Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
From start to finish the DiBiase team was great to work with for our full HVAC system replacement. We’ve already referred them to friends.
The owner of the business couldn't have been nicer- he had been recommended to me by my neighbor who was also very happy with the service and product. The technicians showed up promptly- they were very courteous and very informative. They did a great job- and checked and rechecked everything. I have already recommended them to another neighbor.
Tech had a good attitude, was respectful
Brian has been servicing my heat pump for years now. It is always a very pleasant experience. Brian is always on time, very pleasant and very professional. I have just recommended the company to my neighbor who will be purchasing a heat pump from them.
Thank you - you guys did a terrific job!
Knowledge of the equipment and systems was excellent. Good communication and treated with respect.
Chris was prompt efficient and personable.
Turn Oil supply off and cut oil line. Install a new RF-1 Oil Filter Canister onto the Oil Line and reconnect. Purge system of air and test operation. 11/30/20. Installed oil canister with rf1 oil filter. Tightened and secured conections. Checked flare and thread conections for leaks. Cycled thermostat on emergency heat and bleed oil line to furnace. Oil furnace is working fine at time of service.
Placed tarp back over air handler to prepare for roof to be re-done. Found that while I was up in attic some large bees started flying around, let homeowner know about this so she can have them removed.
Performed precision heat tune up on Goodman gas furnace. Found 20x25x4 air filter is dirty. Replaced with 1â€ 20x25x1 for now( homeowner to replace larger filter). Serviced Aprilaire humidifier with #35 humidifier pad. Checked all electrical conections and components. Blew out condensate drain and pressure switch tubing. Cleaned flame sensor. Checked temperature rise. Tested condensation pump. Checked gas pressure and performed combustion test. Gas furnace is working fine at time of inspection.
Sent to perform heating maintenance, found that there is only a air conditioner. Will return in the spring to perform cooling maintenance.
Performed heating maintenance on lp boiler. Cleaned burners gun and sensor. Adjusted manifold pressure to 3.39â€ from 3.97â€. Cleared air intakes. Tested limit and safety switches. Checked draft. Inspected flue pipe. Checked barometric damper. Checked water pressure and temperature.
Performed Precision Heating Tune Up on Oil Fired Furnace. Replaced 16x20x1 Air Filter. Furnace had a washable filter installed in the Blower Cabinet also. Removed the washable filter from the unit as it is not needed with the replaceable filter. Replaced Oil Nozzle and Pump Strainer. The oil line does not have an oil filter installed on it. Would recommend installing an Oil Filter on the system to help keep debris and dirt from getting into the the Oil Burner and Pump. Cleaned Flue Pipe, Chimney Base, and Heat Exchanger. Put system in operation and performed Draft Test, Smoke Test, and Combustion. Measured Air Temperature readings on Oil Furnace. System is a hybrid heat pump/oil Furnace. Switched over to heat pump and measured Air Temperatures. Measured a 25 Degree Split on the Heat Pump. Performed Heat Pump tune up on the second system. Replaced 16x25x1 Air Filter. While testing system, found outdoor unit was going off on high pressure. Removed refrigerant from the system to test wh
Performed oil furnace tune up, check electrical low and high ok filter ok cleaned heat exchanger and flue pipe, also cleaned chimney base, replace pump strainer and nozzle, customer provided oil filter garber spin off style, check air and fuel mixture, performed smoke and combustion test ok cycle furnace check temp rise, cad cell is getting discoloring, reset electrodes at this time both electrodes are within range, would recommend replacing next time,
Returned to site to install a new Humidifier. Disconnected and removed existing Humidifier. Installed new Aprilaire 600M Bypass Humidifier. Ran new Water Line and installed Control above Humidifier. Ran new Wiring to Furnace and wired into system. Sealed Humidifier around ductwork. Cleaned Condensation Pump and blew through vinyl tubing. Condensation Pump was extremely dirty and does not have a safety float. Filled pump multiple times to test operation. Due to how dirty condensation pump was and not having a safety float replacing with a new Pump is highly recommended. Spoke with homeowner about concerns and included an Estimate for replacement. Turned heat on and tested Humidifier. Set control to 35% upon completion.
Performed heating maintenance, replaced standard air filter. Checked voltage, amperage and electrical connections, measured capacitor values. Tested electric back up heaters. Started heat pump, tested defrost cycle. Calculated btu output. Checked operation and temperature rise across coil.
Checked no heat complaint, found gas boiler temperature down to 70. Found no 24 volts at fan center. Checked incoming voltage getting 121 to the control. Need to replace boil fan center.11-20-20 Luis return call to installed new fan center for boiler, installed new fan center and start operation during testing transformer was over heating until blew its windings, smoke was coming out, found one of the taco heads was shorted cresting high resistance and overheating fan center, installed amp fuse customer replaced power head, cycle operation performed combustion test ok test high limit ok
Performed Quality Assurance inspection on a newly installed gas furnace and air conditioning system. Checked over entire system. Wiring proper and secure. All penetrations sealed and ductwork sealed. No leaks at gas line. Disconnect was not level but outdoor unit is. System working great at time of QA
No heat kitchen area number 2 zone, other two zones customer stated are heating ok, check boiler operation previously customer had issues with zone 3 overheating, found zone valve number 2 not attached completely to body of valve, repositioned valve so is making good contact between body and actuator, zone valve is getting voltage and it is closing end switch closing t t in boiler....zone 2 is now getting heat,,,, not sure if actual valve is going bad ...weak mechanism, or some one by accident hit the valve, would recommend having boiler cleaned and if problem keeps occurring would recommend replacing complete valve check water pressure added water to boiler 15 psi and also combustion test
Service call that the Heat Pump was running non stop. Upon arrival found thermostat set to 65 Degrees and temperature was satisfied. Turned temperature up to test operation. Measured air Temperatures and was measuring about a 15 Degree Temperature rise. Checked refrigerant pressures and system appeared to be low on refrigerant. On previous visit had added refrigerant and leak dye to system. Used UV Light and searched indoor and outdoor unit for signs of a leak. Could not find any leak point in the system. To get system back up and running began adding refrigerant to system. Found the Suction Refrigerant pressure was not increasing and the high pressure was rising. The Outdoor TXV is restricted and is not allowing the proper amount of refrigerant to flow through the system. Will need to replace TXV for the system to operate properly. As system needed refrigerant charge on last visit, system may also have a leak that would be an additional repair once the leak point has been determined.
Checked no heat complaint, found furnace switch off on first floor furnace, turned on, furnace started and ran. Checked air filter, getting dirty. Checked operation ok. Checked second floor furnace found furnace switch off. Turned furnace on, could heat banging coming from the furnace. Checked furnace, found off on limit. Reset limit. Furnace tried to light but a large flame roll out occurred. I can see soot in the primary heat exchanger. I recommend replacing furnace due to to scooted and restricted heat exchangers. Shut furnace off until repairs are made no heat on the second floor at this time.
Returned to replace compressor capacitor, shut off power, confirm witch capacitor is bad. Replaced 80 uf compressor run capacitor. Started heat pump and checked amp draw.