Danny is an exceptional technician. He’s thorough, knowledgeable and professional. We’ve been using Folkes Heating for a long time - highly recommend them!
Response from Folkes Heating, Cooling and Burner Service:
Perfect! We appreciate you.
Completed annual maintenance on two high efficiency gas boilers. Customer stated was getting temperature sensor lockouts at the end of last season. Ran boiler through several cycles, did not receive error code. Recommended replacement of water temperature sensors. Customer will wait on repairs. Took ordering information in event of further repairs.
Found broken wire. Fixed wire after chasing it found thermostat bad. Replaced thermostat and tested system and system operational.
Completed annual ac tune up on one system. Cleared drain and trap lines. Customer replaced 16x25x4 Merv 11 filter upon arrival. Took temperatures and pressures. Sprayed coils with cleaner. No issues to report at this time.
Found condenser not running, had 24 volts to the contactor but no high voltage to it. Tested for voltage at the disconnect and did not have voltage. Found a tripped breaker, removed the low voltage and turned the breaker back on, the breaker did stay on and I had voltage to the disconnect. I then disconnected the 3 wires going to the compressor and tested the fan motor, the fan motor ran and did not trip the breaker. The compressor has a short in it. This system is r22 and would have to be replaced, there is nothing we can do at this point to get this system running again. Went over details with wife and husband.
Completed annual AC tuneup on two systems. Both systems low on R22. Took temperatures, took delta T, took amperage, took pressures. Recommend replacement of both units as per R 22. Recommend duct cleaning.
New MA 1 oil and 2 A/C
Found break in low voltage line on 1st Floor, repaired, tested, system operational.
Clean and service Oil with maintenance Agreement
Clean and service oil with MA, replaced circulator pump, air vent, and flanges. Tested, system operational.
Ac Tune up x4, Cleaned Electronic Air Cleaners, and added trap to first floor unit found unit not draining water properly. Systems operational.
Found thermostat at indirect Water Heater not functioning properly, reset, primary control on hard reset due to not getting proper flow of air to nozzle assembly, found clogged burner head, cleaned , tested, system operational.
MA renewal 1 oil
Completed annual maintenance on oil boiler