Danny was awesome. He’s probably due for a raise!
Just had Chris from Folkes service our boiler. Great experience with Folkes and such nice people. We’re very careful when we pick a company to service anything. Highly recommend.
The serviceman was very polite and knowledgeable.
Liked that I got text when he was about to arrive. The tech came at time scheduled which was amazing.
The tech, Chris, was very nice. I think he did everything that he was supposed to do. He also answered all of my questions in a very nice manner.
Folkways provide excellent service
Chris Hait was very professional. He serviced the HVAC system and provided me a folder with information about Folkes and coupons. Thank you!
Cleaned and serviced one oil fired system with MA. Also cleaned and serviced one oil fire boiler with MA. Customer also renewed maintenance agreement.
Bad cad cell eye, reading 3-4000 ohms replaced, transformer is weak, replaced, tested, system operational, cycled on and off several times, no issues to report. Collecting half of the amount of $701.19 which is $350.60 remaining amount in two weeks, 12/15/2020 of $350.60. Follow up
Cleaned and serviced gas furnace itâ€™s MA.
1 gas & 1 A/C renew
Primary control tripped upon arrival, before powering unit back up pulled burner head to inspect nozzle and electrodes which looked good, burner head not dirty, made sure was getting oil to pump which I was. Reset primary control system fired flame looked good, priority zone which is hot water heater heated up to temperature then tested all other three zone which all called for heat and turned on. Boiler operational at this time may have a intermittent issue happening let boiler run for close to an hour and primary didnâ€™t trip.
Clean and service Gas with MA
Cleaned and serviced one gas furnace with MA. Customer also renewed maintenance agreement.
C/S Oil. Replaced filter strainer and nozzle. Brushed and vacuumed System. Boiler was installed 2019, all parts are under a year old and are all in good shape. All zones working properly, took smoke and combustion reading. System running normally. Customer has $189 coupon, purchased Ma for $199.
Arrived and found pilot out, relit the pilot and tested the system. This system uses a different type of thermocouple but the thermocouple is testing good. If the issue continues the customer will have to replace the gas valve.
Cleaned and serviced one gas furnace with MA.
Completed annual maintenance on one oil fired furnace, vacuumed combustion chamber, changed filter nozzle and strainer, changed return air filter 20x20x1, took combustion and efficiency test which everything looked normal, tested system and everything operational at this time.
Replaced OEM control board. Cycled system a few times fired every time. System operational and working at this time.
Cleaned and serviced one gas furnace with MA. Brought to customers attention she has a small leak coming from heat exchanger collector box gasket, she will take a estimate for repair.
Cleaned and serviced one gas furnace with MA. Customer just changed return filter but left a extra filter for customer.
Changed customers return air filter 24x24x1. And noise is just inducer fan motor working, unit sits right up against wall adjacent to bedroom.