO Heat Pump Tune Up Form Provided estimate to install EZ trap and become a plan member. Provided Estimate to become plan member and replace indoor coil. Provided Estimate for plan membership, replace indoor coil, and install EZ Trap.
Performed free water test and water hardness is 16 grains hard. Installed a new amana gas furnace in existing location. Installed amana coil on top with a txv installed. Ran new copper lines from indoor coil to new amana ac unit. Brazed and leak checked with nitro and soapy bubbles. Ac is on a level pad pushed over towards Busch per customer. Installed new disconnect box and electrical wiring to unit. Installed new condensate drain with ez trap wired in to unit. New condensate pump with new vinyl tubing ran over to sink. Reattached supply and return metal. Caulked and taped all duct. Installed a new 20/25/5 filter. Installed 3 new t6 thermostat. Tested unit in heating and cooling. Payment collected.
Performed cooling maintenance, replaced standard air filter. Inspected cooling coil. Checked voltage, amperage and electrical connections, measured capacitor values. Started air conditioner, checked refrigerant charge and temperature drop across coil.
AC Tune Ups for both systems. Replaced both filters. Checked drain, electrical and refrigerant performance/data. Completed AC tune Up forms for each system. Both Systems are operating well at the time of this tune up.