The people at Folkes are awesome, especially Danny B. Thank you
Well informed about project and clean
First time user, but it looks like I'm going to keep using Folkes Home Services for my AC and heating units.
Greg Murphy he was very professional. Was very thorough analysis as we did have same problem four times in row. I appreciate explanation why it kept happening. His helper was very professional as well.
Kurt was great and he was very professional. I wouldn’t mind having him service my unit again in the future if need be. I have no complaints. 10/10
Customer said AC not shutting off, came to home and system was off, first started with AC dropped temperature in home to 73, let run turned thermostat to 76 and system shut off, cycled heat raised temperature to 80 burner came on let run until blower came on, lowered temperature in home burner shut off and blower ran to cool heat exchanger, customer said she was cooking a lot today and was hot so system probably kept cycling to cool off home. Everything is operational and working.
C/S Oil Furnace. Took temperature rise. Replaced oil nozzle and strainer, no oil filter. Washable filters are clean. Checked transformer, cleaned electrodes, tested blower motor, bled air from oil line. Took combustion reading. Unit would not shut off with thermostat would only turn off when pulling one leg of tt off the primary, diagnosed with Kurt and during trial and error primary burnt out, replaced primary, and made new wire at thermostat specifically for rc and rh after retiring unit heat will not come on and shut down with thermostat, tested ac as well to make sure ac would come on and off. Unit running normally.
Clean and service Gas x2
Install Mitsubishi 3ton Heat Pump Run line hide Run line set Electrician came and installed circuit with GFI Outlet Installed remote and explained to customer how system works
Completed annual maintenance on one gas furnace, changed return filter 14x25x1 that customer provided, cleaned flame sensor, inspected igniter, cleared p trap, inspected heat exchanger, checked pressure switch, tested capacitor which tested in range, blower wheel and ducts clean home is only two years old, all amp readings normal, temperature rise was 50 degrees, performed combustion and efficiency test which system looked normal, tested both zones, put thermostat back to where they were set, customer signed up for maintenance agreement and system operational. Mail invoice to customer.
Performed annual A/C tuneup. Checked and clean Evap coil. Tested blower on furnace. Checked air filter(customer just replaced). Cleared and tested condensate drain and pump. Cleaned outdoor coil. Checked pressures on condenser. Tested compressor and condenser fan motor. System in good operational condition.
Customer had several concerns, 1 was with a washable filter sitting on the side of his system, explained that the washable filter was dirty so my technician had put in a disposable air filter in his system, also told him to check his filter once a month and if itâ€™s dirty replace it, he also had concerns about a noise he would hear coming from the openings on the air handler by the refrigeration lines, sealed all air gaps around system with foil tape, tested no noise, he also had an issue with straps missing and fallen down off flex lines, added new strap and re-secured flex lines, tested, system operational.
Completed annual maintenance on two air conditioning systems and one high efficiency gas boiler, for AC systems changed filters 20x20x1/20x22x1, cleaned indoor coils, cleared condensate traps, took amp readings of blower wheels which were normal, delta t readings normal, at condensers tested pressures which were normal, capacitors tested in range, contactors all tested normal, amp readings of compressor and fan motor normal, coils clean. For Navien gas boiler cleaned air screen and water filter for domestic water, cleaned igniter and flame sensor, inspected all water components, tested both zones, took combustion and efficiency test which was normal, all systems operational and no issues to report at this time, customer also had ducts cleaned today by Folkes, and signed up for maintenance agreement.
Full duct cleaning of two systems. Grills taken down and wiped with disinfectant wipes.
Went over thermostat
Fixed hole in the trunk of duct board.
Found drip in shark bite coupling. Repaired leak under crawl space by replacing shark bite coupling with new shark bite couple. Tested water line to ensure no leaks.
Repipe water lines.with pex tubing under sink and in basement due to leak. Water lines feed bathroom sink toilet and shower. Tested
Repipe under bathroom sink to underside of house. New stop valves and hoses. Collected deposit.
Installed gas fired furnace, and ac condenser with evaporator coil and thermostat, started up ac and heat. Removed oil tank with approx 90 gallons of oil. Removed old equipment. LP conversion by propane company