The techs were very professional, however the out come of the work fell below my expections.
It was a good experience. I thought it was a fair price to clean my Furnace.
Easy and quick. Couldn’t ask for anything better.
Wonderful A+ rating
Recommend several options and very smart overall
Completed annual maintenance on AC system and propane furnace. No issues to report systems operational and working.
Found hole,in pipe in 1â€ copper before well,tank and water filters. Need plumber to follow up with repair.
Arrived at customers home to inspect a leak coming from a pump that circulates chlorine into the water softener. The leak was coming from the base of the pump. I did not have proper material to make repairs and I tried to call the pump manufacturer to order the part that is needed but they was closed at the time I called. Customer simply turned the pump off to stop the leak but we need to order the correct part and return.
Service for pump kicking on and off rapidly. Arrived to meet customer who had just installed new well pump at there home. Customer explained he has done it before but this time it was kicking on and off and draining back down the well. Found that the check valve down the well was not holding and the tank needed air in it. Customer explained he knew how to do it he just needed the brains to get him going. Customer is satisfied with service. He is going to make all the repairs needed.
Replaced thermostat wire for first floor nest ran and tested. Took pressures and temperatures system running normally. Compressor running rough due to age.
Customer had installed nest thermostat for first floor, had to charge thermostat, pulled thermostat off wall and found it did not have enough wires only had three wires connected to Honeywell zone panel in attic, customer will need new thermostat wire run from first floor to attic will need holesaw and extension to go through support beams of home only has a small hole where a tied thermostat wire wonâ€™t fit through hole, also would like a second thermostat wire run for second floor thermostat so he can eventually install a nest on second floor as well. Customer would like work performed Monday if all possible. Emailed estimate for customer to run wire.
Folks arrived on 07/28/2021 to inspect the well system. Upon arrival I noticed the pressure in the faucet in the downstairs bathroom was very low. I started by checking the filter, it was clogged I screwed the housing back up with no filter in it to check pressure. The pressure was better. I then checked the ohms from the pressure switch to the pump to check the pump I got a bad reading. I then went out to the pump and tested the wires going down to pump and wires going to the house. The wires going to the pump were good and showing that the pump was in good shape. I then checked the wires to the house and it was showing that the wires were bad going to the house. Iâ€™m going to recommend replacing the whole house filter to something bigger as well as a uv light to kill the bacteria. Iâ€™m also going to recommend replacing the wires from the house to the well.I then thanked the customer for choosing folks and left. This is for going over the whole system
Found capacitor failed causing breaker to trip. Installed turbo 200 capacitor and reset breaker. Let system run for 20 minutes and breaker did not trip. Pressures and temperatures are good.
Arrived and the customer stated he air didnâ€™t feel as cold as it used to. Also one time the system turned off them 2-3 mins later turned right back on. They have a mercury thermostat for the system which may of caused the turning on and off quickly issue. They like the mercury thermostat. Checked pressures and temperatures. The system is operating fine. No issues. Older r22 system may just be inefficient.
Arrived and found the burner leaking oil and tripped. Found the flare but on the oil line loose. Tightened and cleaned up the leak. Reset the burner and heard a clicking noise and the burner ran very rough. The oil coupling was stripped. Replaced at no charge since this should have been caught when we replaced the oil pump. Restarted and the system ran a lot better but it still tripped off after 45 seconds of run time. Replaced he cad cell eye and the system ran normally.
Found bad oil pump upon arrival. Replaced. Adjusted oil pump pressure. Performed smoke and combustion test. Tested system operation several times. Tested hot water and heat.
Completed annual ac tune up of one system. System is about 10years old. Found duct work to be extremely dirty. Highly recommend duct cleaning. Replaced air filter. Cleared condensate drain line. Checked temperatures and pressures. Cleaned coils. No further issues to report at this time of service.
Completed annual maintenance on ac system. Replaced customer supplied MERV 11 filter. Checked overall system operation
Cleaned and serviced on oil furnace with MA. Changed filter nozzle and strainer, vacuumed burner shoots for furnace, tested blower capacitor which tested in range, blower wheel clean, changed return filter 20x20x1, performed combustion and efficiency test which everything looked good. System operational and working.customer was refby Mike Tesoriero.
Replaced OEM burners for Goodman furnance, tighten nipple going to gas valve slight gas leak, turned system on let run for a half hour before doing combustion test which combustion test looks good, adjusted gas gas pressure for propane on low side only due to unit not being wired for high fire or second stage, changed return filter for customer he provided, checked all vents blowing warm with temperature of supply vent of 120 degrees, cycled system fired each time. System operational