Cleaned coil. Installed filtration system. Blower cleaning could not be performed. Blower motor shaft has seized to wheel and is damaged. Blower motor and wheel need to be replaced. To replace motor and wheel $652.57 that’s with discounting the blower cleaning that wasn’t performed. Please call the office to authorize repairs and schedule appointment
B1 Clean & Check Service Tested AC system. Inspected inside and outside units. Furnace has dirty blower blades, dirty coil. AC start assist is testing bad. We will reschedule to Replace start assist 45+10 Clean coil Clean blower wheel Install 20x25x1 Polarized media air cleaner
Hot in the master bedroom still. Rechecked all system operations and everything is running correctly. Master bedroom is hot due to lack of velocity in return ductwork to pull hot air out. Would recommend adding inline duct fan in master bedroom to remove heat.
This unit is not the right unit for zoning. It is a single stage system. I recommend a variable speed system. Plenum is not sealed. Losing a lot of air out of the coil/supply drop. Most of the supplies are to close to the end of the trunk. This cuts airflow cause there’s no area to build up. All the flex in the attic is R4.2 which isn’t per code. This insulation isn’t rated high enough for an attic. It’s picking up a lot of heat before it gets to the vents. There is one 10in flex feeding 3 runs for workout room. This isn’t big enough. Zones are opting and closing like they are supposed to but we are losing about 25% of cooling because of duct not being sealed and the insulation not being adequate. To properly fix this issue I recommend replacing the system with a variable speed system with communicating dampers and flex that is up to code. Will quote to replace duct and unit.
Performed spring tuneup, this is last visit on current contract. System is functioning properly at this time
Removed return run in basement. Increased cfm/ton to 400 and blocked off all downstairs returns. This increased return airflow upstairs substantially. Due to design of house, Advised homeowner to purchase magnet sheets to cover downstairs returns during summer and remove as needed in winter.
Performed spring tuneup, system is functioning properly at this time. Homeowner still having issues regulating upstairs and downstairs temperature in zoned setup. Verified zoning is working correctly, found all returns upstairs not pulling any air. Marcus/Matt previously diagnosed and homeowner elected to wait. Next step is cutting drywall in various chase locations to determine where blockage is at. Scheduled this step for 7/1 @9am
Performed spring tuneup on both systems. Corrected filter direction on downstairs unit. Both systems functioning properly at this time. Recommend checking outdoor coils and cleaning off with hose as needed due to high amount of cottonwood in area.
Called out for system not cooling. Upon arrival found filter clean, airflow appropriate and all components operating. Checked charge and found very low on 410a, system holds 12lbs. Evaporator coil has substantial formicary corrosion. Full system is 15 years old and recommend replacement over repair. Solutions declined at this time
AC service in Fortville
Service In fortville