Noah is very knowledgeable technician! He can find out the cause within a few minutes.
Amazed to get same day service. Technician was friendly, polite, professional and honest. Great experience.
Greg knows his stuff and did what he could for my aging AC unit. Thanks Greg!
The prompt and excellent customer service between the office staff and the technician was amazing. The communication updates on the techs arrival time was very much appreciated. Thanks for everything!
Noah did a great job! Thank you!
Dustin was very responsive and had a technician at my house in less than an hour on a Saturday. Danny diagnosed and fixed the issue with my air conditioning system quickly and without any issues. He was extremely knowledgeable, professional and explained the issue very well. I would highly recommend Folkes and Danny as a technician.
Arrived at customer house and gave estimates to replace water heater with new water heater and to replace water heater with navian. Gave customer estimates for both a direct replacement and a high efficiency replacement.
Truck desperately needs oil change.
Found system leaking out of the backside, customer cleared water from the secondary drain pan himself before I arrived. Float switch did not go off, found the condensate drain clogged, blew it out 6 times, repitched the entire system with vibration pads and tested drain with multiple bottles of water. System is operating properly.
Customers indoor units blower would kick on and off every 2 to 3 seconds. Found defective board. Replaced board, system would fire up for about 5 minutes, when compressor and fan would fire up indoor unit would kick off 2 minutes after. Attempted to diagnose issue, senior tech is needed to diagnose issue. Left new circuit board hooked up, and old one is in box nex to unit, did not charge for board or diagnostic, when senior tech diagnoses issue; charge for diagnostic and circuit board if it was the issue.
Arrived at customers house for a water leak coming. From well pressure tank. After explained what was going on found the boiler drain on the tank tee to the pressure tank had a slow drip. Tried tightening it but couldnâ€™t get it to stop. Replaced the boiler drain.
Found leaking capacitor and tested which fan side of capacitor was dead. Replaced capacitor and tested system and everything operational.
Completed annual ac tune up on one system. Cleared drain lines. Brushed both coils. Replaced one 20x30x1 filter. System has r22, customer advised of phase out. No further issues to report.
Customer mentions thereâ€™s a noise at furnace, checked blower wheel and motor, found housing a little loose, secured, took door off evaporator coil examined coil, heat exchanger, and blower wheel with inspection camera, did not find anything that could cause noise. No noise, system operational checked pressureâ€™s, delta t.
Replaced Evaporator coil, pressure test, pulled vacuum, and charged, tested, system operational.
Customer stated system was still not cooling overnight. Checked over entire system. Cycled on/off multiple times. Checked refrigerant pressures and temperatures. Found evaporator coil completely restricted. Removed coil and cleaned. Pressure tested, evacuated and recharged system. Current running pressures 136/331psi, superheat 4, sub cooling 6, temperature differential 20.
Found ac system working properly, system has very good air flow in all supply vents and it has a 15 degree split. Explained to customer since master bedroom has 5 vents and kids room only has one and doors to bedroom are mostly closed. Will have them try leaving doors open to get as much cold air into kids room as possible.
Called out for an estimate to install a customer supplied stackable washer and dryer also to to move the toilet and sink in the bathroom to a different location in the bathroom. After speaking with the customer regarding the work that needs to be done, I gave an estimate and went over that with the customer. If they decide to move forward with the work they will call back to schedule.
Sprayed and tested all gas line fittings also checked gas valve and burners and ignition rod for any leaks. No gas leaks found at this time. No smell of gas upon arrival looked over all gas components on boiler. System safe with no leaks at this time.
System operational suction line sweating on unit, Told customer to seal with tape or wrap.
No AC due to bad control board at furnace, board dropping 24 volts to condenser, replaced, tested, system operational.