Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
On time and thorough
Brian did a great job. Very nice and professional as well.
Excellent service! We will call for service again for sure.
Informative when asked questions, considerate and friendly professional service.
Performed precision peco heat tune up on 2 heat pumps. 1 mini split heat pump, and 1 luxaire heat pump system. Replaced (1) 20x25x1 air filter. (1) washable air filter on mini split system. Checked all electrical conections and components. Found strip heater not working on luxaire heat pump, homeowner will let us know if the want to repair or not. Checked refrigerant pressures and temperatures at indoor and outdoor units.
Found when we arrived found nothing running . Found that outdoor unit was locked out on high pressure lock out but indoor unit was not running on emergency heat. Found that common wire was loose on terminal block at indoor unit tightened up conection and turned system back on and checked refrigerant pressures. Pressures were 279/81 at 42 degrees. Also found air filter is pretty dirty it is a 20x24x1, this does not help with airflow, homeowner is going to pick one up recommend to Change more frequently than every 3 months . Also performed a new software update on system and checked over set up in cool cloud. Found a code in cool cloud that said blower motor not running, incorrect or loose wiring, or fan motor upstruction. Checked over rest of settings in cool cloud. System is working fine now.
Found that after homeowner gave call for heat humidifier came right on. There was water draining in the condensation pump. Humidistat was set on 45% humidity. Explained to homeowner on warmer days like yesterday , if the heat pump is not giving to many calls for heat to come on , your humidifier will not be running. Then also customer mentioned an oil smell like heating oil , found nothing inside air handler and also examined air scrubber, found nothing burned . Do not smell anything at unit that smells like heating oil.
Found bad blower motor. Found furnace running and control board sending 120v to blower motor. Homeowner replaced capacitor earlier today which capacitor tested ok. Found motor has failed. Replaced blower motor with motor 1/2h.p. Motor had on truck and performed combustion test. Furnace is back up and working fine again. Offered membership, homeowner just wanted to repair at this time.
Performed precision heat tune up on gas furnace. Replaced 20x25x1 air filter. Checked all electrical conections and components . Cleaned flame sensor. Blew out condensate drain and pressure switch tubing. Checked temperature rise. Checked gas pressures and performed combustion test. Gas furnace is working fine at time of service. ( furnace is running under extreme temperatures)
Performed precision peco heat tune up on Coleman heat pump. Electronic air filter is clean. Found very clogged up humidifier pad , serviced humidifier with Aprilaire #35 humidifier pad. Checked operation of emergency heat. Checked refrigerant pressures and temperatures at indoor and outdoor units. Heat pump is working fine at time of service. Also found leaking 80 gallon electric water heater. Talked to homeowner about replacement. Water heater is a 2005. They only have two people living there so wanted a price on a 50 gallon electric. Found leaking 80 gallon hot water heater, replaced with 50 gallon 1. PECO Acc# 6681069149 2. Measured refrigerant charge and took air temperature measurements. Suction Pressure 81 and liquid pressure 370. Refrigerant was to standards. 3. Filter is clean. 4. Motors are encased motors and do not need to be lubricated. 5. Evaporator and condenser coils were inspected and did not need to be cleaned. 6. Heat pump capacity is 48,000 Btus for heating and coo
Service call that there was no water pressure from the fixtures after we installed the Expansion Tank. Tested pressure at the Water Heater upon arrival and found pressure to be low at 40 PSI and when a faucet or Shower was turned on very little water was coming out. Adjusted the Pressure Reducing Valve on the incoming water to the home. Increased water pressure to 65-70 PSI when the water Heater was fully heated. Tested all sinks and Shower in the home and found Water pressure had increased back to normal levels.
Performed precision peco tune up. 20x20x1 air filter is clean. Checked all electrical connections and components. Checked refrigerant pressures and temperatures. System is 18,000 btu. System is a 1992. Overall condition is ok but should be replaced due to age of the system. Homeowner does not use system at this time.
Found blown bladder on expansion tank. Called son about bad expansion tank , replaced st-12 expansion tank and found water pressure at 110 psi, adjusted pressure reducing valve to 55psi. Also performed precision heat tune up on American standard gas furnace. Replaced 14x25x1 air filter. Checked all electrical conections and components. Checked gas pressure and performed combustion test. Also cleaned flame sensor and blew out pressure switch tubing. Gas furnace is working fine at time of service.
Install new Lineset for the Second Floor Attic Unit. Run Line Hide down Outside Wall and seal Wall Penetrations. Pressure test system and test for leaks. Perform Evacuation on system to below 500 Microns. Release refrigerant to the system. Test system and weigh in additional refrigerant 2.1 pounds. Checked basement system and added 4 ounces
Performed gas heat tune up check electrical low and high ok replace air filter noticed blower wheel very dirty would recommend removing blower and cleaning on the outside, check burners and clean flame sensor performed combustion test cycle furnace ok noticed lot of corrosion on the burner monitors and gas pipe, due to condensation from intake pipe would recommend adding drain kit on intake to prevent any further damaged to other parts
Upon arrival found system off, check heater operation and found defective inducer assembly, quoted for new assembly customer ok with repairs installed new inducer assembly and test operation ok cycle furnace combustion test ok customer signed up for service plan
Installed emporia vue monitoring system on power wires inside air handler to help vue energy usage. Took pictures of install. Also took down login information to be able to monitor from our office. Outdoor wire is rated for outside usage and does not need seal tight covering.explained to homeowner condionions where outdoor heat pump is not running at all and still getting heat from vents it could be only on emergency heat at this point. Also explained defrost cycle.
System 1: Disconnected and removed old heater , coil and ac unit. Replaced it with a new American standard heater and coil. Adapted all duct work as needed and installed a new Aprilaire HE filter. Taped and sealed all duct work. Ran new copper lines from indoor coil to new American standard outdoor ac unit . Brazed and nitrogen tested with 300 psi. Ran a new 4x4 electrical box and added a double outlet and switch . Installed a new condensate drain with an ez trap wired in. A new pump with new vinyl tubing to discharge. Adapted all gas piping as needed and checked for leaks with soapy bubbles. Caulked all penetrations into the house. Installed a new t10 thermostat. Adapted flue piping as needed. Installed a American standard ac unit on a new pad with rocks underneath. A new disconnect box and whip ran to the unit. Performed a combustion test and tested unit. System 2: Disconnected and removed old equipment. Installed a new American standard heater , coil and ac unit . Installed heate
Performed precision heat tune up on New Yorker oil boiler. Replaced rf2 oil filter. Replaced.85x60b nozzle. Performed smoke and combustion test. Oil boiler is working well at time of service.