Have any feedback for us? We'd love to hear it! Call us at (205) 417-2030 and let us know how we are doing.
They were on time and the work timely. They left work area tidy
He was very professional but personable. Wore his mask and shoe covers while in the house. Quickly zeroed in on what the problem was with the heater. Very reasonable charge for service
Really appreciate fast service !!
The technician was knowledgeable and understandable person.
Jason was very professional and very knowledgeable. A true asset to your company.
I will recommend to others
Ian did a thorough job checking both of our heating units. He did an excellent job explaining our systems .
Did a good job
The technician showed up very early in the given window, which was much appreciated. He was professional, efficient, and wore his mask the whole time. Good experience.
Change out pressure switch on main level system furnace working as should
Arrived on no heat Call, upon further inspection found 2 bad relays Ordered 2 new one from wittichen installed checked wiring Heating at time of departure
Arrived to serviced condensor coil checked refrigerant levels. Costumer said filter was changed and no problems with heat
Performed full system tune up. - ran and tested proper operation of system. - tested all components, voltages, and refrigerant charge. - cleaned coils. - added cleaner to drain line. System is clean and functioning normally upon my departure. Filter could use replacing.
Found locked up draft motor, and significant issues with heat exchanger have supervisor contacting manager to discuss issues
Came out to job. Cleaned unit. Found bacteria inside unit. Other than that checked components and all checked out today. Operation is fine today. Unit is working on departure.
Ran 3/4 supply gas to increase volume for additional 1/2 copper ran for future gas stove
Performed system clean and check x2. Found no areas of. Both systems operating properly upon departure.
Blower motor not working. Will need to call and get price tomorrow. System not heating upon departure.
Arrived on call no heat found a bad power switch to furnace customer is going to replace him self
Mobile home style for double wide
Replaced high limit switch, system is now working normally. System is 16 years old and mismatched with 8 yr old ac, insulation is peeling off inside Furnace and coil is also leaking. Recommended repair vs replacement options, but Mr. Sun wants to keep repairing it.
Blower pull and clean. Swapped out blower motor. Clean dust and dirt in cabinet of furnace. Check blower and heat system operating as should
Arrived on call system making loud noise while heating. Upon inspection found a defective outdoor fan motor. Gave price of $656 to replace, customer has family member that can probably do it.