I had Juan come out for a second opinion. He found the existing issue to be simple to solve. I was told the AC could not repaired and should be replaced. Juan corrected the issue, gave the unit a good review, and let me know the unit still has some life left to live.
B1 Clean & Check Service Cleaned and Tested heating system. Everything is working well at this time.
Water in flue pipe. Likely caused by the 90 being turned up and it rained in yesterday. Everything is working well at this time.
Reme halo is no longer working. Blower wheel has some debris. Recommended blower cleaning and an Airscrubber
Performed furnace tuneup, this is first visit on system (contract with purchase of new system.) Verified furnace operating properly at this time.
Performed heating tuneup, this is last visit on current contract. Recommend changing filter within a month (see magnet on furnace for filter shop.) System is operating properly at this time. Passed carbon monoxide test at 0ppm.
Pulled and cleaned blower wheel/assembly. Verified proper operation after cleaning.
Performed furnace tuneup with humidifier cleaning. Blower wheel has substantial buildup due to remodeling. All renovations are finished, scheduled blower assembly cleaning for Wednesday, 2-4 arrival. System is currently functioning properly at this time.
Second option on AC unit in Fishers
Second option on AC in Noblesville
Calibrated thermostat. It was off by 2°. Found no other issues. Everything‘s working good
Calibrating thermostat in Fortville
Cleaned coil. Installed filtration system. Blower cleaning could not be performed. Blower motor shaft has seized to wheel and is damaged. Blower motor and wheel need to be replaced. To replace motor and wheel $652.57 that’s with discounting the blower cleaning that wasn’t performed. Please call the office to authorize repairs and schedule appointment
B1 Clean & Check Service Tested AC system. Inspected inside and outside units. Furnace has dirty blower blades, dirty coil. AC start assist is testing bad. We will reschedule to Replace start assist 45+10 Clean coil Clean blower wheel Install 20x25x1 Polarized media air cleaner
Hot in the master bedroom still. Rechecked all system operations and everything is running correctly. Master bedroom is hot due to lack of velocity in return ductwork to pull hot air out. Would recommend adding inline duct fan in master bedroom to remove heat.
This unit is not the right unit for zoning. It is a single stage system. I recommend a variable speed system. Plenum is not sealed. Losing a lot of air out of the coil/supply drop. Most of the supplies are to close to the end of the trunk. This cuts airflow cause there’s no area to build up. All the flex in the attic is R4.2 which isn’t per code. This insulation isn’t rated high enough for an attic. It’s picking up a lot of heat before it gets to the vents. There is one 10in flex feeding 3 runs for workout room. This isn’t big enough. Zones are opting and closing like they are supposed to but we are losing about 25% of cooling because of duct not being sealed and the insulation not being adequate. To properly fix this issue I recommend replacing the system with a variable speed system with communicating dampers and flex that is up to code. Will quote to replace duct and unit.