Have any feedback for us? We'd love to hear it! Call us at (205) 417-2030 and let us know how we are doing.
It was a pleaure to meet Rodney Malone from your organization who provided scheduled maintenance on my cooling and heating systems. Rodney did a supurb job of inspecting and replacing parts which needed repair as well as recommending improvements where warranted. I was impressed by his knowledge, enthusiasm and professional attributes. Your organization is fortunate to have him on board. Dr. Adel Alapour.
Pleasant young man that seem to know what he was doing. My only complaint would be to be more conscientious about making a mess inside the home after coming from a wet outside to spreading insulation from the attic everywhere. WHAT WENT WITH THE BOOTIES??? previously the tech always wore them when working inside. That should be a must every time a tech enters someone’s house.
Rodney was great at explaining to me about my return not being big enough for my unit.
Felt confident in his diagnosis of problems, his solutions, and the efficiency of job performance.
Nic did a great job!
Arrived for maintenance. Cycled thermostat in heat and emergency heat. Made sure heat strips are working. Changed both filters. Checked control boards for burn marks. Checked electrical. Checked outdoor unit. Checked capacitor. Found a weak secondary motor on the American standard unit. Replaced. Checked contacts. Checked motor amps. Cleaned outdoor coils. Cycled system back on. System up and running.
Replaced tstat under warranty Checked power issue customer to contact electrician power issue appears to be due to to high of amp draw or over load on panel on particular circuit
Arrived for service tune up and checked all three indoor units such as evap coil, motors, switches, wirings and pressures. Andre. He led all three outdoor units such as fan motors, compressors, contactors and wirings and washed units with coil cleaner and systems are operating normal.
Installed surge protectors and virus eliminator and new tstat on 1/17/20
Came out to job. Cleaned two units. Did two furnace tune ups. Checked components, checked wiring, wiped down inside of furnace. All checked out today. Maintenance agreements expire. Need to renew. Units could use surge protection.
Did system maintenance and checked all components. System is working fine but bacterial growth starting to develop inside blower housing.
These items will need to be done to assure the safe, efficient and long term operation of your system.
Attached filter grill temporarily till we get new ceiling filter grill in to return to install New grill is a 20x30x1 89.00 Client already pre paid for grill and install
System fully inspected furnace operating as expected cycling on and off normally no areas of concern on condensing unit outside or coil inside , ductwork clean and properly put together system refrigerant levels look normal no leaks found, nothing recommended to do with unit system functioning normally upon departure client wants copy of invoice for selling home
Performed system clean and check x2. Replaced Filters 20x30x5. Found no other areas of concern. Both systems running upon departure.
Arrived for maintenance Checked indoor unit. Checked drain line Made sure lights were operating properly Checked particle catcher. Checked heat strips. Checked blower cap and found it in bad range. Customer yes repair. Checked outdoor unit. Sprayed it off. Checked capacitor and contactor. Found some pitting on the contacts. Checked amp draw on unit was higher than I like it. Recommended a hard start kit to take some load off the compressor and help the lifespan of the unit. System staring amp draw is high. Thermostat operating properly. System up and running before leaving Upgrade
Upgrading outdoor part Part sold and installed by Aaron Anderson today.
Installed new power supply board, and checked operation unit working properly upon departure
Replaced nest thermostat and 213 filter. System performing properly upon departure.
Arrived for door panel not being properly set back on unit found bad thermostat Cycled system multiple times in a/c and heat Had customer check vents for proper air flow in each mode Returning on01/16/20 to install media cabinet BGI and surge protectors Already installed new t stat and client has already prepaid