Wonderful A+ rating
Recommend several options and very smart overall
Performed annual maintenance on air conditioning system. Changed return filter 20x30x1 In hallway. Test capacitor inside upstairs unit. Cleared condensate trap lines. On outside unit heard fan running but no compressor running. Tested capacitor and it was dead. Replaced with turbo 200 capacitor to get system running. Checked pressures and noticed they were very low system almost empty of R22 refrigerant. Customer will think about recharging system at later time since they recharged it last summer as well.
Performed ac tune up, checked all components. Found a lot of growth on the merv 11 filter, customer had a replacement. Went over options to take care of this issue with the customer.
Cleaned and serviced two oil fired furnaces. Replaced filters, strainer and nozzles. Took combustion tests.
Estimate for Oil to Gas conversion. CHUD will gave gas run there by April. He needs pricing for new gas equipment, removing old oil equipment, running line from curb to house and to appliances. Both he and wife Darcey will be present.
Found fan not energizing on call for fan. Checked fan circuit. Jumped up out circuit at thermostat and fan turned on. Checked settings and tried to run fan in test mode. Still will not turn on. Thermostat or completing circuit for fan. Customer stated was working before maintenance. New customer installed nest.
Arrived at customers home found the water pressure low. Recommened replacing the jet pump with a new pressure tank to increase pressure. Water pressure now is around 30 psi. Also tested water and recommend a water softer to treat hard water. Ph, iron and sulfur are fine or not present. Water analysis Hardness 15 gpg Ph 7.1 Iron 0 mg/L at faucet Sulfur 0ppm
Completed annual maintenance on oil furnace. Customer would like to schedule appointment with plumber. Have water pressure issues in home, well water.
No heat due to bad Aquastat, not sending voltage to circulator pump, needs to be replaced. Shut down system so parts donâ€™t burn out.
Navien system making howling noise. Sent video to manufacturer. Recommended to have heat exchanger flush and and system pump sized increased. Need to call customer with pricing. Customer would also like to set appointment for ductless ac estimate.
Installed vapor sensor. Hot water checked and tested.
Repair boiler zone piping
Found circuit board no good not sending power to blower replaced and tested
Completed annual maintenance on 1 year old gas boiler. Found water heater locked out on â€œvapor sensorâ€. Flammable vapor sensor is missing, need pricing and availability to install also need to replace boiler relief valve. Brass is bent and cannot install drip leg on current valve.
Vacant house. Found no power to boiler. Electrician has ran new circuit to boiler. Have power to emergency switch but not down to boiler. Bad circuit. Needs to have electrician come back and correct power issue to boiler.
Customer stated indirect is causing burner to short cycle. Checked indirect settings. Temperature 130 and raised differential setting to 15. Boiler aquastat set to 180. Zone valve operating normally. Checked domestic water temperature, normal.