Have any feedback for us? We'd love to hear it! Call us at (610) 595-9072 and let us know how we are doing.
Curt is a professional HVAC man. He wore a mask, boot covers and most of all he made us feel comfortable to do business with. He explained exactly what he had to do on his job assignment. He also replaced a dented outside unit cover under warranty at no charge.
Paul,Zack & Luke did an excellent job on our heat pump installation. I would recommend them if you want 3 installers who work hard to please the customer.
I will definitely use your co in the future
Very professional yet friendly service. Took time to answer all my questions thoroughly and clearly cares about, and takes pride in, providing quality service.
Brian was neat, tidy and efficient and let us know he was on his way. Photograph of Brian in the text message so we knew who to expect made us feel safe and secure. And the office was diligent in their follow-up to get the scheduled maintenance preformed. Great job servicing the AC.
timely, respectful, knowledgeable, prompt
He is as very professional, informative and courteous
Performed oil heater tune up check electrical low and high ok cleaned heat exchanger and flue pipe, replaced nozzle and pump strainer, cleaned cad cell, test transformer ok check blower cap and motor, performed smoke test and combustion ok cycle furnace, noticed cad cell has discoloring and electrodes are wearing out, exhaust pipe has Corrosion and metal is very soft would recommend replacing all three items, emailed proposal for recommendations
Replaced damaged side on condenser.
Performed heating maintenance on 2 gas furnaces, replaced air filters. Pulled and cleaned burners and flame sensor, inspected heat exchanger. Blew out condensate traps. Checked voltage, amperage and electrical connections, measured capacitor values. Started gas furnaces, measured fuel pressures. Performed combustion test. Tested limit and safety switches. Checked operation and temperature rise. Found on the first floor furnace the inducer was noisy and found failing bearings. Need to replace first floor inducer. 9/15/20. Installed new inducer moter. Connected all electrical conections and mounting hardware. Also performed combustion test. Gas furnace is working fine at time of service.
Reclaimed and removed old ac and coil.removed old furnace and replaced the furnace with an American standard furnace on feet. Installed a new American Standard coil on top of heater and adapted all ductwork as needed. Installed a HE filter in the return and sealed all duct. Filter size 413 . Installed a new American standard ac unit on a new plastic pad and new disconnect box and electrical wiring to unit. Ran new copper lines and brazed and leak checked with nitro and soapy bubbles. Cut in new plastic pvc piping and ran to heater. Caulked around pvc. Installed a new condensate pump with new vinyl tubing. New condensate drain with ez trap wired in. Installed a reme and t9 thermostat. Adapted gas line and electrical wiring. Tested unit in all modes. Drained down and removed old hwh and installed a new Bradford white hwh with 2 new shut offs and an exspansion tank. Tested hwh and it is working good.
Performed cooling maintenance, replaced standard air filter. Blew out condensate trap and drain. Checked voltage, amperage and electrical connections, measured capacitor values. Started heat pump, checked refrigerant charge and temperature drop across coil. Please call: Mr. Wilkerson wants to talk to someone about replacing his heat pump.
Performed heating maintenance, replaced media air filter, serviced humidifier, cleaned and replaced water panel. Checked voltage, amperage and electrical connections. Cleaned burners and flame sensor, inspected heat exchanger. Started gas furnace, tested limit and safety switches. Measured fuel pressures and performed combustion test. Checked operation and temperature rise
Checked no cooling blower motor making noise, found variable speed blower motor, checked bearings ok. Checked blower wheel ok. Started air conditioner, checked blower operation ok. Checked refrigerant charge and temperature drop across coil. Found no reason for noise.
Installed new Honeywell zone panel and replaced top of American standard heat pump. Also filled out quality assurance form and tested out system in cooling mode. Both zones are operating correctly. System is working fine at time of inspection.
Performed precision heat tune up on comfort maker gas furnace. Replaced 16x25x1 air filter. Checked all electrical conections and components. Blew out condensate drain and pressure switch tubing. Cleaned flame sensor. Checked gas pressure. Performed combustion test. Gas furnace is working fine at time of inspection.
Reclaimed and removed old equipment. Installed new leveled pad, disconnect, whip, line-set, and American standard 2 stage heat pump. Brazed lineset in with nitrogen. Installed new filter rack and placed new American standard air handler on top. Fabricated plenum and sealed all ductwork. Brazed in line-set and filter drier with nitrogen and pressure tested to 300 psi then evacuated down to 130 microns. Installed new ez trap and condensate pump. Ran new vinyl tubing to discharge. Installed new Honeywell t6 pro thermostats and programmed To system. Installed new zone panel and 2 zone dampers. Tested system in cool and adjusted refrigerant charge. Tested in heating and emergency heat. Tested pump. Zone panel was faulty from the factory will need to return to replace and test. System working great at time of install.
Attic unit, heat pump with air handler, found system off upon arrival, set thermostat to call for ac, noticed auxiliary pan was full of water, check drain did not see any blockage on drain, flushed drain with two gallons of water draining fine, auxiliary pan is not level, check ac operation pressures 410........310/140 filter ok, coil looks to be clean, system does not have ez trap or wet switch, unit is from 2009, not sure where the water came from. Primary pan could be cracked and leaking into auxiliary pan, needs further troubleshooting on checking main drain pan, main drain is fine, pressures are within manufacture specifications emailed proposal to check primary pan add water sensor and ez trap, would also recommend the option with system replacement
Installed new 50 propane powervented water heater. Adapted to water lines and gas piping. Installed water heater in a pan with water alarm. Checked piping for leaks. Checked water temperature. Water heater is working fine at time of install.
Performed Quality Assurance inspection on a newly installed air conditioning system. Lots of stuff in the utility room where the furnace is. Did speak with the customer about the items being right up against the furnace and water heater and some things could fall and hit the gas line. Her daughter is coming to the house today and she will clear it out. Inspected the indoor coil the best we could with all the stuff in there. Everything looks great inside and everything is properly sealed. All penetrations sealed and wiring secure and proper. Outdoor unit level. Everything looks and runs great at time of QA.
Performed Quality Assurance inspection on a newly installed gas furnace. Checked over entire system. No ac. Everything good at time of QA.
No ac, found broken low voltage wire inside worn handler, noticed mold inside as well, check outdoor operation and found very weak capacitor, quoted to replace cap customer ok repairs after repairs check ac operation pressures r22 ok, air handler does not have a return/open return from basement straight ac, atmospheric hydronic boiler next to it,