Professional and Friendly
Unbelievably fast response during our emergency. Professional, and extremely helpful!!! Very knowledgeable and diagnosed the problem as well as fixed same day!! We are very happy with him and will definitely continue using your services for all of our HVAC needs! Thanks- Rich and Christy
The technician came in and did everything he was supposed to do. Very knowledgeable and friendly.
punctual and so far so good
Technician was very professional and detailed work done.
Our tech was great!
Found clogged drain and condenser shut off due to the spill switch, barely any water in pan, wiped up and replaced spill sensor, blew out drain and system is operating normally.
Installed Amana condenser with evaporator coil, new linset.
Air handler running but not condenser upon arrival, nest thermostat had error code for no power to Y. Went in attic found float switch tripped due to water in emergency pan, and drain pan over flowing with water. Cleared condensate line and took water out of pan. System fired up and cooling.
Checked operation of dehumidifier. Found compressor tripped on internal overload from overheating. No refrigerant in unit. Recommended to replace. Will follow up with customer with replacement estimate
Completed annual maintenance on two ductless heat pump,systems.
Found Cracked drain pan in attic Hydro Air Handler, causing water damage on 2nd Floor Bedroom through 1st Floor. need to follow up with price to replace.
Drain line was clogged, also found pitch off a little on line, adjusted, tested, system operational.
Performed annual maintenance. Checked pressures, capacitor,contactor, cleared trap, checked blower wheel and delta t. Replaced 20x20x4 Merv 11 filter. System is operating normally.
Found emergency pan filled with water. Found condensate trap restricted and also condensate pump overflowing. Removed water from pan, cleared condensate drain trap and replaced condensate pump. Tested with water.
Found system low upon arrival , system has r-22. Recharged system. Delta t now at 20 degrees. Also found mold in system. Recommend uvc system. Replaced one 20x30x1 customer supplied filter. Cleared condensate line. Cleaned both coils. Completed tune up on this system. Customer would like estimate for replacement of ac system. No further issues to report at this time.
Completed annual ac tune up on one system. Learned condensate line. Replaced one 16x25x1 filter. Cleaned both coils. Took temperatures and pressures. Customer advised of r-22 phase out. Recommend uvc system. Unit tested positive for mold growth. Tested both capacitors. No issues to report at this time.
Completed annual ac tune up on one system. Replaced one 16x25x1 customer supplied filter. Cleared condensate line. Took temperatures and pressures. Tested capacitors. Tested condensate pump. Cleaned both coils. Performed mold test in indoor unit. Mold test came back positive, recommend uvc system.
Completed annual ac tune up on one system. Replaced one 16x25x1 filter. Cleared condensate line. Cleaned both coils. Tested indoor evap coil for mold. Mold test was positive. Recommend uvc system. Checked temperatures and pressures. No issues to report at this time.
Found emergency drain pan filled with water. Float switch never shutdown system and pan overflowed onto ceiling. Checked operation and installation of system. Found improper drain trap for attic air handler. Float switch was never secured to drain pan properly. Found air filter completely restricted. And found system slightly low on charge. Installed proper drain trap, removed water from emergency drain pan, secured float switch to pan, replaced air filter. And charged system with R410a to proper running pressures and temperatures. Checked drain with water. Maintenance to be done next spring.
Condenser still turning on/off every few minutes. Tried moving air sensor a few feet farther away from coil. Still doing same thing. Looked at zone dampers again. Opening and closing normally. Need to replace blower or replace furnace.