James was so polite, personable, and efficient. Tended to my problem and was finished up in short order. He cleaned up his mess and asked lots of pertinent questions regarding my issues before he left to make sure we were on the same page. I'm so appreciative.
Gave my two systems a thorough checkout, both inside and outside, and declared everything in good order. Professionally done. Very neat and courteous.
Very pleased with the service and installation we received in replacing our water heaters.
Bryan was professional and clearly communicated the problem and the required repairs. He was friendly and timely too. AC is working again. Thanks!
Jorge was great
Josh gave us a call before his arrival and matched his ETA. After checking our system, it was determined the system was faulty. Being 11 years old, the "bandaid fix" was not trustworthy, so a new A/C was the best choice. After much information on comparison units, Josh gave us a presentation on three that would fit our needs. He even surveyed our home area to calculate size. After a three hour meeting, we came to a decision. AND....the installation will be tomorrow! Quick service!
Very professional! Very courteous!
Jorge did a very thorough job and was very kind and respectful. I most appreciated that he gave me ideas on what may need to be updated in the future. He represented your company in a very professional way. I feel like he truly knew what he was talking about! This made me pleased that I changed my maintenance contract to Home Force.
Knowledgeable and frank. I wish more people were like him
Quick response, quick diagnosis, good communication
Performed maintenance on single gas furnace and coil
Performed three system spring maintenance club members
Performed two system spring maintenance non club members
2 carrier gas systems with coils
Performed two system spring maintenance Angie's list special
Spring tune up
Performed two system spring maintenance club members diagnosed and replaced contractor
Spring tune up
AC Service- Spring AC Tune Up on Lennox Air Conditioning System
Diagnosed blown fuse performed full diagnostic test found system to be low on r22 freon added. Charging to manufacture specs. Performed load calculation An replacement system quote
Performed one system spring maintenance club members on carrier gas furnace straight cool ac found no potential failures at this time.
Plumber Needed Repairing Leaking Dishwasher and filtration system.
Plumber Needed Free Estimate to repair or replace leaking pipe.
AC Service Cleared primary drain line