Performed a Silver ESA Summer Maintenance on main York split heat pump. Checked coils, and customer did not want cleaning. Checked amp draws on motors and compressor. Checked thermostat, capacitor, and temperature split. Checked 410A pressures. Unit is operating properly at this time. Customer renewed Silver Maintenance agreement for Main York system.