Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Kurt was very informtive on everything did not delay in his job a perfect gentleman
Really know how to fix things.
Bill was excellent . No high pressure reviewed options. Gave great educational review of what to have in a HVAC system. Switched my service agreement to his co.
Same as above
Very profesional workers on time, respectful and did great work.
Took time to carefully check the system and explain the options for repairs.
Kurt was very professional & knowledgeable. He answered all my questions, very patient and kind.
Brian is a very friendly and informative Teck.
Found a serious problem my last company Horizon would never have found because they admitted that they never clean the flue.
Found thermostat calling for cooling up to defrost board but low pressure switch is open. Found no refrigerant in the system. Found some oil it look like at both outdoor and indoor coil. Recommended to Wayne to replace the system. Called our office and discussed all the details. Office to send over replacement estimate.
First day Disconnected and removed old oil furnace, also removed customers old humidifier per customer. Removed old outdoor unit line set line voltage and low voltage wires. Installed new electric heat pump heater and AC, installed new Bosch outdoor unit on pump of legs, also installed new disconnect box pad and stone. Ran new three-quarter inch refrigerant lines along with 8 wire thermostat wire. Breached the refrigerant lines indoor and outdoor and play system on a nitrogen test system held for 30 minutes at 300 psi. Then placed system on vacuum pump pumped down 157 Âµm, Lines that was under 15 feet. Installed new easy trap ran new vinyl tubing to discharge inside at the plumbing stack. Also capped off old chimney and sealed up line set holes inside and out customer is getting Mark Hetchler to remove oil tank and oil inside. Installed new Bosch air handler on new return box. Supported air handler with 3 inch PVC in the box. Installed new supply ductwork. Taped and sealed all holes
Performed cooling maintenance on attic second floor heat pump. Cleaned condensate trap and drain. Replaced air filter. Checked voltage, amperage and electrical connections. Measured capacitor values ok. Started heat pump, checked refrigerant charge, found system low on charge. Topped off refrigerant charge, balanced charge by sub cooling. Checked operation and temperature drop across coil. Need to schedule first floor cooling maintenance. Need to quote to level first floor outdoor unit
Performed cooling maintenance, checked air filter ok. Cleaned condensate trap and drain. Checked voltage, amperage and electrical connections, measured capacitor values. Started heat pump, checked refrigerant charge. Checked operation and temperature drop across coil.
Plan member AC maintenance 2.5 Ton Amana AC: Replaced 20x20x1 Filter. Measured static pressure and temperature split. Checked wiring, controls electric motors and components. Checked condition of both indoor and outdoor coils. Checked EZ trap and drain. Tested pump. Checked refrigerant pressures and diagnostics. AC system is operating well at the time of this maintenance.
Plan member AC maintenance; 2 Ton Carrier Infinity AC system: Replaced 14x25x1 Checked and tested drain. Measured temperature rise. Measured static pressure. Checked wiring, controls, electric motors and components. Both indoor and outdoor coil are in good condition. Checked refrigerant pressures and diagnostics. AC system is operating well at the time of this maintenance.
Had homeowner give thermostat a call for cooling. System came on and had no codes at the outdoor board. Checked refrigerant pressures, pressures were good. Got homeowner to turn temperature up to cycle of outdoor unit. Turned temp back down in cooling, system came on correctly. Homeowner had turned down temperature on way home from vacation and said it was at 75 when he came home and expected it to be cooler. System is working fine at time of service.
Found after hooking up gauges to thru the wall heat pump system, found head pressure climbing the whole way to 500 psi and shutting off. Found outdoor fan motor running but cutting out in the middle of a call. Fan motor and compressor were replaced by another company. Went to a different unit inside the building and checked how ecm fan moter was wired. ( could not find a schematic for this exact motor online). Changed wiring to match other apartment fan motor wiring now fan motor is staying on and system is cooling with a 15 degree split. Heat pump system is working at time of service.
Water leak from kitchen mini split head, noticed some water dripping from front cover, removed cover and inspect drain line, found drain line not connected and draining directly behind wall, tried to re connect drain line, would not stayed together, needed longer piece, added 3 extra inches of drain line and strap drain line along line set and creating slope alway from unit, after repairs check drain by adding one gallon of water into drain pan, drain line is draining ok with no issues. Ran unit for 2 minutes (customer had to leave) filters need to get clean, customer will take care of them since he needed to leave. No charge installation warranty
Performed ac tune up on two Lennox units, 3 and 2 ton check electrical low and high voltage connections, replaced filter flushed drain check airflow return and supply ok inspect both indoor and outdoor coils, check outdoor unit refrigerant r22 pressures capacitor and contactor, both units contactors are in bad shape making sound, capacitors are still within manufacture standards, both units uses R22 Freon, no longer available, first floor compressor takes a minute to come on, itâ€™s a sign that will be going bad soon, outdoor disconnect is very difficult to removed pullout disconnect, provided an estimate to replace both contactors and adding hard start assist to both unit, and replacement of high voltage disconnect would recommend replacement of both ac units. Home comfort consultant to reach out to customer regarding new ac systems proposal.
Performed precision a/c tune up on Payne a/c system. Replaced 14x20x1 air filter. Checked all electrical conections and components. Found no safety on condensation drain itself. Recommend installing an ez trap. Checked temperature split at indoor unit. Checked refrigerant pressures and temperatures at indoor and outdoor units. Also visually inspected water heater and found some fittings going into water heater not in the best of shape. 80 gallon electric water heater is 14 years old. Provided estimate to install a new Bradford white water heater that is 50 gallon ( homeowner now has less people living in the home). Checked refrigerant pressures and temperatures at indoor and outdoor units. A/c system is working at time of service.
No cooling 5 Ton Amana AC system: Found tripped. 240V breaker for outdoor equipment. Checked all electric components. Reset breaker. Ran system in cooling, checking a,p draw and monitoring refrigerant data. Checked filter. Checked temperature split. System is operating well at the time of this service.
2.5 Ton Heat pump: System was locked out on low pressure. 9PSI standing. Charged system with R410A. Found lose/leaking Schrader core at high side service port. Tightened Schrader core. There was no filter at indoor equipment. Added filter. Made filter rack accessible. Explained filter replacement to homeowner. Checked all wiring, electric motors and components. Filter size 16x20x1 Final refrigerant data 100/235 20SH 7SC 68F outdoor dry bulb. 50% RH. Temperature split 20F AC system is operating well at the time of this service. Strongly recommend AC Heat Pump Plan membership.
Installed new Amana air handler in attic. Installed new support bracket for unit. Installed new unit on leveled swing, plywood and aux drain pan. Installed unit on snow legs. Installed new Aprilaire 3310 filter. Adpated to existing return and supply plenum. Sealed all duct connections. Installed new flex duct for each supply run and installed new 16in return flex with collars. Installed new lineset and linehide. Pressure tested past 300 psi and evacuated below 500 microns. Installed new reme halo for attic system. Installed new supply plenum and reme halo for basement system. Installed new disconnect for attic unit and installed new ez trap and condensate line. Installed new wet switch and wired all safetyâ€™s. Installed new heat pump on leveled stone and pad. Installed new disconnect and whip. Tested system in heating and cooling, system working properly. Work area cleaned.
Had to first locate outdoor unit, located outdoor unit by turning off power to indoor disconnect and checking for 24 v to r&c at roof top heat pumps. Located outdoor heat pump and found thermostat calling but unit flat on charge. Wayne wanted to just charge the unit for now to see how it works. Addded 8lbs 6 ozs of r-410a (they provided). Pressures were 256/112. System is working fine at time of service. No further work on this system at this time.